1 Operating Instructions Controller wms-4/4i II for the ultrasonic sensors of the wms series *B2885*
2 Front panel Legend LED»OFF«LED»ON«1»UP«button 2»DOWN«button 3»ENTER«button 4 Green LEDs»NEAR/FAR«5 Green LEDs channel characteristic 6 Slider switch»scan/sync«7 Green LEDs for type of sensor 8 Yellow LEDs for indicating channel Fig. 1: Dimensions Fig. 2 Controls and LEDs showing sensors connected 2
3 Contents Contents 1 Description of unit Important advice concerning installation and use Installation Setting-up Operation Normal mode Setting up the reference channel (option) Programming a channel of the controller Copying settings Activating/Deactivating a channel Technical Specification Indicator mode Optional SHIFT mode Programming
4 Description of unit 1 Description of unit Please refer to the technical specification for details of the controller and the wms series data sheet for details of the sensors. The wms-4/4i II controller is designed for connecting up to four ultrasonic sensors of the wms series. The sensors are controlled and signals evaluated centrally in the contro l l e r. There f o re, only the robust sensors (all complying with class of pro t e c- tion IP 65) are subjected to the (sometimes) tough conditions of the working enviro n m e n t. The controller (class of protection IP 20), which c o n t rols the sensors and evaluates the signals, is accommodated safely in an electrical cabinet. 4 The analogue signals are determined by ultrasonic measurement in the controller. The sensor emits a brief sound pulse (see Fig. 3). This pulse propagates in the air and is reflected back from an object as an echo. The wms-4/4i II measures the time taken between emitting the signal and receiving the echo. From this propagation time, the controller determines an analogue signal proportional to the distance (rising: ma, or falling: ma). Fig. 3: Ultrasonic measurement
5 Description of unit Fig. 4: Analogue signal proportional to distance 5 Various wms sensors can be operated by one device. The controller can control the wms sensors either simultaneously (synchronous mode) or successively (scan mode or multiplexmode). The choice of operating mode (selected by way of a slider switch on the front, see Fig. 2) depends on the application. Very precise distances or thicknesses can be measured by combining the controller with the appropriate wms sensors (e.g. wms-25/rt/hv M18, see Fig. 5). The controller offers users the option of using one sensor channel for temperature compensation. The sensor connected to this channel measures the distance to a fixed target. The measured values of the other sensors are then compensated by the value of the»reference sensor«(see Fig. 6). Further, the average current value of the other, active channels is output at the reference channel output. The analogue windows set for all active sensors can be moved simultaneously and identically via the»shift«input. This option requires the addition of an external circuit consisting of one special switch (see»optional»shift«mode«) and two resistors.
6 Important advice concerning installation and use 2 Important advice concerning installation and use The wms-4/4i II is one component within a control system! During installation, setting-up or maintenance work, all measures must be taken to ensure safety of personnel and plant (refer to operating instructions for complete plant and instructions of plant operator). Fig. 5: Possible application: conveyor belt with measurement of width and height 6 Fig. 6: Possible application: film extruder with reference channel Hazards can arise from substances and materials being processed in the plant! Take all necessary precautionary measures and wear suitable protective clothing (adhere to directives of employers liability insurance association as well as instructions of plant operator or plant operating instructions).
