1 T-68 Protecting Your Equipment through Power Quality Solutions Dr. Bill Brumsickle Vice President, Engineering Nov. 7-8, 2012 Copyright 2012 Rockwell Automation, Inc. All rights reserved.
2 2 Agenda What is Power Quality? Importance of Power Quality to Industrial Users Power Quality Events & Voltage Sags Voltage Sag Protection
3 3 Power Quality vs. Power Reliability Power Reliability: Continuity of electric power delivery measured by the number and duration of power outages (Zero voltage) Outages are tracked by Utilities Power Reliability can be as high as % availability Power Quality: Related to fluctuations in electricity, such as momentary interruptions, voltage sags or swells, flickering lights, transients, harmonic distortion and electrical noise Fewer such incidents indicate greater power quality Events go mostly untracked by Utilities Sag & Momentary events can take out a process as many as times per year The Grid is designed for Reliability, not Quality
4 Power Quality Frequency is regional Determined by HV & EHV network generators Problems are rare Voltage is area-wide Determined by MV distribution network Problems occur randomly, but with regularity Current is local Determined by facility loads Problem loads can be identified and resolved Source: DTE Energy website 4 Copyright 2012 Rockwell Automation, Inc. All rights reserved.
5 Utility Power Properties of AC Grid Not always ideal sinusoidal voltages! Highly interconnected Transformer and line impedances between generators and loads Terminal voltage drops with load current System faults cause significant voltage sags (dips) Most wiring is overhead Susceptible to lightning, animals, wind-blown tree branches, etc. Source: NPR: Power Hungry: Reinventing The U.S. Electric Grid May 1, 2009 Insulation fails, equipment fails 5 Copyright 2012 Rockwell Automation, Inc. All rights reserved.
6 6 Power Quality Problems All have physical causes
7 7 Agenda What is Power Quality? Importance of Power Quality to Industrial Users Power Quality Events & Voltage Sags Voltage Sag Protection
8 Electrical Equipment Designed Assuming Power Quality Operate with input ac voltage variation of 10% Possible new requirements: Operate through some voltage sags SEMI F47 IEC Present a unity Power Factor: Current phase angle near zero Current harmonic distortion low 8 Copyright 2012 Rockwell Automation, Inc. All rights reserved.
9 Impact of Power Quality Events Possible Agency, Utility, or Facility Requirements Power Factor correction (current phase angle) Harmonic current limits Load equipment mis-operation Voltage sags and momentary interruptions Voltage distortion (harmonics, notching) Voltage imbalance or single-phasing High-frequency voltage transients Load equipment damage High-voltage transients Current inrush following voltage sag Facility infrastructure damage High-voltage transients Current inrush following voltage sag Overheating due to current harmonics 9 Copyright 2012 Rockwell Automation, Inc. All rights reserved.
10 Consumer is Responsible for Power Quality Utility cannot provide perfect power quality and are not required to. (e.g., Wisconsin PSC ) Customers having equipment or operations that are sensitive to such voltage fluctuations may find it necessary to install, at their own expense, power conditioning equipment or other modifications Job is to Keep the lights on. Goals Deliver maximum energy through the existing infrastructure Maintain +/-10% (on average) voltage at service entrance Minimize outages longer than 2-5 minutes Hz, when averaged over 24 hours Keep large industrial customers satisfied Minimize large customers disrupting neighbors power quality The utility is responsible for reliability, not quality of power.the customer is responsible for protecting their sensitive equipment at their own expense 10 Copyright 2012 Rockwell Automation, Inc. All rights reserved.
11 11 Agenda What is Power Quality? Importance of Power Quality to Industrial Users Power Quality Events & Voltage Sags Voltage Sag Protection
12 Power Quality Issues Voltage sag (dip) and Momentary interruption High voltage transients (spikes) Current distortion (harmonics) Voltage distortion and voltage flicker caused by distorted current loads Voltage unbalance EPRI (Electrical Power Research Institute) Monitored 300 sites for 2+ years. 92% of all events were voltage sags under 2 seconds 4% of event interruptions from 2 seconds to 10 minutes Voltage notching Uncommon issues in the U.S. and high-tech. parks: brownout voltage swell frequency variation Poor grounding 12 Copyright 2012 Rockwell Automation, Inc. All rights reserved.
