CHAPTER 5 POWER QUALITY IMPROVEMENT BY USING POWER ACTIVE FILTERS


 Lee Bell
 2 years ago
 Views:
Transcription
1 86 CHAPTER 5 POWER QUALITY IMPROVEMENT BY USING POWER ACTIVE FILTERS 5.1 POWER QUALITY IMPROVEMENT This chapter deals with the harmonic elimination in Power System by adopting various methods. Due to the development of Power Electronics technology, more Power Electronics appliances are used, which leads the serious harmonics pollutions. Using Shunt Active Filters we can eliminate these kinds of harmonics. The development of new Shunt Active Filter is presented. The concept of proposed Shunt Active Filter and its operating Principle, Control Theory is also discussed. The filtering scheme provides harmonics suppression at the source so that the source will supply high quality power to linear load. The Power Quality has become the buzzword in the last one decade due to increase in qualitysensitive load, like computers, nonlinear switched devices, which are the sources of disturbance to create poor power quality & awareness of implications of power quality. 5.2 INTRODUCTION Quality means customer satisfaction, which cannot be defined absolutely. It is defined with reference to consumer expectations. The quality of a product is thus measured by using yardstick of consumer satisfaction. Electric power quality is satisfaction of its customer; a consumer is satisfied if he is able to use power through his equipment and devices to serve his purpose. This is possible only if his equipment and devices have Electromagnetic Compatibility (EMC) with the supply quality; Thus, EMC is the measure of power quality. The SIMULINK/MATLAB is a highly developed graphical user interface simulation tool. It has proved instrumental in
2 87 implementing the graphical based controller. The Simulation tool has been used to perform the modeling and simulation of the customer power controller for a wide range of operating conditions. The Simulation results of the proposed filter are discussed. The objective of this chapter develops the proposed new shunt active power filter for the current harmonics suppression using SIMULINK / MATALAB for power quality improvement.[42] 5.3 FILTERS Filters are used to restrict the flow of harmonics current in the Power Systems. It is a LC circuit, which passes all frequencies in its pass bands and stops all frequencies in its stop bands. There are two basic types of filters. The simplest method of harmonics filtering is with passive filters. It uses the reactive storage components, namely capacitors and inductors. It has two types. Shunt passive filter is the Combination of L and C elements, which are connected in parallel with the line. It will restrict the flow of harmonics through the line. Fig5.1 shows the configuration of Shunt passive Filter. Nonlinear load L supply Nonlinear load L c supply c Fig 5.1 Shunt passive filters Fig 5.2 Series passive filters Series passive filter is the combination of L & C in parallel, which are connected in series with the supply as in Fig 5.2, which has the ability to eliminate harmonics amplification of shunt
3 88 passive filter. The series active filter needs a much smaller kva rating than a conventional shunt active filter, and as a result, the combined system has good filtering characteristics and high efficiency. This chapter presents a design of the shunt passive filter that makes possible a great reduction in the required kva rating of the series active filter. It can minimize the peak voltage across the series active filter and reduce the required kva rating of the filter to 60 percent. A computer simulation geared to practical applications of large threephase. Thyristor rectifiers are used to compare the compensation characteristics of the optimized system with those of a combined system that uses a conventional shunt passive filter. Active Filters are newly emerging devices for harmonics filtering, which will use Controllable Sources to cancel the harmonics in the Power Systems. The basic principle of operation of an Active Filter is to inject a suitable nonsinusoidal voltage and currents in to the system in order to achieve a clean voltage and current waveforms at the point of filtering. Nonlinear loads source Active filter source Nonlinear loads Active filter Fig 5.3 Shunt active filters Fig 5.4 Series active filters Shunt Active Filter is connected in parallel to the load. The system configuration is shown in Fig 5.3. It consists of a Voltage Source Inverter and a filter inductor connected in series. It performs a harmonics current suppression to the line. Where as series active filter shown in Fig
4 89 5.4, is connected in series with the load. The major advantages of the Series Active Filter are, it maintains the output voltage waveform as sinusoidal and balances the threephase voltage.[43] 5.4 HARMONICS MEASUREMENT Importance of monitoring PQ In a case study where the enduser equipment knocked offline 30 times in 9 months but there were only five operations on the utility substation breaker. There were so many events, which will result in enduser problems that never show up in the utility statistics. One example is capacitor switching, which is quite common and normal on the utility system, but can cause transient overvoltage that disrupt manufacturing of machinery. Another is a momentary fault any where in the system that causes voltage to sag briefly at the location of the customer, which might cause an adjustablespeed drive or a distributed generator to trip off, but the utility will have no indication that anything will miss on the feeder unless it has power quality monitor installed Harmonics study If a case study is conducted with two transformers, in which first transformer is supplying nonlinear load and there are 4 feeders on this transformer, whose rating is 2MVA which were supplying the nonlinear loads. The harmonics distortion can be observed from Fig 5.5. Fig 5.5 Current Harmonics
5 90 Current Time Fig 5.6 Current waveform Table 5.1 Current Harmonic Amp A B C N Harmonics THD%f H3%f H5%f H7%f H9%f H11%f H13%f H15%f Voltage Time Fig 5.7 Voltage waveform
6 91 Voltage Harmonics Time Fig 5.8 Voltage Harmonics Table 5.2 Voltage Harmonic Volt A B C N Harmonics THD%f H3%f H5%f H7%f H9%f H11%f H13%f H15%f Table 5.3 Power & Energy P/V/I/pf A B C Total kw kva kvar pf (least) I rms V rms
7 92 It can be observed from the above waveforms and tables that the transformer contains current harmonics of around 16% and voltage harmonics of 4%. Major harmonics in Current waveform are 5 th and 7 th harmonics. Hence it is strongly recommended to mitigate the 5 th and 7 th harmonics in current waveform Power Quality Evaluation Transform rating: 2 MVA Electrical System = 415V,50 Hz, 3 Ph 3 Wires (With capacitor bank switched ON) Apparent Power, S = kva Real Power, P = 700 kw Reactive Power, Q = 500 kvar Power Factor, pf = 0.97(lagging) (5.1) Source Voltage, V (PhaseA), V A = 243 Vrms THDV fund, A = 4.1% (PhaseB), V B = 243 Vrms THDV fund, B = 4.4% (PhaseC), V C = 243 Vrms THDV fund, C = 4.2% (5.2) Load Current, I L (PhaseA), I L, A = 1500 A THDI fund, A = 15.2% (PhaseB), I L, B = 1260 A THDI fund, B = 16.0% (PhaseC), I L, C = 1560 A THDI fund, C = 13.2% (Neutral), I L, N = 120 A THDI fund, N = 20.6% (5.3) Power & Current are calculated by using CT Ratio 400:1 The total harmonic current for each phase is calculated as follows I H = THDI fund (i L (1+THDI 2 fund ))