7 Important advice concerning installation and use The controller is not intended for use with systems serving the safety of persons or security of machines! The operating instructions make use of the following keywords: Danger health hazard or risk of injury Caution important information regarding the safe operation of equipment Warning risk of severe damage to equipment, machinery or the environment Note advice concerning rational operation or special aspects which have to be taken into account Before you attempt to intervene in the operation of the controller, carry out a risk analysis with regard to the repercussions of: failure of controller failure of sensors failure of temperature compensation set-up incorrect control commands (e.g. when programming the controller) In doing so, take into account not only the immediate risks for personnel and plant but also the effects on the local environment! Danger! Ignoring the following instructions can result in a risk of injury to yourself or others or damage to property. Only operate the plant when you have sound knowledge of its operation and control. If necessary, ask the operator s specially trained personnel to assist you. Switch the plant to a safe condition (e.g. switched off, creep mode). For details, refer to the operating instructions for the complete plant. Take all precautions to ensure that this safe condition cannot be changed while work on the system is being carried out (e.g. actuate key-operated switch). 7
8 Installation Take all prescribed industrial safety measures (adhere to directives of employers liability insurance association as well as instructions of plant operator or plant operating instructions). 3 Installation The controller is intended to be mounted in a protective housing (e.g. distribution cupboard, electrical cabinet), and attached to a top-hat rail conforming to DIN EN Warning! All installation work must be carried out by a qualified, competent electrician. Caution! The voltage supply for the sensors is provided by the wms-4/4i II controller. Never connect the sensors to any other external voltage supply. The connections for sensor voltage supply are protected against reversed polarity but not against short-circuits! A short-circuit can lead to considerable damage to the electronics. Ensure that the controller is installed in a wellventilated position to keep it cool during operation (see»technical Specification«). The operating environment for the controller must be dry and dust-free (class of protection IP 20). The sensor cables must not be more than 25 m long. All cables longer than 5 m should be shielded. 8
9 Installation Place the controller on the top-hat rail at the desired position and clip it onto the rail using light pressure. If required, install sensor and target for reference measurement (e.g. for temperature compensation). Attach the sensors to the screw terminals for inputs (see Fig. 2). The wms-4/4i II can be operated with 1, 2, 3 or 4 sensors. 9 The following types of sensors can be operated simultaneously with the controller: wms-25/rt/hv/m18 wms-30/rt/hv/m30 wms-101/rt/hv/m30 wms-301/rt/hv/m30 wms-601/rt/hv/m30 Fig. 7 Sensor selection table If you are using microsonic connecting cables, note the colour coding of the wires. Terminal Colour Pin-No. on unit S e n d e r / S e n s o r white 2 U0/Sensor brown 1 Echo/Sensor black 4 GND/Sensor blue 3 Fig. 8: Colour coding and view of pins on wms-type sensor
10 Setting-up If required, connect a»shift«switch to the»shift«screw terminal via the two external resistors according to the following diagram: Fig. 9: Connection diagram for»shift«switch Danger! The controller starts operating immediately once the voltage supply is switched on. This could result in undesirable control commands leading to hazards for persons and plan. Switch off the plant or only connect the cables to terminals»output 1...4«after the controller has been properly programmed (see»setting-up«). Lay the cables for controlling the plant as far as the controller. Connect the controller to the low-voltage supply ( V d.c.) via screw terminals +UB and -UB. 4 Setting-up All setting-up operations (e.g. initial set-up or after modifications/repairs) must be carried out by suitably trained, competent persons! The settings of the controller must be checked or the controller fully programmed during every setting-up procedure. The wms-4/4i II is preprogrammed as follows before being dispatched: all sensor channels ON sensor type wms-101/rt/hv/m30 sensor local window limit 190 mm sensor remote window limit 340 mm rising output characteristic synchronous mode 10
11 Setting-up Danger! The controller starts operating immediately once the voltage supply is switched on. This could result in undesirable control commands leading to hazards for persons and plant. To carry out accurate programming of the device or to check the settings you will need a measuring instrument (e.g. ammeter) for the output currents of the controller s sensor channels. Observe the foregoing warnings and safety instructions when attaching the measuring instrument! Note The connections for the voltage supply to the controller incorporate reverse polarity protection. If the controller or the sensors supplied via the controller do not function correctly, check the polarity of the connections for the controller s voltage supply and the connections of the sensors at the controller. Switch on the voltage supply to the controller. The controller and its associated sensors are opera - ting correctly when the green LEDs (Fig. 2, Pos. 7) of the active sensors light up in a cycle and hence indicate normal measuring mode (see»normal mode«). 11
