7 Grounding for Power Quality NEC states that ground resistance should be less than 25 ohms. Is this true?
8 Grounding for Power Quality No! NEC states A single electrode shall be supplemented by an additional electrode... If a single electrode has a resistance to earth of 25 ohms or less the supplemental electrode shall not be required. Is this good enough?
9 NFPA 70 the NEC
10 Conventional Industry Standard IEEE Std
11 Grounding for Power Quality Why do we ground our electrical systems? We ground our electrical systems for two reasons: 1. For Safety 2. For Power Quality This seminar will discuss safety, however, our primary topic is POWER QUALITY.
12 The Power Quality Pyramid Custom Solution Custom Solution Uninterruptible Power Supply System Uninterruptible Power Supply System Power Conditioning Power Conditioning Harmonic Cancellation Harmonic Cancellation Grounding and Surge Protection Devices Grounding and Surge Protection Devices (SPD)
13 The basic Safety grounding system (Normal Conditions) Transformer 480V Secondary Panel Motor/Load (40 Ohms) 20Amp CB N G 480 Volts 40 Ohms Equivalent Circuit? Amps 12 V A R
14 The basic Safety grounding system (Ground Fault condition) Transformer 480V Secondary Panel 20Amp CB Breaker Trips Motor/Load Internal Ground Fault.2 Ohms N G 480 Volts.2 Ohms Equivalent Circuit? Amps 2400 V A R
15 The basic Safety grounding system (No/poor ground) Transformer 480V Secondary Panel 20Amp CB Motor/Load Internal Ground Fault.2 Ohms N G 480 Volts.2 Ohms Equivalent Circuit? Amps Ohms V A R
16 The basic Safety grounding system (No/poor ground w/people) Transformer 480V Secondary Panel 20Amp CB Motor/Load Internal Ground Fault.2 Ohms N G 20,000 Ohms 480 Volts.2 Ohms Equivalent Circuit 24mA Can Kill! Ohms? Amps 20,000 Ohms V A R
17 Why Grounding for Power Quality? IEEE 142 IEEE The grounding of sensitive electronic equipment, such as computers, programmable logic controllers, process plants, distributed control systems, and similar electronic equipment, has been found to be one of the important items in achieving useful operation from these systems. The low operating voltage of computers and other sensitive electronic equipment makes them susceptible to random voltages far below levels that are perceptible to humans and that have no effect on electrical power equipment. Certainly the voltages injected into the earth by lightning strokes even within several thousand feet, unless suitable neutralization is accomplished, can cause malfunction and can possibly damage the equipment.
18 Grounded vs. UnGrounded Systems UnGrounded system An electrical system in which there is no intentional connection between the conductors and earth.
19 UnGrounded Systems UnGrounded system An electrical system in which there is no intentional connection between the conductors and earth. Advantages Service Continuity. Disadvantages Very High ground currents due to leakage Capacitance in the entire system. Power System overvoltages passed into the premises wiring system. (Lightning, switching surges, inter-contact between high voltage systems) Transients are not controlled. System voltages can be unbalanced.
20 Grounded Systems Grounded system - Delta An electrical system in which there is an intentional connection between the conductors and earth. Advantages High fault currents may flow on the first ground fault, requiring the immediate clearance of this first fault. The voltage to ground in this system will be the system voltage, usually 240 or 480 volts. Disadvantages Avoidance of installing equipment ground fault protection as required by the NEC on solidly grounded Wye electrical services. The system is unable to supply dual-voltage service for lighting and power loads. It requires a positive identification of the grounded phase throughout the system. A higher line-to-ground voltage exists on two phases than in a neutral-grounded system. Fault switching (opening) is much more severe for the clearing device, and ratings may be greatly reduced. Many manufacturers electrical distribution equipment is not rated for use on this system. They are not recommended for new installations because more suitable and reliable systems are available today Power System overvoltages passed into the premises wiring system. Transients are not controlled.
21 Grounded Systems Grounded system - Wye An electrical system in which there is an intentional connection between the conductors and earth.
22 Grounded Systems Grounded system - Wye An electrical system in which there is an intentional connection between the conductors and earth. Advantages Low ground currents due to no leakage Capacitance in the system. Power System overvoltages attenuated into the premises wiring system. Transients attenuated. System voltages balanced. Personnel Safety. Disadvantages Some may argue for Service Continuity, however, many more power quality problems usually occur with ungrounded systems.