13 13 Voltage Sag (Dip) Characterization Sag - RMS voltage reduction between 1/2 cycle - 60 sec Magnitude and Duration 1 Duration: 4 Cycles Magnitude: 60% Remaining
14 Voltage Sag 90% Magnitude (per unit) Duration (ms) Copyright 2012 Rockwell Automation, Inc. All rights reserved. 14
15 Why mostly brief sags and interruptions? 12 kv 69 kv Radial Distribution F kVA Reclosing breakers 20 MVA " C" 480 VOLTS THREE PHASE FAULT F 2 " B" " A" V = V s Z line *I F 3 Fault results in short voltage sags and interruptions for most customers, affecting up to 200 mile radius VOLTAGE BEGIN FAULT F2 OPENS VOLTAGE AT "C" AND ON F1 & F3 VOLTAGE AT "B" TIME F2 CLOSES V=0.67 p.u. V=0.40 p.u. F2 OPENS FAULT CLEARS F2 CLOSES 15 Copyright 2012 Rockwell Automation, Inc. All rights reserved.
16 Why Sag Durations are short Clearing Time in Cycles Type of Fault Typical Minimum Typical Time Delay Number of Retries Clearing Device Expulsion Fuse to 60 None Current Limiting Fuse 0.25 or less 0.25 to 6 None Electronic Recloser 3 1 to 30 0 to 4 Oil Circuit Breaker 5 1 to 60 0 to 4 SF 6 or Vacuum Breaker to 60 0 to 4 Source: IEEE Std Copyright 2012 Rockwell Automation, Inc. All rights reserved.
17 Sags at High-Tech Mfg. Sites Very few outages, still many sags! 1000 sag events from 15 Semi plants Avg. 5.4 events below CBEMA per year with transmission-level service! SEMI F47 source: International SEMATECH & EPRI, 1999
18 Impact of Voltage Sags Sensitivity of various 3-ph. 4kW drives to single-phase sag (rated speed, torque) [Djokic] 18 Copyright 2012 Rockwell Automation, Inc. All rights reserved.
19 Impact of Voltage Sags AC Relay Voltage Sag Tolerance Curves % of Nominal Voltage Duration of Sag (milliseconds) Upper range Average Lower Range Source: IEEE Std Copyright 2012 Rockwell Automation, Inc. All rights reserved.
20 Data Corruption Source: Djokic
21 IEEE P1668 a new standard Recommended Practice for Voltage Sag and Interruption Ride-through Testing for End-use Electrical Equipment Less than 1,000 Volts A standard for the response of electrical equipment to voltage sags Expected to include: Guidance for evaluation of equipment sensitivity to voltage sags and interruptions Minimum performance criteria to specify during the purchasing process Levels of performance for acceptance of the product Voltage tolerance curves for three-phase equipment: more useful than CBEMA or ITIC
22 22 Effect of Voltage Sags on Equipment Most common effect is equipment drops offline PLC shutdown Open contact or relay (As little as 80% remaining voltage for 1 Cycle) A secondary effect is that when voltage returns, high current inrush can occur because the Softcharge circuit is bypassed RF Amplifiers, Gradient Amplifiers, and Low Voltage Power Supplies subjected to repeated hits Fail. Typical rectifier circuit diagram: Voltage SAGS can shut-down and/or damage equipment!
23 23 Voltage Sags Effect Equipment Example: Inrush current measured for 1kVA electronic load Normal Inrush Inrush after Sag Volts Volts Amps Peak inrush 10A Soft-charge circuit is active Amps Peak inrush 50A Soft-charge circuit bypassed Note the scale change necessary to get the sagged results on the same page!