8 93 I H, A = (1500 ( )) = A I H, B = (1260 ( )) = A I H, C = (1560 ( )) = A I H, N = (120 ( )) = A (5.4) Hence from the above calculation it is observed that the transformer contains a harmonics current of 200A per phase. Hence it is strongly recommended to reduce harmonics currents. THD results are obtained by FFT test. 5.5 HARMONIC ANALYSIS The case study conducted on 3 transformers in which one of them is of 1.5MVA, which drives a load of 50 kw with variable frequency. It is observed from Fig 5.1 that, the transformer is supplying a highly nonlinear load current of 25% THD. In which major harmonics are 5 th and 7 th Power Quality Evaluation Transformer rating :(1.5MVA) Electrical System = 415 V, 50 Hz, 3 Phase 3 Wires Apparent Power, S = 834 kva Real Power, P = 815 kw Reactive Power, Q =180 kvar Power Factor, p f = 0.98(lagging) (5.5)
9 94 Source Voltage, V (PhaseA), V = Vrms THDV fund, A = 4..5% (PhaseB), V B = Vrms THDV fund, B = 4.2% (PhaseC), V C = Vrms THDV fund, C = 4.3% (5.6) Load Current, I L (PhaseA), I L, A = 1260 A THDI fund, A = 25.2% (PhaseB), I L, B = 1260 A THDI fund, B = 24.5% (PhaseC), I L, C = 1140 A THDI fund, C = 25.0% (5.7) Power & Current are calculated by using CT Ratio 600:1 The total harmonic current for each phase is calculated as follows I H = THDIfund (i L (1+THDI fund 2 ) I H, A = (1260 ( )) = A I H, B = (1260 ( )) = A I H, C = 0.25 (1140 ( )) = A (5.8) Hence from the above calculation it is observed that the transformer contains a harmonics current of 300A per phase. Hence it is strongly recommended to reduce harmonic currents [44].THD results are obtained by FFT test. 5.6 MECHANISM OF ACTIVE HARMONIC FILTER A 100 Amp Active Harmonics filter may be installed in PDB2 of Plant III supplied by Tx1. The Plant III has got 30 Ring frames, each ring frame having VFD (Variable Frequency Drive) of 50 kw rating. 30 Ring frames have been grouped into four groups. A Power Distribution
10 95 Board (PDB) supports each group. PDB2 supports 8 numbers of ring frames. Single line diagram of the same installation is given below in Fig 5.9. They were facing a Problem of high current harmonics more than 25% in PDB2. Tripping of the Circuit breaker and higher temperature of cable and transformer (Tx1). The 100 Amp APF Units may be installed across the load of PDB2. VFD 8 Incomer V p I p V s I s Transformer Tx 1 Source point Is 1 I H I L VFD 2 VFD 1 PDB 2 Other loads PFC Solid state Harmonics filter Fig 5.9 Single Line Diagram of Active Filter Transformer: 4 MVA, 33 kv /440 V, /, PFC: power factor correction capacitors (50 kvar cap Bank) Solidstate harmonics filter rating: 415 V, 50 Hz, 3Ph3 wire, 100 Amp AHF. VFD Rating: Each VFD is of 50 kw, 440 V, 50 Hz (5.9)
11 96 Slight Distortion in current wave is, because of higher harmonics current presents in the system than the rating of the AHF installed at the time of measurement. Due to variation in load sometimesharmonics current exceeds rating of AHF & work in full correction mode voltage waveform. 5.7 RELATIVE STUDY Easy Installation. Installation without affecting the Production. Time required to install the AHF is less than 45 Min. User Friendly control Panel. Maintenance can be done easily without disturbing load efforts. Current transformers are to be connected at load side for Current Sensing. R, Y, & B terminals of AHF to be connected In shunt with the Load point. Current THD: Before AHF Installed Current THD (I THD ) was: 3031% After AHF Installed Current THD (I THD ) brought down to: 56%. Voltage THD: Before AHF Installed Current THD (I THD ) was: 67% After AHF Installed Current THD (I THD ) brought down to: 45%. Improved power factor (up to Unity) without power factor correction capacitors.[45]
12 97 Parameter Table 5.4 Variation of Parameters Before AHF installation (Cap Bank ON) After AHF installation (Cap Bank OFF) Avg Amp Avg kva Max kva kw pf kvar I THD 24.5% 6.5% V THD 6.4% 5.3% Voltage Table 5.5 Transformer Primary Side Parameter Before AHF Installation After AHF Installation I THD % V THD 2.7% 2.4% Voltage 33KV 33KV PF at TX Max kva Table 5.6 Transformer Secondary Side Parameter Before AHF After AHF Installation Installation I THD 20.5% 16% V THD 4.7% 4.2%
13 ACTIVE FILTER CONTROL ALGORITHM Three phase voltage source i a i b i c Nonlinear loads Active filter Fig 5.10 Block diagram of the system Source 3ph i source i comp i load V source P controller V dc i comp ref Coupling coil Inverter module DC bus Load 3ph i load Shunt Active Filter Fig 5.11 Shunt Active Filter Description of System configuration The system configuration of the proposed shunt active filter is shown in the Fig It consists of a threephase source, which is connected to a threephase nonlinear diode bridge rectifier circuit. The Shunt Active Power Filter is connected in shunt with the load. It consists
14 99 of the voltage source inverter in series with the inductor and capacitor. The triggering for the inverter circuit is given through the control circuit. The inverter can be implemented by IGBTs operating in hardswitched PulseWidth Modulation (PWM) mode to provide sufficient bandwidth for the filtering function Operating Principle Threephase bridge rectifier with RL loads (nonlinear loads) is connected to the three phase three wire distribution system as shown in Fig Due to the nature of the nonlinear loads, harmonics are injected in to the system. Shunt Active Power Filter is connected in shunt with the load to suppress the harmonics. The Voltage Source Inverter (VSI) generates a compensating harmonics current in to the phase conductors through the inductor and capacitor sets connected in series with it. The generated harmonics currents cancel each other with out affecting the fundamental part of the source current Control Strategy There are three stages in the active filtering technology. In the first stage the essentials voltage and current signals are sensed using power transformers and current transformers to gather accurate system information. In the second stage, compensating commands in terms of current or voltage levels are derived based on control methods and AF configuration. In the third stage of control, the gating signals for the solidstate devices of the AF are generated using PWM techniques. In this we have used the instantaneous pq theory for deriving the compensating signal. [46] Control Algorithm The generalized theory of the instantaneous reactive power in three phase circuits is also known as instantaneous power theory, or PQ theory. It is based on instantaneous values in
15 100 threephase power systems with or without neutral wire, and is valid for steady state or transitory operations, as well as for generator voltage and current waveforms. The pq theory consists of an algebraic transformation of the threephase voltages and currents in the abc coordinates to the  0 coordinates, followed by the calculation of the v 0 1/ 2 1/ 2 1/ 2 v a v = 2/3 11/21/2 v b v 0 3/23/2 v c (5.10) pq theory instantaneous power components. As explained above the first step in pq theory is to transfer the abc frame of voltage and currents into  0 coordinates. i 0 1/ 2 1/ 2 1/ 2 i a i = 2/3 11/21/2 i b i 0 3/23/2 i c (5.11) The instantaneous powers p and q are calculated using the equations given below p 0 = v 0 i 0 instantaneous zero sequence power. p = v i +v i instantaneous real power. q = v i v i instantaneous imaginary power