12 Normal mode Check the settings or reprogramme the controller. To do this, refer to»programming«. 5 Operation The wms-4/4i II controller can operate in the following modes: normal mode indicator mode»shift«mode 5.1 Normal mode Indication of measuring activity All active sensor channels indicate measuring activity by way of a flashing green LED (Fig. 2, Pos. 7). Function of channel LEDs If there is an object within the detect range of a sensor, then the sensor s associated yellow LED (Fig. 2, Pos. 8) lights up. 12
13 Indicator mode Selecting the operating mode The controller may be switched between two operating modes at any time. To do this, switch the»scan/sync«slider switch (Fig. 2, Pos. 6) accordingly.»sync«: switches the unit into the synchronous mode. All sensors are controlled and evaluated simultaneously.»scan«: all sensors are controlled and evaluated in succession. This mode allows, for example, opposing sensors to be operated. Please note that the measurement repeat rate of each individual sensor is lower than for sync mode. 5.2 Indicator mode The unit s settings can be indicated at any time in normal mode. The normal operation of the controller does not have to be interrupted. Briefly press the»up«or»down«button (Fig. 2, Pos. 1 or 2). This selects the indicator mode. The following information is provided for one channel (see Fig. 10): number of channel indicated channel characteristic type of sensor Sensor channel (yellow LEDs, Fig. 2, Pos. 8) Type of sensor (green LEDs, Fig. 2, Pos. 7) wms-25/rt/hv/m18 wms-30/rt/hv/m30 wms-101/rt/hv/m30 wms-301/rt/hv/m30 wms-601/rt/hv/m30 Characteristic of sensor channel (green LEDs, Fig. 2, Pos. 5) rising ma falling ma reference channel 13 Fig. 10 LEDs on controller
14 Optional»SHIFT«mode Briefly press the»down«button to switch to the next sensor channel or the»up«button to switch to the previous one. Briefly pressing both buttons simultaneously switches the controller back to normal mode. The unit automatically returns to the normal mode 20 s after the last button is pressed. 5.3 Optional»SHIFT«mode This operating mode allows the window limits for the output of analogue values to be modified. Consequently,»SHIFT«mode is suitable for the fine calibration of sensors and control, e.g. during a plant test run. This operating mode is an optional feature. To enable this function, a special switch must be installed (see»installation«). This switch has three positions:»upoffdown«all window limits for the output of analogue values are moved in the same direction (»UP«or»DOWN«). You can make small changes by briefly moving the switch to»up«or»down«or larger changes by holding the switch in one of these positions. The preset window size remains constant. The windows can be moved until they reach the preset limits of the sensors. The speed at which the windows are moved depends on which mode»scan«or»sync«has been set (»SCAN«= slower shift than»sync«). 14
15 Optional»SHIFT«mode Danger! The operation of the controller is not interrupted during»shift«mode! All changes take effect immediately. This could result in undesirable control commands leading to hazards for persons and plant. Move the»shift«switch into the»up«or»down«position (briefly and then releasing it or by holding it in position). The preprogrammed windows for the output of analogue values are changed for all active sensors.»up«= moving away from sensor»down«= moving towards sensor The direction of the movement is indicated by the flashing green LEDs»NEAR«(= down) or»far«(= up) on the front of the controller. At the same time, the channel indicator LED flashes for the channel which is being adjusted. Release the»shift«switch. The new values for the window limits local to and remote from the sensor are stored in the EEPROM. The controller returns to the normal mode. 15
16 Programming 6 Programming The programming feature enables settings to be made so that the controller s program can be adjusted to the actual measuring and control requirements of the application. The following settings are possible: (complete) programming changes to programmed settings copying of settings activation/deactivation of channels Programming (e.g. initial set-up or after modifications/repairs) must be carried out by suitably trained, competent persons! Danger! The operation of the controller is not interrupted during programming! All changes take effect immediately. This could result in undesirable control commands leading to hazards for persons and plant. Warning! If the plant cannot be shut down completely, then the connection between plant control and wms controller may only be interrupted when no undesirable control commands would result from such an interruption. Take all necessary measures to ensure safety of persons and plant (see»important advice concerning installation and use«). The exact settings of the analogue windows (position and size) can be made and checked with an ammeter. Observe the foregoing warning and safety instructions when attaching the measuring instrument! 16