23 Earth Reference IEEE 142 (4.1.2) states that ground resistance should be 1 ohm for substations and 1-5 ohms for commercial and industrial services. Many equipment vendors require less than 3 ohms. Why?
24 Why ground resistance less than 5 ohms? IEEE States: A quality connection to earth through the grounding electrode system for a commercial or industrial facility's power system is necessary for: Providing a low impedance path for lightning stroke current dissipation The reduction of Step and Touch potentials under line-to-earth fault conditions The dissipation of electrostatic charges The proper operation of electrical and electronic equipment The proper operation of Surge Protection Devices (SPD s) (TVSS units)
25 Earth Reference IEEE Recommended Acceptable Values The most elaborate grounding system may not perform satisfactorily unless the connection of the system to earth is adequate for the particular installation. The earth connection is one of the most important parts of the whole grounding system. The connection to earth or the electrode system, needs to have a sufficiently low resistance to help permit prompt operation of the circuit protective devices in the event of a ground fault, to provide the required safety from shock to personnel who may be in the vicinity of equipment frames, enclosures, conductors, or the electrodes themselves and to limit transient overvoltages.
26 How many rods do you need? Using information from two sources lets look at a typical ground rod installation. Source #1- ANSI/IEEE 142 Source #2- White Paper - DEEP EARTH GROUNDING VERSUS SHALLOW EARTH GROUNDING by Martin D. Conroy and Paul G. Richard
27 How many rods do you need? Service Entrance Panel Service Entrance Panel 1-10 ground rod 25 ohms to earth 2-10 ground rods 15 ohms to earth 3-10 ground rods 11 ohms to earth Using IEEE Does this meet IEEE standards? 1-10 ground rod 25 ohms to earth 1-20 ground rod 7 ohms to earth 1-30 ground rod 4 ohms to earth Using Deep Earth paper
28 Soil Moisture Changes NEC states.that ground electrodes shall be embedded below permanent moisture level. This is prefaced by the term If practicable
29 Soil Moisture Changes Soil moisture content varies greatly down to about 10 feet Does not peak dry much below 30 feet. Nevada
33 Earth Reference After Installation IEEE Need for Measurement Many indeterminate factors exists in any formula for the calculation of the resistance to earth. Total reliance should not be placed on the calculated results. For example, the soil resistivity varies inversely with the soil temperature and directly with the moisture content and may vary with the depth. The only certain way to determine the resistance is to measure it after the system has been completed. IEEE Periodic Testing Tests should be made periodically after the original installation and test so that it can be determined whether the resistance is remaining constant or is increasing. If later tests show that the resistance is increasing to an undesirable value, steps should be taken to reduce the resistance Don t bury it and forget it!
34 Ground Measurement Techniques Two Main Methods: 1. Fall of Potential Method 2. Signal Injection Method
35 Fall of Potential Method Service Entrance Panel Ground Meter Ground Electrode Area of Influence
36 Signal Injection Method Service Entrance Panel Ground Electrode Area of Influence
37 Pulling Green Wire IEEE Insulated Grounding Conductors Reliance on the metal raceway is not recommended. An internal grounding conductor improves the efficiency of the ground return path. Internal ground-return conductors do improve reliability, especially when sensitive electronic equipment grounding is a concern.
38 Single Point Reference
39 Multiple Ground Rods IEEE Problems Analysis (indicates) that the separation of grounds was responsible for very large voltages being impressed on computer components under thunderstorm conditions. These voltages occurred whether or not computers were in operation. The large voltages were due to lightning striking either the building housing the computers or the power system serving the building. When charge centers on lightning clouds were overhead, charges were induced in buildings on the ground beneath them. For Example
40 Is this correct? Service Entrance Sensitive Equipment Ground Rod #1 Ground Rod #2
41 Grounding for Power Quality Service Entrance Sensitive Equipment 10 Ohms Ground Rod #1 Ground Rod #2
42 Grounding for Power Quality Service Entrance Sensitive Equipment 10 Ohms Ground current of 1000Amps caused by lightning Ground Rod #1 Ground Rod #2
43 Ohms x Amps = 10 Ohms x 1000Amps = 10,000Volts Service Entrance Sensitive Equipment 10 Ohms Ground current of 1000Amps caused by lightning Ground Rod #1 Ground Rod #2
44 Ohms x 10 Ohms x 1000Amps = 10,000Volts Service Entrance Sensitive Equipment 10 Ohms Ground current of Ground Rod #1 1000Amps caused Ground Rod #2 by lightning
45 Solution Service Entrance Sensitive Equipment Bond ground rods Ground Rod #1 Ground Rod #2
46 FYI IEEE Connection of the equipment ground to earth with an electrode that is physically separate from all other power system and structural grounding electrodes and is not bonded to any of these other grounding electrodes, will inevitably produce common mode noise, since it is not referenced to the power source ground. The magnitude of this common mode potential can be destructive to the equipment and hazardous to personnel, since a power system fault can raise the power system or structure several hundred or thousand volts above other earth references. This grounding method is also in violation of the NEC, Article 250.