24 Only some machines shut down. Why? Fabrication or Assembly Line Layout: 480-b Machine 1 Machine 2 Machine 3 Machine 4 Machine 5 Machine a Machine power distribution and power supplies vary: L1 L2 L3 :Y Tranf. Rect. L1 N L2 N Tranf. Tranf. Controls Power Rect. Rect. Controls Power Controls Power L1 L2 L2 L3 L3 L1 Tranf. Tranf. Tranf. Rect. Rect. Rect. Controls Power Controls Power Controls Power L3 N Tranf. Rect. Controls Power
25 Detection of Power Quality Events Monitoring is Key to Knowing the Local Power Quality I-Sense, I-Grid Voltage Monitoring I-Sense voltage monitor device I-Grid network of monitors and database servers information and notification service & text message notification in real time Web summary, available from anywhere PDF Reports
26 I-Grid I-Sense monitors record & report PQ event data via the Internet Use Web browser to: View event details Manage accounts and monitors Generate reports and export data I-Sense Owners Internet I-Grid Servers & Database Web Utility Engineer Facility Engineer Real-time notifications Report delivery Other users
27 27 Agenda What is Power Quality? Importance of Power Quality to Industrial Users Power Quality Events & Voltage Sags Voltage Sag Protection
31 31 DySC (Dynamic Sag Corrector) DySC (pronounced Disk ) is an adaptive power supply that optimizes the remaining power during a sag by using patented inverter technology to compensate for the sag thereby maintaining an uninterrupted flow of optimal power to the load thus maximizing uptime, minimizing inventory loss and reducing maintenance costs Up to 5 seconds of ride through U.S. and International voltages available Scalable solution MiniDySC (single-phase; kva) ProDySC (3-phase; kva) MegaDySC (3-phase; kva)
32 32 DySC - Normal Operation Utility DySC Auto By-Pass Static Switch DSP Controller Load Cross- Coupling Transformer Power Conversion Rectifier Inverter Core Component DSP Controller Static Switch (99% efficient) Cross-Coupling Transformer Power Conversion Core Automatic By-Pass Activity Constantly monitors incoming power, system integrity and load Closed. Sends power directly to the load Idle Idle Idle Normal Operation - The DySC monitors power quality continuously, while the power electronics are in standby 99.99% of the time
33 33 DySC - Voltage Event Utility DySC Auto By-Pass Static Switch DSP Controller Load Cross- Coupling Transformer Power Conversion Rectifier Inverter Core Component DSP Controller Static Switch (99% efficient) Cross-Coupling Transformer Power Conversion Core Automatic By-Pass Activity Detects the leading edge of a voltage sag, immediately routing power thru the C-C Transformer and Power Conversion Core Open Pulls additional power from the grid Rectifies and inverts to recreate a true sinusoidal Output Idle DySC is On in under 2 milliseconds and recreates a true sinusoidal output
34 34 DySC Operation Normal Operation (Monitoring) Static Switch ON, Highly efficient Power electronics OFF Capacitors charged & ready No thermal cycling, long life Low maintenance Voltage Sag Correction 1-2 millisec. detection Static switch OFF Power Electronics ON, to produce corrected sinusoidal load voltage Energy from capacitors needed only for sags below 50% V = 100% V = 60% 167% 67% 167% 100% (V = 40%) patented V = 100% 100% LOAD 100% Example: voltage sag to 60%, full load We keep load voltage at 100%, so load power remains 100% Input Current rises briefly to (100% / 60%) = 167% Load energy comes from ac input, not from capacitors! Static bypass 99.99% of the time Corrects voltage by maintaining power flow (P = V x I) Most of the time the DySC is in a monitoring mode
35 35 DySC Sag Correction 330 kva MegaDySC responding to 3-phase 50% voltage sag, duration 4.5 seconds input waveforms output waveforms
36 36 DySC Interruption Correction input rms voltage 330 kva MegaDySC-ER 3-phase interruption for 250 ms (15 cycles) 90% output rms voltage
37 For More Information or Questions Power Quality at Automation Fair 2012 Essential Components (Booth 127): Protection Solutions Energy Management (Booth 541): Power Quality Monitoring Backroom Session: Hands-on DySC and I-Sense / I-Grid More information available at Booths
38 Thank you for your attention. Questions? Follow ROKAutomation on Facebook & Twitter. Connect with us on LinkedIn. Copyright 2012 Rockwell Automation, Inc. All rights reserved.