17 Programming The following points apply to the procedure: Individual programming steps may be skipped. Briefly press the»enter«button. This switches to the next step and existing settings are not altere d. An incorrect entry can be corrected by waiting 20 s. Provided no button is pressed during the 20 s, no changes are stored and the unit automatically returns to normal mode. Settings and changes are only accepted when the programming procedure has been completed or the copying of settings has been completed. Note the various functions of the»enter«button: In normal mode, press»enter«for approx. 3 s in order to initiate the channel selection (one yellow channel LED flashes). Briefly press»enter«in order to confirm a selection/setting and to switch to the next programming step. Press»ENTER«for approx. 5 s in order to copy settings to the other active channels (see»copying settings«). Note If you wish to use one sensor channel for temperature compensation, you must first set up this channel as a reference channel before programming the other sensor channels. 17
18 Setting up the reference channel (option) 6.1 Setting up the reference channel (option) Initiating the programming Press the»enter«button until one of the yellow channel LEDs (Fig. 2, Pos. 8) flashes (after approx. 3 s). Briefly press the»enter«button. Entering the type of sensor Select the type of sensor connected to the reference channel by pressing the»up«or»down«button. Selecting the channel characteristic»ref«select the channel characteristic»ref«by pressing the»up«or»down«button. Both channel characteristic LEDs (Fig. 2, Pos. 5) must flash. =»REF«Release the»enter«button. Selecting the reference channel Select the reference channel using the»up«or»down«button. The yellow channel LEDs (Fig. 2, Pos. 8) indicate the channel selected. 18 The green LEDs (Fig. 2, Pos. 7) indicate the type of sensor. (If all LEDs flash, then this shows that the sensor channel has been deactivated.) Briefly press the»enter«button. Setting up the reference channel Briefly press the»enter«button. The wms-4/4i II now stores the current distance to the reference target. The arithmetic mean current value of all the other active channels is output at the analogue output of the reference channel. (In the case of thickness gauging with two sensors plus one reference sensor, the value of the current at the
19 Programming a channel of the controller reference channel now corresponds directly to the measured thickness.) The settings for the reference channel are copied into the EEPROM of the controller and stored permanently. The controller immediately returns to normal mode. You should now set the other sensor channels. 19 Note If there is no valid echo time present in the analogue window set for the reference channel, the programming procedure stops at this point until a valid measurement is available; until no button is pressed within 20 s. If another channel was previously the reference channel, then this now becomes a»normal» channel. Its settings type of sensor, channel output characteristic, position and size of analogue window remain unchanged. 6.2 Programming a channel of the controller The programming is carried out separately for each channel of the controller. The window sizes can be set manually or copied at the press of a button (»teach-in«). Note The minimum width of window is 50 mm. If this width is reached, then the other window limit is moved 50 mm ahead of the limit to be adjusted until the maximum range or the blind zone of the sensor is encountered (see Fig. 4). If there is no target within the beam spread during teach-in, then the local sensor limit is set 50 mm short of the maximum range or the remote sensor limit is set to the maximum range.
20 Programming a channel of the controller Abb. 11: Variable window limits Initiating the programming Press the»enter«button until one of the yellow channel LEDs (Fig. 2, Pos. 8) flashes (after approx. 3 s). Release the»enter«button. Largest window Smallest window limit remote from sensor 20 limit close to sensor wms-25/rt/hv/m18 35 mm 350 mm wms-30/rt/hv/m30 65 mm 600 mm wms-101/rt/hv/m mm mm wms-301/rt/hv/m mm mm wms-601/rt/hv/m mm mm Selecting a channel Select the channel to be programmed by pressing the»up«or»down«button. The yellow channel LEDs (Fig. 2, Pos. 8) indicate the channel selected. Briefly press the»enter«button. Entering the type of sensor Select the type of sensor connected to the channel input by pressing the»up«or»down«button. The green LEDs (Fig. 2, Pos. 7) indicate the type of sensor selected. (If all LEDs flash, then this shows that the sensor channel has been deactivated.) Briefly press the»enter«button. Selecting the channel characteristic Select the channel characteristic by pressing the»up or»down«button. The green channel characteristic LEDs (Fig. 2, Pos. 5) indicate the chosen characteristic:»rising«( ma) or»falling«( ma) Briefly press the»enter«button. Setting the local window limit The green LED»NEAR«flashes (Fig. 2, Pos. 4).