47 Ground Loops Sub Panel Ungrounded Conductor Current Flow (Hot) Grounded Conductor Current Flow (Neutral) Main N G Computers VFD s PLC s Sensitive Equipment Panel L N G None Computers VFD s PLC s Sensitive Equipment
48 Ground Loops Sub Panel Current Flow Return neutral current flowing on Ground Main N G Computers VFD s PLC s Sensitive Equipment Panel L N G Bad Computers VFD s PLC s Sensitive Equipment
49 Ground Loops Sub Panel Current Flow Return neutral current flowing on Ground Main N G Computers VFD s PLC s Sensitive Equipment Panel L N G Computers VFD s PLC s Sensitive Equipment Worse G Stray neutral current flowing through sensitive equipment
50 Ground Loops Sub Panel Current Flow Return neutral current flowing on Ground L Main Panel N G Computers VFD s PLC s Sensitive Equipment Stray neutral current flowing through sensitive equipment via Phone &data cable N G Computers VFD s PLC s Sensitive Equipment Worst G Stray neutral current flowing through sensitive equipment
51 Dedicated Circuits Panel Sensitive Equipment Other Equipment Worst
52 Isolation Transformer Circuit Harmonic Cancellation Isolation Transformer or Low Harmonic UPS System Panel Panel Sensitive Equipment Other Equipment Must Be Bonded Better
53 Separate Circuits Panel Sensitive Equipment Panel Best Other Equipment
54 Isolated Ground Circuits L N IG EG
55 Isolated Ground Circuits IEEE Isolated ground systems are likely to exaggerate power line surges because they do not equalize voltages between different system feeders Isolated grounding may cause stray currents and voltages due to transients Isolated grounding systems rarely (if ever) provide the anticipated protection from EMI (electrical noise) on the system. This is due to the fact that almost all internal circuits in electronic equipment are grounded to the frame of that equipment..
56 The Grounding System An effective grounding system: Using SPD units provides a more stable system with a minimum of transient voltages and electrical noise. Provides a path to ground in fault conditions to insure proper operation of ground fault protection equipment. Provides grounding of all conductive enclosures that may be touched by personnel, thereby eliminating shock hazards.
57 The Grounding System An effective grounding system: Reduces static electricity that may be generated within facilities. Provides protection from large electrical disturbances (such as lighting) by creating a low resistive path to earth. Eliminates ground loops that induce voltages into sensitive equipment.