16 101 p v v i = q v v i (5.12) Where p = p + p ~ q = q + q ~ p 0 = p 0 + p ~ 0 p 0 = Mean value of the instantaneous zero sequence power corresponds to the energy per time unity which is transferred from the power supply to the load through the zero sequence components of voltage and current. p ~ 0 = Alternated value of the instantaneous zero sequence power. It means the energy per time unity is exchanged between the power supply and the load through the zero sequence components. The zerosequence power only exists in threephase system with neutral wire. Furthermore, the system must have unbalanced voltages and currents and/or 3 rd harmonics in both voltage and current of at least one phase. p = Mean value of the instantaneous real power, corresponds to the energy per time unity, which is transferred from power supply to the load, through abc coordinates, in a balanced way (it is the desired power component). p ~ = Alternated value of the instantaneous real power, it is the energy per time unity, that is exchanged between the power supply and the load, through abc coordinates. q = Instantaneous imaginary power, corresponds to the power that is exchanged between the phases of the load. This component does not imply any transference or exchange of energy between the power supply and the load, but is responsible for the existence of undesirable
17 102 currents, which circulates between the system phases. In the case of a balanced sinusoidal voltage supply and a balanced with or without harmonics, q(the mean value of the instantaneous imaginary power) is equal to the conventional reactive power (q=3.v.i 1.sin ) Vc 120 Vb 120 Va Power supply N Linear loads Balanced unbalanced Nonlinear loads Balanced unbalance Shunt Active power filter C V dc Fig 5.12 Shunt Active Filters with Linear Loads As in Fig 5.12, is usually desirable pq theory power component. The other quantities can be compensated using a shunt active filter. Can be compensated without the need of any power supply in the shunt active filter. This quantity is delivered from the power supply to the load through the active filter. This means that the energy previously transferred from the source to the load through the zero sequence components of voltage and current, is now delivered in a balanced way from the source phases. It is also concluded from Fig 5.12 that the active filter DC Bus is necessary to compensate input power P i and out put power p o, since these quantities must be stored in this component at one moment to be later delivered to the load. The instantaneous imaginary power (q), which includes the conventional reactive power, is compensated without the contribution of the DC Bus. This means that, the size of the DC
18 103 Bus does not dependent on the amount of reactive power to be compensated. The compensation reference currents in  0 components can be calculated by using the equations (4.13) & (5.14) i c i c = 1 v  v p  p 0 v 2 2 +v v v q (5.13) Since zero sequence current must be compensated, the reference compensation current in the 0 coordinate is i 0 itself. i c0 = i 0, In order to get the compensating currents in abc reference frame the inverse transformation of  0 to abc is applied. i ca 1/ i c0 i cb = 2/3 1/ 21/2 3/2 i c i cc 1/ 21/23/2 i c (5.14) Fig 5.13 Active & Reactive power control
19 Features of pq theory The above Fig 5.13 synthesizes the reference current calculations of instantaneous pq theory It is inherently a 3phase system theory It is based on instantaneous values, allowing excellent dynamic response Its calculations are relatively simple (it only includes algebraic expressions that can be Implemented using standard processors). It can be applied to any threephase system (balanced or unbalanced, with or without Harmonics in both voltages and currents) [47] 5.9 SIMULATION RESULTS The SIMUINK/MATLAB (version 7) is a highly developed graphical user interface simulation tool. It has proved instrumental in implementing the graphical based controller. The Simulation tool has been used to perform the modeling and simulation of the custom power controller for a wide range of operating conditions. The Simulation results of the proposed filter are discussed in this chapter. The Proposed scheme of Shunt Active Filter is shown in Fig For both with and without filter. The active filter is connected in parallel with the 3 phase supply. The load taken for the simulation is Diode and Thyristor bridge rectifier with RL load. The Tables 5.7 & 5.8 show the values of R and L for both diode and thyristor bridge rectifiers respectively.
20 105 Table 5.7 Parameters for Diode Bridge Load Resistance =2 ohms Inductance =1.5mH Load parameters Active filter parameters IGBT Inverter DC Bus = 900V Inverter Coupling Inductance/Phase =1.5mH Ripple Filter Parameters Rect./phase = 4 ohms Cap/phase =36 µf Cap/phase =72 µf Table 5.8 Parameters For Thyristor Bridge Rectifier Load Resistance =2 ohms Inductance =1.5mH Load parameters Active filter parameters IGBT Inverter DC Bus = 900V Inverter Coupling Inductance/Phase =1.5mH Ripple Filter Parameters Rect./phase = 4 ohms Cap/phase =36 µf Cap/phase =72 µf As explained in the control algorithm, there are basically three main steps in instantaneous pq theory. First step is converting the voltage and currents in ABC reference (stationary) frame into alpha beta zero sequence (which is also stationary) frame as shown in Fig 5.15.
21 106 Second step is to calculate the instantaneous real and reactive powers and extracting reference compensating currents for compensating the harmonic currents and reactive power at the source side of the system as shown in Fig 5.16 Third step is to generate the reference compensating current by using an IGBT based voltage source inverter as shown in Fig 5.14 The results waveform will depict the effectiveness of the active filtering algorithm. It can be observed from Fig 5.17 that the source current has become a pure sinusoidal wave and it has been observed form POWER GUI tool that source current THD has been reduced from 24% to 2%. This can be observed from Fig 5.18 that, load power oscillations are reduced with active filtering.
22 107 Fig 5.14 Simulated Diagram of Active Harmonic filter
23 108 Fig 5.15 Simulated Diagram for ABC to Alpha Beta ZeroTransforamtion Fig 5.16 Simulated Diagram for Reference current calculation
24 109 Fig 5.17 Source and load current waveforms (Time on xaxis, V s & I L on yaxis) Fig 5.18 Source and load power waveforms (Time on xaxis, P s & P L on yaxis) The same active filter is connected to thyristor based bridge rectifier which is containing more harmonics in current compared to the diode bridge rectifier as mentioned in Fig The current THD is reduced from around 44% to 3% hence the designed active filter is effective with high percentage of THD. The designed active filter is capable of reducing around 50 amps of harmonics current in load. The simulation diagram for Active harmonics filter with thyristor based bridge rectifier load is shown in Fig 5.19
25 110 Fig 5.19 Simulated diagram of Active harmonic filter with thyristor bridge load Fig 5.20 Shows that the load current waveform has been improved and the source becomes a pure sinusoidal current waveform. It can also be observed from Fig 2.21 that the power variation at the load side is reduced compared to source side, in addition to this the active harmonics filter is capable of supplying the reactive power to the load and power factor at the source side is also increased.