21 Programming a channel of the controller Move the object to be scanned or a temporary target to the position at which the local limit of the analogue window is to be set. Press the»up«and»down«buttons simultaneously. The controller accepts the current distance to the target as the local window limit (»teach-in«). Or adjust it manually: Press the»up«or»down«button. The local limit is moved away from the sensor with the»up«button, towards it with the»down«button. Check the setting with an ammeter if necessary. Note You can adjust the limit step by step (press briefly) or continuously (hold down). Briefly press the»enter«button. Setting the remote window limit The green LED»FAR» flashes (Fig. 2, Pos. 4). Move the object to be scanned or a temporary target to the position at which the remote limit of the analogue window is to be set. Press the»up«and»down«buttons simultaneously. The controller accepts the current distance to the target as the remote window limit (»teach-in«). Or adjust it manually: Press the»up«or»down«button. The remote limit is moved away from the sensor with the»up«button, towards it with the»down«button. Check the setting with an ammeter if necessary. Note You can adjust the limit step by step (press briefly) or continuously (hold down). 21
22 Copying settings Briefly press the»enter«button. Only now are all the settings copied into the EEPROM of the controller and stored permanently. The controller returns to normal mode. If necessary, set further sensor channels. To do this, return to»initiating the programming«. 6.3 Copying settings This program function of the controller eases the task of programming several channels of the controller. All the settings are copied to the other channels of the controller. A number of points must be taken into account: The copying of settings is only possible when the active sensors are all of the same type. No settings can be copied from a (temperature) reference sensor to other sensors. Only the setting»output characteristic rising/falling«can be copied to a re f e rence sensor. Warning! The changed settings are copied into the EEPROM without any further acknowledgement! Press the»enter«button until one of the yellow channel LEDs (Fig. 2, Pos. 8) flashes (after approx. 3 s). Release the»enter«button. Briefly press the»up«or»down«button until the channel is shown from which you wish to copy settings. 22
23 Activating/Deactivating a channel Press the»enter«button for approx. 5 s. The controller copies all settings from this sensor channel to all other active sensor channels and then returns immediately to normal mode. Release the»enter«button. 6.4 Activating/Deactivating a channel The activation and deactivation of channels are among the programming functions of the contro l l e r. Press the»enter«button until one of the yellow channel LEDs (Fig. 2, Pos. 8) flashes (after approx. 3 s). Release the»enter«button. Briefly press the»up«or»down«button until the channel you wish to activate or deactivate is shown. The green LEDs (Fig. 2, Pos. 7) indicate the type of sensor. Briefly press the»up«or»down«button until the type of sensor connected is shown (activation) or all sensor type LEDs flash (deactivation). Briefly press the»enter«button four times. The change is copied to the EEPROM. The controller automatically returns to normal mode. Briefly press the»enter«button. 23
24 7 Technische Daten wms-4/4i II Technical Specification Operating voltage U B 20 bis 30 V d.c., reverse polarity protection, 10% voltage ribble No-load current consumption 50 ma (without sensors) Type of connection 23 srew terminals (wire cross-section max. 1,5 mm 2 ) Outputs Controls Indicators Sensors wich may be connected Sensor connections Method of measurement Resolution Reproducibility 4 x current outputs ma 3 button & 1 slider 4 yellow LED s (sensor chanel) 8 green LED s (programming) wms-25/rt/hv/m18, wms-30/rt/hv/m30 wms-101/rt/hv/m30, wms-301/rt/hv/m30 wms-601/rt/hv/m30 up to 4 sensors with 4 wires (U 0, GND, 2 x signal lines) Echo propagation time 0,36 mm ± 1 mm in scan mode, ± 3 mm in synchronous mode Temperature drift 0,17 %/ C without temperature compensation Temparature compensation by way of ultrasonic reference measurement Measurement recording S y n c h ronous of scan (multiplex) oparation selected via slider swith Responce time 85 to 220 ms, depends on sensortype Housing Plastic housing, suitable for top-hat rail mounting (DIN EN ) Operating temperature 20 C C, non-condensing Storage temperature 40 C C Class of protection IP 20 Weight 210g EMC-resistance IEC Electrostatic dischage 4 kv/8 kv IEC HF interference 10V/m IEC Fast transient 2 kv IEC HF interference 10 V (3 V) EN irradiated interference 24
25 The address microsonic GmbH Hauert 16 D Dortmund Telefon: +49 (0) 231/ Telefax: +49 (0) 231/ Internet: Subject to change without notice Errors and omissions excepted MV-DO-817 Rev.0
Original instructions INCA-1 Tina Emergency stop for enclosure installation INCA-1S Tina Safety stop for enclosure installation ABB AB / Jokab Safety Varlabergsvägen 11, SE-434 39 Kungsbacka, Sweden www.abb.com/lowvoltage
en 03-2014/06 50126540 We reserve the right to make technical changes DB 112 B Double Sheet Testing Unit TECHNICAL DESCRIPTION 2014 Leuze electronic GmbH + Co. KG In der Braike 1 D-73277 Owen / Germany
Model Number Features Very small housing High climatic resistance 12 Bit singleturn Analog output Surge and reverse polarity protection Description This absolute rotary encoder with internal magnetic sampling
DB 12 B Double Sheet Testing Unit GB 03-08/08 50104956 Table of contents 1 General information... 2 1.1 Explanation of symbols... 2 1.2 Declaration of conformity... 2 2 Safety notices... 3 2.1 Safety standards...