58 The Power Quality Pyramid Custom Solution Custom Solution Uninterruptible Power Supply System Uninterruptible Power Supply System Power Conditioning Power Conditioning Harmonic Cancellation Harmonic Cancellation Grounding and Surge Protection Devices Grounding and Surge Protection Devices (SPD)
59 Grounding for Power Quality END Please fill out the evaluation form to receive attendance credit. An Address MUST be Provided to receive your attendance certificate. Thank you for attending PQU s Grounding for Power Quality
April 1994 EFFECTIVE EQUIPMENT GROUNDING ECOS Electronics Corporation by Chris C. Kleronomos The quality of the electrical wiring and grounding in a facility containing sensitive electronic equipment is
Upgrading Your Electrical Distribution System To Resistance Grounding The term grounding is commonly used in the electrical industry to mean both equipment grounding and system grounding. Equipment grounding
2 Grounding of power supply system neutral 2.1 Introduction As we had seen in the previous chapter, grounding of supply system neutral fulfills two important functions. 1. It provides a reference for the
Grounding Recommendations for On Site Power Systems Revised: February 23, 2017 2017 Cummins All Rights Reserved Course Objectives Participants will be able to: Explain grounding best practices and code
Overview of Grounding for Industrial and Commercial Power Systems Presented By Robert Schuerger, P.E. HP Critical Facility Services delivered by EYP MCF What is VOLTAGE? Difference of Electric Potential
Single Earthed Neutral and Multi Earthed Neutral. SEPTEMBER 6, 2011 5 COMMENTS Single Earthed Neutral and Multi Earthed Neutral: In Distribution System Three Phase load is unbalance and non linear so The
Current will always try to return to its source In order for there to be current, there must be a complete circuit Current will take as many paths or circuits available to it to return to the source The
Distribution System Operator Certificate This program provides you with a proficient working knowledge in modern electric power distribution systems. These four classes are designed to walk students through
CHAPTER 15 GROUNDING REQUIREMENTS FOR ELECTRICAL EQUIPMENT A. General In a hazardous location grounding of an electrical power system and bonding of enclosures of circuits and electrical equipment in the
The University of New South Wales School of Electrical Engineering and Telecommunications Industrial and Commercial Power Systems Topic 7 EARTHING 1 INTRODUCTION Advantages of earthing (grounding): Limitation
GOOD GROUNDING PRACTICES A Brief Introduction to the Basics of Electrical Grounding for Power Systems Introduction to Grounding TABLE OF CONTENTS 1.0 Introduction to Grounding 2.0 Standard Industrial Grounding
IEEE PES Transmission and Distribution Conference 2008 Panel Session Large Wind Plant Collector Design Wind Farm Collector System Grounding by Steven W. Saylors, P.E. Chief Electrical Engineer Vestas Americas
Summary of the Impacts of Grounding on System Protection Grounding System grounding big impact on ability to detect ground faults Common ground options:» Isolated ground (ungrounded)» High impedance ground»
GROUNDED ELECTRICAL POWER DISTRIBUTION Excerpt from Inverter Charger Series Manual BY: VIJAY SHARMA ENGINEER .0 Conductors for Electrical Power Distribution For single-phase transmission of AC power or
Tower Grounding Training For Telecommunications Networks Contact us Today for a FREE quotation to deliver this course at your company?s location. https://www.electricityforum.com/onsite-training-rfq The
ECE 528 Understanding Power Quality http://www.ece.uidaho.edu/ee/power/ece528/ Paul Ortmann email@example.com 208-316-1520 (voice) 1 Today Wiring and grounding Why it s important References Terms and
American Electrical Institute Oregon Electricians Continuing Education Grounding & Bonding (Article 250) 4 Hours American Electrical Institute PO Box 31131 Spokane, WA 99223 www.aeitraining.com Article
Protection Basics Presented by John S. Levine, P.E. Levine Lectronics and Lectric, Inc. 770 565-1556 John@L-3.com 1 Protection Fundamentals By John Levine 2 Introductions Tools Outline Enervista Launchpad
The Confusion Surrounding Stray Voltage Jim Burke, InfraSource Inc., Fellow, IEEE Abstract While stray voltage has been a concern for farm livestock for many years, it is only within the past few years
9. INTRODUCTION Control Cabling The protection and control equipment in power plants and substations is influenced by various of environmental conditions. One of the most significant environmental factor