26 111 Fig 5.20 Source and load current waveforms (Time on xaxis, I s & I L on yaxis) Fig 5.21 Source voltage and power waveforms (Time on xaxis, V s & P on yaxis)
27 CONCLUSION The purpose of this chapter is to review the results obtained during the present work before proceeding with the conclusions of the work done, the objective of the thesis stated in the first chapter are recalled. The primary objective of this chapter is to model and develop the proposed new Shunt Active Power Filter for the current harmonics suppression using SIMULINK/MATLAB (Version 7) simulation tool. The model of the proposed new Shunt Active Power Filter is realized. The developed new Shunt Active Power Filtering technology is implemented for a system feeding a nonlinear load. It is simulated using the highly developed graphic tool SIMULINK available in MATLAB. The results reveal that the proposed new Shunt Active Filtering technology is simple and effective and is suitable for practical applications. Table 5.9 Harmonic Distortion of Load Voltage Dead V ab _50Hz THD HS H7 8kHz Time(µs) V(rms) (%) (%) (%) (%) From Table 5.10, it is observed that by the suppression of voltage and current harmonics using new active filtering technology, the power quality can be improved as discussed in the various chapters.
Sinusoidal Current Control based Shunt Active Power Filter for Current Harmonics Reduction
Sinusoidal Current Control based Shunt Active Power Filter for Current Harmonics Reduction Anju Yadav 1, K. Narayanan 2, Binsy Joseph 3 1, 2, 3 Fr. Conceicao Rodrigues College of Engineering, Mumbai, India
More informationSHUNT ACTIVE POWER FILTER
75 CHAPTER 4 SHUNT ACTIVE POWER FILTER Abstract A synchronous logic based Phase angle control method pulse width modulation (PWM) algorithm is proposed for three phase Shunt Active Power Filter (SAPF)
More informationHARMONICS THE BASICS H A R M O N I C M I T I G A T I O N A N D D I S P L A C E M E N T P O W E R F A C T O R C O R R E C T I O N
HARMONICS THE BASICS H A R M O N I C M I T I G A T I O N A N D D I S P L A C E M E N T P O W E R F A C T O R C O R R E C T I O N Harmonic Basics 3 rd Harmonic Fundamental 5 t1h Harmonic 7 th Harmonic Harmonic
More informationCHAPTER 6 UNIT VECTOR GENERATION FOR DETECTING VOLTAGE ANGLE
98 CHAPTER 6 UNIT VECTOR GENERATION FOR DETECTING VOLTAGE ANGLE 6.1 INTRODUCTION Process industries use wide range of variable speed motor drives, air conditioning plants, uninterrupted power supply systems
More informationThree Phase PFC and Harmonic Mitigation Using Buck Boost Converter Topology
Three Phase PFC and Harmonic Mitigation Using Buck Boost Converter Topology Riya Philip 1, Reshmi V 2 Department of Electrical and Electronics, Amal Jyothi College of Engineering, Koovapally, India 1,
More informationPower Quality Improvement using Shunt Passive Filter
Power Quality Improvement using Shunt Passive Filter Assistant Professor, Department of Electrical Engineering Bhutta Group of Institutions, India Abstract: The electricity supply would, ideally, show
More informationControl Of Shunt Active Filter Based On Instantaneous Power Theory
B.Pragathi Department of Electrical and Electronics Shri Vishnu Engineering College for Women Bhimavaram, India Control Of Shunt Active Filter Based On Instantaneous Power Theory G.Bharathi Department
More informationChapter 2 Shunt Active Power Filter
Chapter 2 Shunt Active Power Filter In the recent years of development the requirement of harmonic and reactive power has developed, causing power quality problems. Many power electronic converters are
More informationSimulation Results of a Shunt Active Power Filter with Control Based on pq Theory
Simulation Results of a Shunt Active Power Filter with Control Based on pq Theory Emílio F. Couto, Júlio S. Martins, João L. Afonso Department of Industrial Electronic University of Minho Campus de Azurém
More informationHarmonics Reduction of 3 Phase Diode Bridge Rectifier by Implementing PQ Theory with Active Filter
IJSRD  International Journal for Scientific Research & Development Vol. 4, Issue 07, 2016 ISSN (online): 23210613 Harmonics Reduction of 3 Phase Diode Bridge Rectifier by Implementing PQ Theory with
More informationPIVPI Based Current Control Strategy to Improve the Performance of Shunt Active Power Filter
PIVPI Based Current Control Strategy to Improve the Performance of Shunt Active Power Filter B.S.Nalina 1 Ms.V.J.Vijayalakshmi 2 Department Of EEE Department Of EEE 1 PG student,skcet, Coimbatore, India
More informationHow adjustable speed drives affect power distribution
How adjustable speed drives affect power distribution Application Note Adjustable speed drives (ASDs) can be both a source and a victim of poor power quality. ASDs as victim loads Although ASDs are usually
More informationHarmonics Reduction using 4Leg Shunt Active Power Filters
Harmonics Reduction using 4Leg Shunt Active Power Filters K Srinivas Assistant Professor & Department of EEE & JNTUH CEJ Telangana, India. Abstract Harmonics in power system are caused by highly nonlinear
More informationINSTANTANEOUS POWER CONTROL OF DSTATCOM FOR ENHANCEMENT OF THE STEADYSTATE PERFORMANCE
INSTANTANEOUS POWER CONTROL OF DSTATCOM FOR ENHANCEMENT OF THE STEADYSTATE PERFORMANCE Ms. K. Kamaladevi 1, N. Mohan Murali Krishna 2 1 Asst. Professor, Department of EEE, 2 PG Scholar, Department of
More informationPower Quality Improvement of NonLinear Load by Using Instantaneous PQ Theory
Power Quality Improvement of NonLinear Load by Using Instantaneous PQ Theory 1 R.V.L. Narayana Divakar, 2 P.Kishore, 3 CH.Ravi Kumar, 4 V.Madhu Kishore, 5 V.Pradeep Kumar 1 Assistant Professor, 2,3,4,5
More informationPower Conditioning Equipment for Improvement of Power Quality in Distribution Systems M. Weinhold R. Zurowski T. Mangold L. Voss
Power Conditioning Equipment for Improvement of Power Quality in Distribution Systems M. Weinhold R. Zurowski T. Mangold L. Voss Siemens AG, EV NP3 P.O. Box 3220 91050 Erlangen, Germany email: Michael.Weinhold@erls04.siemens.de
More informationCASE STUDY. Implementation of Active Harmonic Filters at Ford Motor Company SA Silverton Plant
CASE STUDY Implementation of Ford Motor Company SA Silverton Plant 1 SCENARIO Ford Motor Company is a global automotive and mobility company based in Dearborn, Michigan. Ford Motor Company of Southern
More informationDesign and Simulation of Three Phase Shunt Active Power Filter Using SRF Theory
Advance in Electronic and Electric Engineering. ISSN 22311297, Volume 3, Number 6 (2013), pp. 651660 Research India Publications http://www.ripublication.com/aeee.htm Design and Simulation of Three Phase
More informationCHAPTER 4 MULTILEVEL INVERTER BASED DVR SYSTEM
64 CHAPTER 4 MULTILEVEL INVERTER BASED DVR SYSTEM 4.1 INTRODUCTION Power electronic devices contribute an important part of harmonics in all kind of applications, such as power rectifiers, thyristor converters
More informationMITIGATION OF VOLTAGE SAGS/SWELLS USING DYNAMIC VOLTAGE RESTORER (DVR)
VOL. 4, NO. 4, JUNE 9 ISSN 89668 69 Asian Research Publishing Network (ARPN). All rights reserved. MITIGATION OF VOLTAGE SAGS/SWELLS USING DYNAMIC VOLTAGE RESTORER (DVR) Rosli Omar and Nasrudin Abd Rahim
More information5DESIGN PARAMETERS OF SHUNT ACTIVE FILTER FOR HARMONICS CURRENT MITIGATION
5DESIGN PARAMETERS OF SHUNT ACTIE FILTER FOR HARMONICS CURRENT MITIGATION Page 59 A.H. Budhrani 1*, K.J. Bhayani 2, A.R. Pathak 3 1*, 2, 3 Department of Electrical Engineering,..P. Engineering College
More informationPower Quality improvement of a three phase four wire system using UPQC
International Research Journal of Engineering and Technology (IRJET) eissn: 239556 Volume: 2 Issue: 4 July215 www.irjet.net pissn: 239572 Power Quality improvement of a three phase four wire system
More informationCurrent Control Technique for Three Phase Shunt Active Power Filter by Using Adaptive Hysteresis Current Controller
Current Control Technique for Three Phase Shunt Active Power Filter by Using Adaptive Hysteresis Current Controller Rekha Soni Department of EEE C.V.R.U. Kota, Bilaspur (C.G.) soni.rekha25@gmail.com Durga
More informationHarmonics Elimination Using Shunt Active Filter
Harmonics Elimination Using Shunt Active Filter Satyendra Gupta Assistant Professor, Department of Electrical Engineering, Shri Ramswaroop Memorial College of Engineering and Management, Lucknow, India.