Slide 1 Electric Power Quality: Voltage Sags Momentary Interruptions Ward Jewell Wichita State University email@example.com Slide 2 Power Quality Events Voltage sags Outages/interruptions Voltage
Managing Power Quality Issues Questline Academy November 4, 2015 Mike Carter Justin Kale 2 Economic Value Productivity Customer Confidence How often do you deal with power quality problems at your facility?
Reducing the Effects of Short Circuit Faults on Sensitive Loads in Distribution Systems Alexander Apostolov AREVA T&D Automation I. INTRODUCTION The electric utilities industry is going through significant
Power Quality Monitoring and Power Metering Tutorial Power generation and transmission today are accomplished using three phase alternatingcurrent. To understand electrical power quality monitoring and
Harmonic Mitigation for Variable Frequency Drives HWEA Conference February 15, 2011 Kelvin J. Hurdle Rockwell Bus. Dev. Mgr. 1 OVERVIEW Linear vs. Non- Linear Load Definitions AC Drive Input Current Harmonics
Power Quality Analysers Review of Power Quality Indicators and Introduction to Power Analysers ZEDFLO Australia 6-Mar-2011 www.zedflo.com.au Power Quality Indicators Review of main indicators of electrical
Notes 1: Introduction to Distribution Systems 1.0 Introduction Power systems are comprised of 3 basic electrical subsystems. Generation subsystem Transmission subsystem Distribution subsystem The subtransmission
Generation Interconnection Requirements at Voltages 34.5 kv and Below 2005 March GENERATION INTERCONNECTION REQUIREMENTS AT 34.5 KV AND BELOW PAGE 1 OF 36 TABLE OF CONTENTS 1. INTRODUCTION 5 1.1. Intent
OVERVIEW OF DVR FOR POWER QUALITY IMPROVEMENT Shyam V. Alaspure 1, Snehal G. Vinchurkar 2, Swapnil D. Raut 1 Electronics & Telecommunication 2 Electronics & Power 3 Computer 1 Lecturer, G.H. Raisoni Polytechnic
POWER CORPORATION Power Quality Specifications and Guidelines for Customers Phone: 403-514-3700 Fax: 403-514-3719 1 GENERAL OVERVIEW........................................ 1.1 WHAT DOES THIS SPECIFICATION
conditioning products Electronic voltage regulator -Sure 700 & 800 -Suppress T7 & 100 Harmonic correction unit Sag ride-through power conditioner The power to work Basics of power quality The partner you
thepower to protect i-gard LITERATURE Low and medium voltage distribution systems Arc Flash Hazards and High Resistance Grounding Grounding of Standby and Emergency Power Systems Neutral Grounding Resistors
MAIN TOPICS DISCUSSED Electric Rates Electrical system utilization ELECTRICAL SYSTEMS AND ELECTRIC ENERGY MANAGEMENT SECTION K Power quality Harmonics Power factor (Cos phi) improvement Section K - 2 ELECTRIC
OVERVIEW OF IEEE STD 1564-2014 GUIDE FOR VOLTAGE SAG INDICES ABSTRACT Daniel SABIN Electrotek Concepts USA firstname.lastname@example.org IEEE Std 1564-2014 Guide for Voltage Sag Indices is a new standard that identifies
Course Power Quality - 1 Ljubljana, Slovenia 2013/14 Prof. dr. Igor Papič email@example.com Introduction to Power Quality Content Session 1 Session 2 Session 3 Session 4 1st day 2nd day 3rd day 4th
Introduction Several sections of the National Electrical Code relate to proper overcurrent protection. Safe and reliable application of overcurrent protective devices based on these sections mandate that
1 McGill Power Sales & Engineering, INC. Power Factor Correction Terry McGill President McGill Power Sales & Engineering Inc. 2007 Eaton Corporation. All rights reserved. Agenda What is power factor? What
Southern Company Power Quality Policy Alabama Power Georgia Power Gulf Power Mississippi Power i Table of Contents: Southern Company Power Quality Policy SCOPE AND PURPOSE... 1 DEFINITIONS... 2 I. HARMONICS...