To Float or Not to Float? Analysis of a floating vs. grounded output Associated Power Technologies Introduction In electrical circuits, voltage is always measured between two points: a point of high potential
LA-UR-98-1 Los Alamos NationalLaboratory is operated by the University of California for the United States Department of Energy under contract W-7405-ENG-36 TITLE: SUBMITTED TO: Electrical Potential Transfer
Safety Issues Caused by High Earth Resistance and Identifying Them Using Instruments Thomas Szollossy Senior Technical Support Engineer Power Quality Thailand PQSynergy 2017, Chiang Mai, Thailand Introduction
SEC DISTRIBUTION GROUNDING STANDARD SDCS-03 Part-II Rev.01 SDCS-03 DISTRIBUTION NETWORK GROUNDING CONSTRUCTION STANDARD (PART-II) OVERHEAD NETWORK GROUNDING Rev. 01 This specification is property of SEC
Article 250 Grounding & Bonding AMERICAN ELECTRICAL INSTITUTE N16 W23217 Stone Ridge Dr. Waukesha, WI 53188 855-780-5046 www.aeitraining.com DISCLAIMER NOTE: This course is APPROVED for continuing education
3 CONTINUING EDUC ATION FOR WISCONSIN ELECTRICIANS 2017 NEC Article 250 2 Hours WISCONSIN CONTRACTORS INSTITUTE N16 W23217 Stone Ridge Drive Suite 290 Waukesha, WI 53188 262-409-4282 www.wcitraining.com
IMPORTANT NOTE: You should have received an email from us with a link and password to take your final exam online. Please check your email for this link. Be sure to check your spam folder as well. If you
Applied Grounding and Bonding Paul Dobrowsky Member NEC Panel 5 1 Introduction This presentation is a representative sample from the following Chapters of Applied Grounding and Bonding. Chapter 1, Introduction
CATALOG 2019 Our Brands Aktif trade mark for Measuring, Protection, Automatic Meter Reading, Billing and Energy Management Software. by Aktif Aktif trade mark for Measuring, Protection, Control and Power
SAFETY ASPECTS AND NOVEL TECHNICAL SOLUTIONS FOR EARTH FAULT MANAGEMENT IN MV ELECTRICITY DISTRIBUTION NETWORKS A. Nikander*, P. Järventausta* *Tampere University of Technology, Finland, firstname.lastname@example.org,
1 PRACTICAL PROBLEMS WITH SUBSTATION EARTHING Dr Hendri Geldenhuys Craig Clark Eskom Distribution Technology This paper considers the issues around substation sites where the soil resistivity is of particularly
SDCS-03 DISTRIBUTION NETWORK GROUNDING CONSTRUCTION STANDARD (PART-I) UNDERGROUND NETWORK GROUNDING Rev. 01 This specification is property of SEC and subject to change or modification without any notice
thepower to protect i-gard LITERATURE Low and medium voltage distribution systems Arc Flash Hazards and High Resistance Grounding Grounding of Standby and Emergency Power Systems Neutral Grounding Resistors
Webinar: An Effective Arc Flash Safety Program Daleep Mohla September 10 th, 2015: 2pm ET Agenda Arc Flash Defined and Quantified NFPA 70E / CSA Z 462 - Recent Updates What is the ANSI Z10 Hierarchy of
1.1. Define the term Quality A Standard IEEE1100 defines power quality (PQ) as the concept of powering and grounding sensitive electronic equipment in a manner suitable for the equipment. A simpler and
WAVEFORM CORRECTOR (WAVEFORM CORRECTORS) REPLACES SURGE PROTECTION DEVICES (SPD) PREVIOUSLY KNOWN AS (TVSS) 1 PART 1: GENERAL This section describes materials and installation requirements for low voltage
ARTICLE 810 RADIO AND TELEVISION SATELLITE EQUIPMENT Introduction to Article 810 Radio and Television Satellite Equipment This article covers transmitter and receiver (antenna) equipment and the wiring
Specialists in HV and MV test and diagnostics Testing in Substations Testing in Substations Testing in Substations At 4fores we specialize in the diagnosis and measurement of all types of existing technologies
Surge Protection and Grounding Issues Presented to SCTE Chicago Chapter January 21, 2004 By: Nisar Chaudhry VP Electrical Engineering, CTO Introduction Transients caused by disturbances on the power lines
701880MAC0010.1177/0020294017701880 research-article2017 Contributed Paper Tech Talk (12) Down to Earth: A Discussion of the General Requirements for the Earthing of Control and Instrumentation Systems
Part C: Code Book Questions Article 225: Outside Branch Circuits And Feeders 1.! Open (individual) aerial overhead conductors shall be insulated or covered when within! feet of a building.! (a) 10! (c)
International Journal of Engineering Research and Development e-issn: 2278-067X, p-issn: 2278-800X, www.ijerd.com Volume 4, Issue 6 (October 2012), PP. 100-107 HV Substation Earthing Design for Mines M.