More informationPower Quality Improvement of Distribution Network for NonLinear Loads using Inductive Active Filtering Method Suresh Reddy D 1 Chidananda G Yajaman 2
IJSRD  International Journal for Scientific Research & Development Vol. 3, Issue 03, 2015 ISSN (online): 23210613 Power Quality Improvement of Distribution Network for NonLinear Loads using Inductive
More informationActive Harmonic Filter (AF3)
Active Harmonic Filter (AF3) Active Harmonic Filter Improving the Efficiency and Life of System by use of Digital Active Power Conditioner HARMONICS 50 Hz, fundamental 100 Hz, 2nd Harmonic 150 Hz, 3rd
More informationDRIVE FRONT END HARMONIC COMPENSATOR BASED ON ACTIVE RECTIFIER WITH LCL FILTER
DRIVE FRONT END HARMONIC COMPENSATOR BASED ON ACTIVE RECTIFIER WITH LCL FILTER P. SWEETY JOSE JOVITHA JEROME Dept. of Electrical and Electronics Engineering PSG College of Technology, Coimbatore, India.
More informationPower Quality enhancement of a distribution line with DSTATCOM
ower Quality enhancement of a distribution line with DSTATCOM Divya arashar 1 Department of Electrical Engineering BSACET Mathura INDIA Aseem Chandel 2 SMIEEE,Deepak arashar 3 Department of Electrical
More informationLiterature Review for Shunt Active Power Filters
Chapter 2 Literature Review for Shunt Active Power Filters In this chapter, the in depth and extensive literature review of all the aspects related to current error space phasor based hysteresis controller
More information2020 P a g e. Figure.2: Line diagram of series active power filter.
Power Quality Improvement By UPQC Using ANN Controller Saleha Tabassum 1, B.Mouli Chandra 2 (Department of Electrical & Electronics Engineering KSRM College of Engineering, Kadapa.) (Asst. Professor Dept
More informationPower Quality Improvement Using Hybrid Power Filter Based On Dual Instantaneous Reactive Power Theory With Hysteresis Current Controller
Power Quality Improvement Using Hybrid Power Filter Based On Dual Instantaneous Reactive Power Theory With Hysteresis Current Controller J.Venkatesh 1, K.S.S.Prasad Raju 2 1 Student SRKREC, India, venki_9441469778@yahoo.com
More informationA MATLABSIMULINK APPROACH TO SHUNT ACTIVE POWER FILTERS
A MATLABSIMULINK APPROACH TO SHUNT ACTIVE POWER FILTERS George Adam, Alina G. Stan (Baciu) and Gheorghe Livinţ Department of Electrical Engineering Technical University of Iaşi 700050, Iaşi, Romania Email:
More informationCHAPTER 5 DESIGN OF DSTATCOM CONTROLLER FOR COMPENSATING UNBALANCES
86 CHAPTER 5 DESIGN OF DSTATCOM CONTROLLER FOR COMPENSATING UNBALANCES 5.1 INTRODUCTION Distribution systems face severe power quality problems like current unbalance, current harmonics, and voltage unbalance,
More informationEffective Harmonic Mitigation with Active Filters
Advancing Power Quality White Paper Effective Harmonic Mitigation with Active Filters Written by: Ian Wallace Variable Speed Drive with no Harmonic Mitigation Industry standard variable speed drives, with
More informationISSN: Page 20. International Journal of Engineering Trends and Technology Volume2Issue32011
Design of Shunt Active Power Filter to eliminate the harmonic currents and to compensate the reactive power under distorted and or imbalanced source voltages in steady state Sangu Ravindra #1, Dr.V.C.Veera
More informationHARMONIC ELIMINATION IN THREE PHASE SYSTEM BY MEANS OF A SHUNT ACTIVE FILTER
HARMONIC ELIMINATION IN THREE PHASE SYSTEM BY MEANS OF A SHUNT ACTIVE FILTER Bhargav R. Gamit 1, Sanjay R. Vyas 2 1PG Scholar, EE Dept., LDRPITR, Gandhinagar, Gujarat, India. 2Head of Department, EE Dept.,
More informationDesign of Shunt Active Power Filter by using An Advanced Current Control Strategy
Design of Shunt Active Power Filter by using An Advanced Current Control Strategy K.Sailaja 1, M.Jyosthna Bai 2 1 PG Scholar, Department of EEE, JNTU Anantapur, Andhra Pradesh, India 2 PG Scholar, Department
More informationImplementation of SRF based Multilevel Shunt Active Filter for Harmonic Control
International Journal of Engineering Research and Development eissn: 2278067X, pissn: 2278800X, www.ijerd.com Volume 3, Issue 8 (September 2012), PP. 1620 Implementation of SRF based Multilevel Shunt
More informationPower Quality improvement with Shunt Active Power filter using pq control technique
Power Quality improvement with Shunt Active Power filter using pq control technique Sumit Kumar 1, Dr.Anju Gupta 2, 1M.Tech Scholar,Power System YMCAUST,Faridabad, 2(Associate Prof.) Electrical Department
More informationCHAPTER 4 POWER QUALITY AND VAR COMPENSATION IN DISTRIBUTION SYSTEMS
84 CHAPTER 4 POWER QUALITY AND VAR COMPENSATION IN DISTRIBUTION SYSTEMS 4.1 INTRODUCTION Now a days, the growth of digital economy implies a widespread use of electronic equipment not only in the industrial
More informationPQ for Industrial Benchmarking with various methods to improve. Tushar Mogre.