New Power Quality Solutions Especially Designed For Industrial Applications Amaya Barona Francisco Ferrandis Iberdrola Distribución Eléctrica - Spain firstname.lastname@example.org email@example.com Javier
Technical Paper Harmonic in Data Centers Written By: Ian Wallace Summary Power quality and power reliability are critical to data center operation. As strides have been made to improve energy efficiency
Power Quality Study of Electrical Installation in Academic Institute Case Study Mr. Mukteshwar N. Patil 1, Prof. Rajesh M. Holmukhe 1#, Mr. Sadashiv Munde 2 1 Department of Electrical Engineering, Bharati
3Ø Short-Circuit Calculations Why Short-Circuit Calculations Several sections of the National Electrical Code relate to proper overcurrent protection. Safe and reliable application of overcurrent protective
POWER QUALITY INITIATIVES IN SINGAPORE S T Chang, K Y Chua, C C Siew and T L Tan PowerGrid Ltd, Singapore SUMMARY PowerGrid Ltd, a subsidiary of Singapore Power Ltd, is responsible for the transmission
1 A Single-Phase Voltage Sag Generator for Testing Electrical Equipments Yan Ma, Student Member, IEEE, George G. Karady, Fellow, IEEE Abstract This paper describes a transformer-based voltage sag generator
Maintaining Voltage-Current Phase Relationships in Power Quality Monitoring Systems Brian Kingham, Utility Market Manager, Schneider Electric, PMC Division Abstract: Historical power quality measurement
POWER QUALITY Energy Efficiency Reference 200V VOLTAGE SAG Voltage 125V 105V 0V 20.0v/div vertical 2 sec/div horizontal LINE-NEUT VOLTAGE SAG Time 100A CURRENT SWELL AMPS Current 30.0A 0A 10.0A/div vertical
Three-Phase Transformer Test Systems PHENIX TECHNOLOGIES R Testing Applications Models Available Perform tests on utility distribution and power transformers in accordance with IEC 60076 and ANSI / IEEE
2/50 Voltage Wave Attenuation CBEMA Constant Voltage Power Supply Voltage surge with a virtual front time of 1.2 ms and a time to half-value of 50 ms delivered across an open circuit. 8/20 Current Wave
DP&L s Technical Requirements for Interconnection and Parallel Operation of Distributed Generation Technical Requirements for Interconnection and Parallel Operation of Distributed Generation Single Phase
APPLICATION NOTE STANDARD EN 50160 VOLTAGE CHARACTERISTICS OF ELECTRICITY SUPPLIED BY PUBLIC ELECTRICITY NETWORKS Antoni Klajn, Marta Bątkiewicz-Pantuła March 2013 ECI Available from www.leonardo-energy.org/node/145851
Harmonics and Their Impact on Power Quality Wayne Walcott Application Engineering Manager June, 2017 Presentation Overview A little about harmonics What are harmonics What are NOT harmonics What creates
1 Power System Protection Where Are We Today? Meliha B. Selak Power System Protection & Control IEEE PES Distinguished Lecturer Program Preceding IEEE PES Vice President for Chapters firstname.lastname@example.org PES
Panel: Microgrid Research and Field Testing IEEE PES General Meeting, 4-8 June 7, Tampa, FL Microgrid Protection H. Nikkhajoei, Member, IEEE, R. H. Lasseter, Fellow, Abstract In general, a microgrid can
Review Power Quality Issues Mahmoud S. Awad Faculty of engineering Technology, Al-Balqa Applied University Amman, Jordan Amman, PO box 15008, Marka Ashamalia Tel: 962-7738-7901 Email: email@example.com,
EH27401 Communication and Control in Electric Power Systems Lecture 2 Lars Nordström firstname.lastname@example.org 1 Course map 2 Outline 1. Power System Topologies Transmission Grids vs Distribution grids Radial grids