Common Mode Susceptibility of Computers White Paper #9 Revision 1 Executive Summary This White Paper examines and challenges the claims made in literature regarding the alleged high susceptibility of computers
Continued from Part 1 Rules 1 25. 26 225.32 Disconnect Location The disconnecting means for a building or structure must be installed at a readily accessible location, either outside the building or structure
SECTION 5 TRANSFORMERS Necessary transformers will be installed and maintained by The City of Aspen. The City of Aspen will not furnish transformers unless they are of standard size and voltage as established
ENGINEERING STANDARD FOR INSTRUMENTS ELECTRICAL POWER SUPPLY AND DISTRIBUTION SYSTEMS FIRST EDITION MAY 2013 This Standard is the property of Iranian Ministry of Petroleum. All rights are reserved to the
Grounding System Theory and Practice Course No. E-3046 Credit: 3 PDH Grounding System Theory and Practice Velimir Lackovic, Electrical Engineer System grounding has been used since electrical power systems
Utility System Lightning Protection Many power quality problems stem from lightning. Not only can the high-voltage impulses damage load equipment, but the temporary fault that follows a lightning strike
High Voltage Pylon Earth Measurements Speaker: Gavin van Rooy Authors: Frank Barnes and Gavin van Rooy Tycom (Pty) Ltd PO Box 3546, Randburg, 2125, South Africa E-mail: email@example.com Phone: 011 787
Grounding and Bonding of Service Equipment 1. Grounding means: attached to an earth ground. 2. Bonding means: physically connected to insure electrical continuity. NEC 250.4 1. Grounding: Electrical Systems
Earthing of Electrical Devices and Safety JOŽE PIHLER Faculty of Electrical Engineering and Computer Sciences University of Maribor Smetanova 17, 2000 Maribor SLOVENIA firstname.lastname@example.org Abstract: - This
A statistical survey of common-mode noise By Jerry Gaboian Characterization Engineer, High Performance Linear Department Introduction In today s high-tech world, one does not have to look very far to find
EVALUATION OF THE EARTH RESISTANCE VALUE FOR ESE LIGHTNING ARRESTOR TECHNIQUE FOR THE SOLAR PLANTS IN INDIA Rajat Verma Project Engineer BHEL EDN, BANGALURU, MYSORE ROAD, KARNATAKA 560024, India ABSTRACT
Section 11: Power Quality Considerations Bill Brown, P.E., Square D Engineering Services Introduction The term power quality may take on any one of several definitions. The strict definition of power quality
7 Transformers Section 26 of the electrical code governs the use and installations of transformers. A transformer is a static device used to transfer energy from one alternating current circuit to another.
ELEC9713 Industrial and Commercial Power Systems Earthing of Low Voltage Electrical Systems: Personnel Protection Equipment Protection 1. Introduction Earthing of electrical equipment and power systems
4th International Conference on Machinery, Materials and Computing Technology (ICMMCT 2016) Hazard of Induced Overvoltage to Power Distribution Lines Jiang Jun, Zhao Rui, Chen Jingyang, Tian Hua, Han Lin
SAFETY AND HEALTH STANDARD ELECTRICAL GROUNDING Effective Date: 07/17/10 Standard: 16.10 Document Number: KUCSH0039 Rev: 4 16.10.1 INTRODUCTION 18.104.22.168 The intent of this standard is to ensure that continuity
The Electrical Power Engineers Qual-Tech Engineers, Inc. 201 Johnson Road Building #1 Suite 203 Houston, PA 15342-1300 Phone 724-873-9275 Fax 724-873-8910 www.qualtecheng.com ARC FLASH PPE GUIDELINES FOR
Smart Ground Test Report Springfield Energy - Springfield Power Station Grounding System Evaluation Prepared for *C.M. Burns *Springfield Energy Springfield Power Station U.S.A. Prepared by A. P. Sakis
Attendee Announcements Seminar Raffle Be sure to drop your raffle ticket in the drum at today s Keynote located in the Mile High Ballroom. You have a chance to win a $250 American Express Gift Card. One
Technical Note Rosemount Radar Transmitters Best Practices for Power and Transient Protection on Rosemount Radar Transmitters BACKGROUND INTRODUCTION This document describes best practices for power and
NWEMS Primary Metering August 22, 2018 Bill Unbehaun, Tacoma Power Exchanging Expertise Since 1893 What is Primary Metering? Metering energy flow past a point at high voltage above 600v Both PTs and CTs
1 No v 1 6 1 No v 1 6 Iu d a Mo r a r a n d ma n a g e r R a c h e le Ha n n o n Vo l.6 -S u b s ta tio n a n d Hig h Vo lta g e E q u ip me n t;p a r tb -S u b s ta tio n Co n fig u r a tio n s 1. Scope
Issue 3, October 2002 Electromagnetic Compatibility and Electrical Safety Contents Telcordia GR-1089 - Documentation Information Generic Requirements Notice Of Disclaimer................. iii Contents.......................................