General PQ: Power Quality has multiple issues involved. Thus, need to have some benchmarking standards. Very little is spoken about the LT supply installation within an industry. There is need to understand
More informationIJSTE  International Journal of Science Technology & Engineering Volume 2 Issue 12 June 2016 ISSN (online): X
IJSTE  International Journal of Science Technology & Engineering Volume 2 Issue 12 June 2016 ISSN (online): 2349784X A Synchronous Reference Frame TheorySpace Vector Modulation (SRF SPVM) based Active
More informationIMPORTANCE OF VSC IN HVDC
IMPORTANCE OF VSC IN HVDC Snigdha Sharma (Electrical Department, SIT, Meerut) ABSTRACT The demand of electrical energy has been increasing day by day. To meet these high demands, reliable and stable transmission
More informationINVESTIGATION OF HARMONIC DETECTION TECHNIQUES FOR SHUNT ACTIVE POWER FILTER
IOSR Journal of Electronics & Communication Engineering (IOSRJECE) ISSN(e) : 22781684 ISSN(p) : 2320334X, PP 6873 www.iosrjournals.org INVESTIGATION OF HARMONIC DETECTION TECHNIQUES FOR SHUNT ACTIVE
More informationModified ThreePhase FourWire UPQC Topology with Reduced DCLink Voltage Rating
Modified ThreePhase FourWire UPQC Topology with Reduced DCLink Voltage Rating P.Ankineedu Prasad 1, N.Venkateswarlu 2. V.Ramesh 3, L.V.Narasimharao 4 Assistant Professor 12 & Professor 4& Research Scholar
More informationPower Quality Analysis: A Study on OffLine UPS Based System
Power Quality Analysis: A Study on OffLine UPS Based System P.K.DHAL Department of Electrical and Electronics Engineering VelTech Dr.RR&Dr.SR Technical University # 42 Avadi VelTech Road, Chennai62
More informationPERFORMANCE ANALYSIS OF SVPWM AND FUZZY CONTROLLED HYBRID ACTIVE POWER FILTER
International Journal of Electrical and Electronics Engineering Research (IJEEER) ISSN 2250155X Vol. 3, Issue 2, Jun 2013, 309318 TJPRC Pvt. Ltd. PERFORMANCE ANALYSIS OF SVPWM AND FUZZY CONTROLLED HYBRID
More informationHarmonic Solutions in Electrical Systems. Raed Odeh Application Specialist  Power Quality & Electrical Distribution
Harmonic Solutions in Electrical Systems Raed Odeh Application Specialist  Power Quality & Electrical Distribution Agenda I. Harmonic Basics II.Harmonic Mitigation Solutions III.Case Study 2 Harmonic
More informationInternational Journal of Advance Research in Engineering, Science & Technology
Impact Factor (SJIF): 3.632 International Journal of Advance Research in Engineering, Science & Technology eissn: 23939877, pissn: 23942444 (Special Issue for ITECE 2016) Harmonic Mitigation of Fluctuating
More informationKINGS COLLEGE OF ENGINEERING DEPARTMENT OF ELECTRICAL AND ELECTRONICS ENGINEERING QUESTION BANK UNIT I BASIC CIRCUITS ANALYSIS PART A (2MARKS)
KINGS COLLEGE OF ENGINEERING DEPARTMENT OF ELECTRICAL AND ELECTRONICS ENGINEERING QUESTION BANK YEAR / SEM : I / II SUBJECT CODE & NAME : EE 1151 CIRCUIT THEORY UNIT I BASIC CIRCUITS ANALYSIS PART A (2MARKS)
More informationPOWER QUALITY IMPROVEMENT BY USING ACTIVE POWER FILTERS
POWER QUALITY IMPROVEMENT BY USING ACTIVE POWER FILTERS Ramesh Kumar V 1, Dr. Dalvinder Kaur Mangal 2 1 Research Scholar, Department of Electrical Engineering, Sunrise University, Alwar 2 Asso. Prof.,
More informationCHAPTER 3 H BRIDGE BASED DVR SYSTEM
23 CHAPTER 3 H BRIDGE BASED DVR SYSTEM 3.1 GENERAL The power inverter is an electronic circuit for converting DC power into AC power. It has been playing an important role in our daily life, as well as
More information16th NATIONAL POWER SYSTEMS CONFERENCE, 15th17th DECEMBER,
16th NATONAL POWER SYSTEMS CONFERENCE, 15th17th DECEMBER, 2010 289 Single phase Active harmonic filters for Harmonic elimination and Power Factor correction for Distributed loads Vinod Gupta, Kamlesh
More informationImprovement of Power Quality in Distribution System using DSTATCOM With PI and PID Controller
Improvement of Power Quality in Distribution System using DSTATCOM With PI and PID Controller Phanikumar.Ch, M.Tech Dept of Electrical and Electronics Engineering Bapatla Engineering College, Bapatla,
More informationMulti Level Inverter Based Active Power Filter for Harmonic Reduction
Multi Level Inverter Based Active Power Filter for Harmonic Reduction K Siva Gopi Raju Department of Electrical and Electronics Engineering, Andhra University, Visakhapatnam, Andhra Pradesh 530003, India.
More informationSynchronous Reference Frame Theory For Nonlinear Loads using Matlab Simulink
Synchronous Reference Frame Theory For Nonlinear Loads using Matlab Simulink Parag Datar 1, Vani Datar 2, S. B. Halbhavi 3, S G Kulkarni 4 1 Assistant Professor, Electrical and Electronics Department,
More informationHigh Voltage DC Transmission 2
High Voltage DC Transmission 2 1.0 Introduction Interconnecting HVDC within an AC system requires conversion from AC to DC and inversion from DC to AC. We refer to the circuits which provide conversion
More informationKanuru; Krishna (Dt); A.P, India. DOI: / Page. 1 G. Aruna Jyothi, 2 DR. P. V. R. L.