Uninterruptible power supply Data sheet 105623_en_00 PHOENIX CTACT 2013-06-07 1 Description Uninterruptible power supply units continue to deliver power even in the event of mains breakdowns or failures.
Industrial motor controller for brushed DC motors 24 VDC Design for output currents up to 5 A Control with the following functions: - reversal of direction of rotation - open-loop speed control (external)
ODSLR 96B Optical laser distance sensors Dimensioned drawing en 05-2012/11 50110336 60 2000mm 18-30 V DC We reserve the right to make changes DS_ODSLR96BMCV62000_en_50110336.fm Reflection-independent distance
Bedienungsanleitung Instruction Manual testo 815 Sound Level Meter de en 18 General Information General Information Please read this documentation through carefully and familiarise yourself with the operation
3B SCIENTIFIC PHYSICS Digital Multimeter E 1018832 Instruction sheet 12/16 SD/UD 1 probe 1a Finger guards 2 Measurement socket 10 A for current measurement in 10-A (positive) 3 Measurement socket COM (negative)
Power supply unit INTERFACE Data sheet 102894_en_03 1 Description PHOENIX CONTACT 2015-11-17 Features MINI POWER power supplies for MCR technology In measurement and control technology (MCR), modular electronics
Compact, self-contained luminescence sensor LISTED US Compact, self-contained design Features Senses luminescent marks, even on luminescent backgrounds and on reflective surfaces, such as ceramic, metal,
Agilent G1888 Network Headspace Sampler Safety and Regulatory Information Agilent Technologies Notices Agilent Technologies, Inc. 2004 No part of this manual may be reproduced in any form or by any means
WLL 0 Photoelectric switches with fibre-optic cable, red light, manual sensitivity adjustment -- DC 0... 0 mm Through-beam systems Dimensional drawing R. -R. Scanning distance 0... 0 mm. Proximity systems
Industrial motor controller for brushed DC motors 12 VDC Design for output currents up to 5 A Control with the following functions: - reversal of direction of rotation - rotational speed control (external)
Smart Power Relay E-48-8I... Description The Smart Power Relay E-48-8I.- is a remotely controllable electronic load disconnecting relay with three functions in a single unit: l electronic relay l electronic
QUINT-PS-24/24/10 QUINT - converter, primary switched mode, input: 24 V, output: 24 V /10 A INTERFACE Data Sheet PHOENIX CONTACT - 02/2006 Description The QUINT - converter 24 V/10 A converts the voltage
M I C R O O H M M E T E R Reference Manual IBEKO POWER AB Sweden 2 IBEKO POWER AB Manual Version:. MV.01 IBEKO POWER AB 2003 This Reference Manual is a publication of IBEKO POWER AB, 18 125 Lidingö, Sweden.
INSTRUCTION MANUAL DM-45 Digital Multimeter Read and understand all of the instructions and safety information in this manual before operating or servicing this tool. Description The Greenlee DM-45 Digital
Instruction Manual EVolution Dear customer, We are delighted that you have decided to purchase the PowerBox Evolution from our range. We wish you every success with your new PowerBox Evolution, and hope
2CDC 271 015 F0t06 a OUTPUT L+, L : terminals output b DC OK: terminal signalling output c INPUT L, N, PE: terminals input d OUTPUT OK: green LED output voltage OK e OUTPUT Adjust: potentiometer adjustment
Operating instructions Flat-Type Wall-Mounted Radio Control Insert 1. Function The wall-mounted radio control insert permits remote control of all receivers of the Funk-Management system. This wall-mounted
L L N N on error RUN 1 2 3 4 KNX EIB 1 1 1 1 Chapter 9: Dimming actuators/control units Chapter 9:Dimming actuators/control unitsart. no.6493xxas of 10/079.2Universal dimming actuators Universal dimming
2CDC 271 028 F0008 OUTPUT L+, L+, L-, L-: terminals - output Features Rated output voltage 48 V DC Output voltage adjustable via front-face rotary potentiometer OUTPUT Adjust Rated output current 5 A Rated
CEC 1-808 VIBRATION TRANSMITTER Operation & Maintenance Manual 746 Arrow Grand Circle Covina, CA 91722 United States of America Tel: (626) 938-0200 Fax: (626) 938-0202 Internet: http://www.cecvp.com E-mail:
M e s s t e c h n i k INSTRUCTION MANUAL PC - Station for wireless Data transmission Document No. : D1F604 001 Version : April 2006 Copyright : IBR Messtechnik GmbH & Co. KG Contents 1. Introduction 1.1
Data sheet DS/LST100-EN LST100 Ultrasonic level transmitter for upstream oil and gas Accurately track and measure the most expensive consumable on your site chemicals. Measurement made easy Features Keep