Industrial Electrician Level 3 Industrial Electrician Unit: C1 Industrial Electrical Code I Level: Three Duration: 77 hours Theory: Practical: 77 hours 0 hours Overview: This unit is designed to provide
1 FTTH ENGINEERING AND INSTALLATION INTRODUCTION GROUNDING FTTH SYSTEMS AT THE HOME. By Dean Mischke, P.E., V.P. Grounding and bonding. Why are we worried about such an old school concept in the modern
ELECTROMAGNETIC ANALYSIS OF WIND TURBINE GROUNDING SYSTEMS Maria Lorentzou*, Ian Cotton**, Nikos Hatziargyriou*, Nick Jenkins** * National Technical University of Athens, 42 Patission Street, 1682 Athens,
Overvoltage and undervoltage Dr Audih 1 A Overvoltage is defined as an increase in the r.m.s. value of the voltage up to a level between 1.1 pu to 1.8 pu at power frequency for periods ranging from a half
Topic 6 Quiz, February 2017 Impedance and Fault Current Calculations For Radial Systems TLC ONLY!!!!! DUE DATE FOR TLC- February 14, 2017 NAME: LOCATION: 1. The primitive self-inductance per foot of length
Minimizing Lightning and Static Discharge in Broadcasting Lightning and static discharge represent two of the most damaging and unpredictable events faced by broadcasters. Together or separately they are
EMI Filters Demystified By William R. Bill Limburg February 21, 2018 Phoenix Chapter, IEEE EMC Society An EMI Filter Defined An EMI filter is a network designed to prevent unwanted electrical conducted
The Importance of the Neutral-Grounding Resistor Presented by: Jeff Glenney, P.Eng. and Don Selkirk, E.I.T. Presentation Preview What is high-resistance grounding (HRG)? What is the purpose of HRG? Why
Safe Engineering Services & technologies ltd. Advanced Technical Seminar on Power System Grounding & Electromagnetic Interference Analysis and CDEGS Level I Certification Location Date Course Fee Sydney,
Power Protection Products, Inc. White Paper by Dan Maxcy l 2018 Update P3 is the industry s trusted and respected critical power, cooling and energy solutions provider. 877-393-1223 I www.p3-inc.com HARMONICS
EMI Installation Guidelines Although Red Lion Controls Products are designed with a high degree of immunity to Electromagnetic Interference (EMI), proper installation and wiring methods must be followed
Chapter 1 Electrical Theory and Code Questions 1 Unit 1 Electrician s Math and Basic Electrical Formulas 3 Part A Electrician s Math 3 1 1 Fractions 3 1 2 Kilo 4 1 3 Knowing Your Answer 4 1 4 Multiplier
2014 Understanding Noise Cut Transformers By Quality Transformer and Electronics James Nealon Understanding Noise Cut Transformers By Quality Transformer and Electronics Engineering and Sales Staff Quality
Safety through proper system Grounding and Ground Fault Protection November 4 th, 2015 Presenter: Mr. John Nelson, PE, FIEEE, NEI Electric Power Engineering, Inc. Event to start shortly Scheduled time:
A Case Study on Selection and Application of Lightning Arrester and Designing its Suitable Grounding Grid 1 Arpan K. Rathod, 2 Chaitanya H. Madhekar Students Electrical Engineering, VJTI, Mumbai, India
POWER SOURCE # POLE MOUNTED SERVICE TRANSFORMER BY POWER HANDHOLE 0/0V, -PHASE, SERVICE CONDUCTORS; -# AWG SERVICE CONDUCTOR AND -# AWG GROUNDED SERVICE CONDUCTOR (NEUTRAL) SERVICE XFMR SECONDARY. A 0V
National Radio Astronomy Observatory Socorro, NM 87801 EVLA Memorandum 41 Lightning Protection for Fiber Optic Cable T. Baldwin June 05, 2002 Summary Double-armor triple-sheath fiber optic cable will be