IOSR Journal of Electrical and Electronics Engineering (IOSRJEEE) eissn: 78676,pISSN: , Volume, Issue Ver. II (Jan Feb. 5), PP 6874 www.iosrjournals.org Implementation of Instantaneous Reactive Power
More informationISSN Vol.03,Issue.07, August2015, Pages:
WWW.IJITECH.ORG ISSN 23218665 Vol.03,Issue.07, August2015, Pages:12761281 Comparison of an Active and Hybrid Power Filter Devices THAKKALAPELLI JEEVITHA 1, A. SURESH KUMAR 2 1 PG Scholar, Dept of EEE,
More informationAnalysis of Advanced Techniques to Eliminate Harmonics in AC Drives
Analysis of Advanced Techniques to Eliminate Harmonics in AC Drives Amit P. Wankhade 1, Prof. C. Veeresh 2 2 Assistant Professor, MIT mandsour Email amitwankhade03@gmail.com Abstract Variable speed AC
More informationCHAPTER 4 PVUPQC BASED HARMONICS REDUCTION IN POWER DISTRIBUTION SYSTEMS
66 CHAPTER 4 PVUPQC BASED HARMONICS REDUCTION IN POWER DISTRIBUTION SYSTEMS INTRODUCTION The use of electronic controllers in the electric power supply system has become very common. These electronic
More informationR. W. Erickson. Department of Electrical, Computer, and Energy Engineering University of Colorado, Boulder
R. W. Erickson Department of Electrical, Computer, and Energy Engineering University of Colorado, Boulder 16.4. Power phasors in sinusoidal systems Apparent power is the product of the rms voltage and
More informationHarmonic Immunity And Power Factor Correction By Instantaneous Power Control Of DSTATCOM
Harmonic Immunity And Power Factor Correction By Instantaneous Power Control Of DSTATCOM B.Veerraju M.Tech Student (PE&ED) MIST Sathupally, Khammam Dist, India M.Lokya Assistant Professor in EEE Dept.
More informationHarmonic Distortion and Variable Frequency Drives
Harmonic Distortion and Variable Frequency Drives Definitions Variable Frequency Drives (VFDs); sometimes referred to as variable speed drives. Harmonic Distortion is a measure of the amount of deviation
More informationCHAPTER 3 IMPROVEMENT OF LOAD POWER FACTOR USING FACTS CONTROLLERS
40 CHAPTER 3 IMPROVEMENT OF LOAD POWER FACTOR USING FACTS CONTROLLERS 3.1 INTRODUCTION The low power factor effects on transmission line, switchgear, transformers etc. It is observed that if the power
More informationCompensation of Distribution Feeder Loading With Power Factor Correction by Using DSTATCOM
Compensation of Distribution Feeder Loading With Power Factor Correction by Using DSTATCOM N.Shakeela Begum M.Tech Student P.V.K.K Institute of Technology. Abstract This paper presents a modified instantaneous
More informationVolume I Issue VI 2012 September2012 ISSN
A 24pulse STATCOM Simulation model to improve voltage sag due to starting of 1 HP InductionMotor Mr. Ajay Kumar Bansal 1 Mr. Govind Lal Suthar 2 Mr. Rohan Sharma 3 1 Associate Professor, Department of
More informationStudy of Power Factor Correction in Single Phase ACDC Converter
Avneet Kaur, Prof. S.K Tripathi, Prof. P. Tiwari 89 Study of Power Factor Correction in Single Phase ACDC Converter Avneet Kaur, Prof. S.K Tripathi, Prof. P. Tiwari Abstract: This paper is regarding power
More informationINTERNATIONAL JOURNAL OF PURE AND APPLIED RESEARCH IN ENGINEERING AND TECHNOLOGY
INTERNATIONAL JOURNAL OF PURE AND APPLIED RESEARCH IN ENGINEERING AND TECHNOLOGY A PATH FOR HORIZING YOUR INNOVATIVE WORK IMPROVED CONTROL METHOD OF GUPQC UNDER DISTORTED AND UNBALANCED LOAD CONDITION
More informationA Novel Power Factor Correction Rectifier for Enhancing Power Quality
International Journal of Power Electronics and Drive System (IJPEDS) Vol. 6, No. 4, December 2015, pp. 772~780 ISSN: 20888694 772 A Novel Power Factor Correction Rectifier for Enhancing Power Quality
More informationAnalysis, Modeling and Simulation of Dynamic Voltage Restorer (DVR)for Compensation of Voltage for sagswell Disturbances
IOSR Journal of Electrical and Electronics Engineering (IOSRJEEE) eissn: 22781676,pISSN: 23203331, Volume 9, Issue 3 Ver. I (May Jun. 2014), PP 3641 Analysis, Modeling and Simulation of Dynamic Voltage
More informationThree Phase Active Shunt Power Filter with Simple Control in PSIM Simulation
Three Phase Active Shunt Power Filter with Simple Control in PSIM Simulation A.Jeraldine viji Associate Professor, EEE department, Mailam Engineering College, Tamil Nadu Email: jeraldrovan@gmail.com Dr.M.Sudhakaran
More informationSimulation and Comparison of DVR and DSTATCOM Used For Voltage Sag Mitigation at Distribution Side
Simulation and Comparison of DVR and DSTATCOM Used For Voltage Sag Mitigation at Distribution Side 1 Jaykant Vishwakarma, 2 Dr. Arvind Kumar Sharma 1 PG Student, High voltage and Power system, Jabalpur
More informationExperimental Results of a SinglePhase Shunt Active Filter Prototype with Different Switching Techniques
ISIE 007  IEEE International Symposium on Industrial Electronics Vigo, Espanha, 47 Junho de 007, ISBN: 144407559 Experimental Results of a SinglePhase Shunt Active Filter Prototype with Different
More informationLoad Compensation at a Reduced DC Link Voltage by Using DSTATCOM with NonStiff Source
International Journal of Emerging Engineering Research and Technology Volume 2, Issue 3, June 2014, PP 220229 ISSN 23494395 (Print) & ISSN 23494409 (Online) Load Compensation at a Reduced DC Link Voltage
More informationCHAPTER 3 COMBINED MULTIPULSE MULTILEVEL INVERTER BASED STATCOM
CHAPTER 3 COMBINED MULTIPULSE MULTILEVEL INVERTER BASED STATCOM 3.1 INTRODUCTION Static synchronous compensator is a shunt connected reactive power compensation device that is capable of generating or
More informationMulticonverter Unified PowerQuality Conditioning System: MCUPQC T.Charan Singh, L.Kishore, T.Sripal Reddy
Multiconverter Unified PowerQuality Conditioning System: MCUPQC T.Charan Singh, L.Kishore, T.Sripal Reddy Abstract This paper presents a new unified powerquality conditioning system (MCUPQC), capable
More informationEnhancement of Power Quality using active power filter in a MediumVoltage Distribution Network switching loads
Vol.2, Issue.2, MarApr 2012 pp431435 ISSN: 22496645 Enhancement of Power Quality using active power filter in a MediumVoltage Distribution Network switching loads M. CHANDRA SEKHAR 1, B. KIRAN BABU
More informationDESIGN AND DEVELOPMENT OF ACTIVE POWER FILTER FOR HARMONIC MINIMIZATION USING SYNCHRONOUS REFERENCE FRAME (SRF)