2CDC 271 024 F0008 OUTPUT L+, L+, L-, L-: terminals - output INPUT L, N, PE: terminals - input OUTPUT OK: green LED - output voltage OK OUTPUT LOW: red LED - output voltage too low OUTPUT Adjust: potentiometer
MANUAL Electrostatic Field Meter EFM 235 / 255 System Prof. Dr.-Ing. Hans Kleinwächter 2 Manual EFM 120 Contents General information about electrostatics... 3 Origin of electrostatic charge... 3 Product
LASER Analog Laser Displacement Transducer LAS Series Key-Features: Content: Measurement Principle & Installation...2 Overview of the Series...3 Technical Data.4 Technical Drawing...7 Linearity & Resolution...8
PWM regulator for electrolysis cell Η 2 Ο Red or Gray Battery positive end (+) via fuse 25Α (30Α max) Blue Positive PWM output towards solution 1 Brown Negative PWM output towards solution Solution state
SYSTXBBSAM01 EVOLUTION SYSTEM ACCESS MODULE Installation Instructions NOTE: Read the entire instruction manual before starting the installation. pointsett U.S. Pat No. 7,415,102 Fig. 1 - Evolution System
MCR-T-UI(/) MCR-T-UI-E(/) Programmable Temperature Transducers for Resistance Thermometers and Thermocouples INTERFACE ata Sheet 00_0_en PHOENIX CONTACT - 0/00 escription A universal temperature measuring
ADC5000 SERIES AC/DC Switch Mode Power Supplies and Rectifiers for Industrial and Telecom Applications 60W, 125W and 250 W Input voltage 230/115 VAC voltages 12, 24, 36 or 48 VDC Statistical MTBF >3 000
Order no.: 0868 00 System rmation This device is a product of the Instabus EIB system and complies with EIBA directives. Detailed technical knowledge obtained in Instabus training courses is a prerequisite
Electronic amplifier type EV1D Product documentation Modular construction Supply voltage UB: Output current IA: 10...48 V DC max. 2 A D 7831 D 09-2015-1.1 by HAWE Hydraulik SE. The forwarding and reproduction
Power Distribution System SVS8 Description The power distribution system SVS8 optimises the DC V distribution in automation and process control, in the production area of the chemical industry and in power
Medium Converter FL MC 0BASE-T/FO G0. Description The FL MC 0BASE-T/FO G0 medium converter provides a high level of noise immunity and a long transmission range in industrial applications by converting
Installation & User Manual Radio Remote RCS 20E SLEIPNER MOTOR AS P.O. Box 519 N-1612 Fredrikstad Norway Tel: +47 69 30 00 60 Fax: +47 69 30 00 70 www.side-power.com email@example.com Made in Norway
English Operating manual Temperature measuring transducer MU125 Company / brands of GHM www.ghm-messtechnik.de Save for later reference. Table of contents Page 1. Intended use (areas of application)...
IDEAL INDUSTRIES, INC. TECHNICAL MANUAL MODEL: 61-920 The Service Information provides the following information: Precautions and safety information Specifications Performance test procedure Calibration
Dimensioned drawing en 02-2012/11 50112361 150 800mm 10-30 V DC We reserve the right to make changes DS_ODSL96BS800_en_50112361.fm Small laser light spot for measurements on small, structured or metallic
PD 5 English Français Español en fr es 1 2 3 4 PD 5 en Original operating instructions.......................... 1 fr Mode d'emploi original............................... 12 es Manual de instrucciones
473 PHOTO PHOTO Ultra-slim Sensor NA-PK5 SERIES SERIES General terms and conditions... F-7 Sensor selection guide... P.4~ Related Information Glossary of terms... P.455~ General precautions... P.458~ Conforming
France: Commercial info Technical info incl.taxes/m in incl.taxes/m in incl.taxes/m in from a land line from a land line from a land line DELTA DORE TALCO - Bonnemain - 35270 COMBOURG E-mail: firstname.lastname@example.org
Fans Air Handling Units Air Distribution Products Fire Safety Air Curtains and heating Products Tunnel Fans System protection by Vibration monitoring for fans 2 Ventilatoren Vibration monitoring for fans
Primary-switched power supply with SFB technology, 1 AC, output current 20 A INTERFACE Data Sheet 103383_en_00 1 Description PHOENIX CONTACT - 06/2008 Features QUINT POWER power supply units highest system
INSTALLATION MANUAL Model: Smart Analyzer Manufacturer: Smart Impulse Power meter with consumption breakdown by use 03/12/13 Table of contents Table of contents... 2 1. Introduction... 3 2. Installation
Réf. 335-4.33 / a -.98.5 X-.39 Synchro output speed reference Menu 3 Max. sp Min. spe Negativ speed s.4 Synchro out speed refere selection Menu 3 Skip frequency Skip width.29.3.3 g t Run Run FWD REV 27
Radio System Strobe Wizard Plus Freemask User manual Translation of the original German user manual Doc. No.: 900.0509.00 Version: 09/2017 Contents Information about this manual and about the manufacturer...
High-resolution absolute encoder based on magnetic technology. Singleturn sensing based on 360 Hall effect technology. Multiturn sensing based on magnetic pulse counter. No batteries used. Main Features
Overview and Identification The 900 MHz unit receives a repeated or re-transmitted RF signal from one or more wireless temperature or humidity transmitters. The signal from the transmitter (418 MHz) is
487 Ultra-slim Sensor NA-PK5 SERIES SERIES General terms and conditions... F-7 Sensor selection guide... P.475~ Related Information Glossary of terms... P.359~ General precautions... P.45 PHOTO PHOTO Conforming
NOVOHALL Rotary Sensor touchless technology transmissive Series RFC4800 analog The RFC 4800 utilizes a separate magnet or magnetic position marker, attached to the rotating shaft to be measured. The orientation
Diagnostics Unit for Electric Charging Stations (Type 2 Connector Socket and Plug) 3-349-878-03 1/3.16 Opening the Instrument / Repairs The instrument may only be opened by authorized, trained personnel
PHV 1000-3-RO High Voltage Passive Probe Instruction Manual Copyright 2012 PMK GmbH All rights reserved. Information in this publication supersedes that in all previously published material. Specifications
Jarvis standing desk Assembly instructions For assembly assistance, visit fully.com/howtojarvis or call 888-508-3725 or email email@example.com Thank you for choosing a Jarvis desk from Fully. Cautions
Isolators, Isolator / Power Supplies Operating Instructions EN Contents 1. About this document...4 1.1. Function... 4 1.2. Target group... 4 1.3. Symbolism used... 4 2. For your safety...5 2.1. Authorized
Universal current transducer Data sheet 104059_en_05 PHOENIX CONTACT 2011-03-09 1 Description MCR-SL-CUC-...-I and MCR-SL-CUC-...-U active current transducers convert DC, AC, and distorted currents into
SIMATIC ET 200SP Digital input module DI 8xNAMUR (6ES7131-6TF00-0CA0) Manual Edition 02/2014 Answers for industry. DI 8xNAMUR HF digital input module (6ES7131-6TF00-0CA0) SIMATIC ET 200SP DI 8xNAMUR HF
MV110-8A Analog input module 8 channel User guide MV110-8A_2016.12_0225_EN All rights reserved Subject to technical changes and misprints Contents 1 Description... 2 1.1 Function... 2 1.2 RS485 network...
Product data sheet 94.077 EY-EM 522, 523: Remote I/O module, ecolink522, 523 How energy efficiency is improved Regulation, control, monitoring and optimisation of operational systems, e.g. room automation
AC 3 Active Antenna Combiner Instruction manual Contents Contents Important safety instructions... 2 The AC 3 active transmitter combiner... 4 Delivery includes... 4 Operating controls... 5 Block diagram...
Your Global Flow Control Partner Series 70 SERVO PRO Version 3.0 Table of Contents 1.0 Safety Instructions - Definition of Terms...........................2 1.1 Hazard-free Use.......................................2
694 Relativ- und Differenz-Drucktransmitter Relative and differential pressure transmitter Transmetteur de pression relative et différentielle 0.5 +0.5 mbar / 0 1 50 mbar Huba Control FEINE MESSIDEEN FÜR
Primary-switched power supply unit with SFB technology, 3 AC, output current 40 A INTERFACE Data sheet 103133_en_00 1 Description PHOENIX CONTACT - 07/2009 Features QUINT POWER power supply units Maximum