DESIGN AND DEVELOPMENT OF ACTIVE POWER FILTER FOR HARMONIC MINIMIZATION USING SYNCHRONOUS REFERENCE FRAME (SRF) Rosli Omar, Mohammed Rasheed, Zheng Kai Low and Marizan Sulaiman Universiti Teknikal Malaysia
More informationEnhancement of Power Quality Using Advanced Series Active Power Filters
Enhancement of Power Quality Using Advanced Series Active Power Filters Manoj siva kumar 1, P.Rayalakshmi 2 Associate Professor, Dept. of EEE, PBRVITS, Kavali, SPSR Nellore, A.P, India 1 M.Tech Student,
More informationp. 1 p. 6 p. 22 p. 46 p. 58
Comparing power factor and displacement power factor corrections based on IEEE Std. 182002 Harmonic problems produced from the use of adjustable speed drives in industrial plants : case study Theory for
More informationPower Factor and Power Factor Correction
Power Factor and Power Factor Correction Long gone are the days when only engineers that worked with large electric motors and high power electric loads need worry about power factor. The introduction
More informationPERFORMANCE EVALUATION OF THREE PHASE SCALAR CONTROLLED PWM RECTIFIER USING DIFFERENT CARRIER AND MODULATING SIGNAL
Journal of Engineering Science and Technology Vol. 10, No. 4 (2015) 420433 School of Engineering, Taylor s University PERFORMANCE EVALUATION OF THREE PHASE SCALAR CONTROLLED PWM RECTIFIER USING DIFFERENT
More informationCHAPTER 2 A SERIES PARALLEL RESONANT CONVERTER WITH OPEN LOOP CONTROL
14 CHAPTER 2 A SERIES PARALLEL RESONANT CONVERTER WITH OPEN LOOP CONTROL 2.1 INTRODUCTION Power electronics devices have many advantages over the traditional power devices in many aspects such as converting
More informationConventional PaperII2011 Part1A
Conventional PaperII2011 Part1A 1(a) (b) (c) (d) (e) (f) (g) (h) The purpose of providing dummy coils in the armature of a DC machine is to: (A) Increase voltage induced (B) Decrease the armature resistance
More informationImproving the Power Factor Correction in the Presence of Harmonics by Reducing the Effect of Resonance and Harmonics
Indonesian Journal of Electrical Engineering and Computer Science Vol. 3, No. 2, August 2016, pp. 282 ~ 295 DOI: 10.11591/ijeecs.v3.i2.pp282295 282 Improving the Power Factor Correction in the Presence
More informationDesign and Simulation of DVR Used For Voltage Sag Mitigation at Distribution Side
Design and Simulation of DVR Used For Voltage Sag Mitigation at Distribution Side Jaykant Vishwakarma 1, Dr. Arvind Kumar Sharma 2 1 PG Student, High voltage and Power system, Jabalpur Engineering College,
More informationCHAPTER 4 HARMONICS AND POWER FACTOR
4.1 Harmonics CHAPTER 4 HARMONICS AND POWER FACTOR In this research a comparative study of practical aspects of mixed use of diode and Thyristor converter technologies in Aluminium Smelters has been carried
More informationARE HARMONICS STILL A PROBLEM IN DATA CENTERS? by Mohammad Al Rawashdeh, Lead Consultant, Data Center Engineering Services
ARE HARMONICS STILL A PROBLEM IN DATA CENTERS? by Mohammad Al Rawashdeh, Lead Consultant, Data Center Engineering Services edarat group INTRODUCTION Harmonics are a mathematical way of describing distortion
More informationPSPWM Control Strategy and SRF Method of Cascaded HBridge MLI based DSTATCOM for Enhancement of Power Quality
PSPWM Control Strategy and SRF Method of Cascaded HBridge MLI based DSTATCOM for Enhancement of Power Quality P.Padmavathi, M.L.Dwarakanath, N.Sharief, K.Jyothi Abstract This paper presents an investigation
More informationImplementation of a low cost series compensator for voltage sags
J.L. Silva Neto DEEUFRJ luizneto@dee.ufrj.br R.M. Fernandes COPPEUFRJ rodrigo@coe.ufrj.br D.R. Costa COPPEUFRJ diogo@coe.ufrj.br L.G.B. Rolim DEE,COPPEUFRJ rolim@dee.ufrj.br M. Aredes DEE,COPPEUFRJ
More informationHYSTERESIS CONTROL FOR CURRENT HARMONICS SUPPRESSION USING SHUNT ACTIVE FILTER. Rajesh Kr. Ahuja
HYSTERESIS CONTROL FOR CURRENT HARMONICS SUPPRESSION USING SHUNT ACTIVE FILTER Rajesh Kr. Ahuja 1, Aasha Chauhan 2, Sachin Sharma 3 Rajesh Kr. Ahuja Faculty, Electrical & Electronics Engineering Dept.
More informationA Review on Simulation and Implementation of Thyristor controlled reactor and Shunt Hybrid Power Filter
A Review on Simulation and Implementation of Thyristor controlled reactor and Shunt Hybrid Power Filter Swapnil S. Motaphale Affiliation TSSM S BSCOER, Pune ME Electrical (Power System) Savitribai Phule
More informationTechnical Report. Zero Reactive Power Passive Current Harmonic Filter (ZRPPCHF) (In House Case Study) Prepared by. Dr. V. R. Kanetkar.
Technical Report on Zero Reactive Power Passive Current Harmonic Filter (ZRPPCHF) (In House Case Study) Prepared by Dr. V. R. Kanetkar (February 2015) Shreem Electric Limited (Plot No. 4346, L. K. Akiwate
More informationChapter 4. Hybrid series active filter. 4.1 Introduction
Chapter 4 Hybrid series active filter 4.1 Introduction The lowest harmonics in the source current spectrum of a 12pulse converter are theoretically the 11 th and the 13 th harmonics but some residual
More informationInvestigation of DStatcom Operation in Electric Distribution System
J. Basic. Appl. Sci. Res., (2)29297, 2 2, TextRoad Publication ISSN 29434 Journal of Basic and Applied Scientific Research www.textroad.com Investigation of DStatcom Operation in Electric Distribution
More informationMitigation of Flicker Sources & Power Quality Improvement by Using Cascaded MultiLevel Converter Based DSTATCOM
Mitigation of Flicker Sources & Power Quality Improvement by Using Cascaded MultiLevel Converter Based DSTATCOM 1 Siddartha A P, 2 B Kantharaj, 3 Poshitha B 1 PG Scholar, 2 Associate Professor, 3 Assistant
More informationHigh Power Factor Bridgeless SEPIC Rectifier for Drive Applications
High Power Factor Bridgeless SEPIC Rectifier for Drive Applications Basheer K 1, Divyalal R K 2 P.G. Student, Dept. of Electrical and Electronics Engineering, Govt. College of Engineering, Kannur, Kerala,
More informationControl of Shunt Active Power Filter for Improvement of Power Quality
Available Online at www.ijcsmc.com International Journal of Computer Science and Mobile Computing A Monthly Journal of Computer Science and Information Technology ISSN 232 88X IMPACT FACTOR: 6.17 IJCSMC,
More informationActive Harmonics Filtering of Distributed AC System
Active Harmonics Filtering of Distributed AC System M.S.Priya M.Sivaram Krishnan S.Sri ragavi P.G Scholar, Dept. of EEE P.G Scholar, Dept. of ECE P.G Scholar, Dept. of EEE Dr.Sivanthi Aditanar College
More information