31 CHAPTER 3 ELECTRIC POWER QUALITY 3.1 INTRODUCTION The planning, design, and operation of industrial and commercial power systems require several studies to assist in the evaluation of the initial and
The Electrical Power Engineers Qual-Tech Engineers, Inc. 201 Johnson Road Building #1 Suite 203 Houston, PA 15342-1300 Phone 724-873-9275 Fax 724-873-8910 www.qualtecheng.com ARC FLASH PPE GUIDELINES FOR
Transformer Protection Principles 1. Introduction Transformers are a critical and expensive component of the power system. Due to the long lead time for repair of and replacement of transformers, a major
Overview of voltage sag mitigation techniques Ambra Sannino Department of Electrical Engineering University of Palermo, Italy Michelle Ghans Miller, Math H.J.Bollen Department of Electric Power Engineering
International Conference On Industrial Automation And Computing (ICIAC- -3 April 4)) RESEARCH ARTICLE OPEN ACCESS Generation of Mathematical Models for various PQ Signals using MATLAB Ms. Ankita Dandwate
CHROMA ATE INC. Programmable AC Source 61500/61600 Series Product Manager: Galen Chou Chroma AC Source Family Outline 1. What is programmable AC source? 2. What is user s need? 3. What do they test with
P2 Power Solutions Pvt. Ltd. An ISO 9001:2008 Company Quality Power within your Reach P2 Power Magnetics P2 Power Solutions Pvt. Ltd. P2 Power Solutions Pvt. Ltd. provides EMC and power quality solutions,
Power Quality Monitoring: Analyse and Improve your Energy Performance Presented by: David Bradley B.Eng (Hons), MBA, C.Eng, MIET Energy Management & Power Quality Key Drivers PART L The energy efficiency
Harmonic Filters and Reactors Harmonics are invisible but costly If one looks up the meaning of harmonics in any one of several technical dictionaries, it is normally defined as being A sinusoidal component
Real Time Power Factor Correction Units (Transient Free Switching) Designers and Manufacturers of Power Factor Correction Equipment and Harmonic Filters 1016 34 AV SE Calgary, AB T2G 1V4 Canada Tel: 403
UProtection Requirements Ufor a Large scale Wind Park Shyam Musunuri Siemens Energy Abstract: In the past wind power plants typically had a small power rating when compared to the strength of the connected
PART 1: GENERAL 1.01 Transformer A. This section includes liquid filled, pad mounted distribution transformers with primary voltage of 12kV or 4.16kV (The University will determine primary voltage), with
Power Quality Measurements the Importance of Traceable Calibration H.E. van den Brom and D. Hoogenboom VSL Dutch Metrology Institute, Delft, the Netherlands, email@example.com Summary: Standardization has
Harmonic Distortion and Variable Frequency Drives Definitions Variable Frequency Drives (VFDs); sometimes referred to as variable speed drives. Harmonic Distortion is a measure of the amount of deviation
Backup Power Automatic Transfer NIPSCO Energy Symposium symposium Backup Power Applications/Considerations Backup Power Types Automatic Transfer Switch Basics Presenters McGill Power - Jeremy Irmeger Eaton
The 19 th International Symposium on High Voltage Engineering, Pilsen, Czech Republic, August, 23 28, 2015 ALLOWABLE LIMITS TO SHORT TIME VOLTAGE DROPS IN HV WITHSTAND TESTS William Larzelere Evergreen
SYSTEMS AND COMPONENTS FOR TRANSFORMER TESTING 9.11/2 Transformer Testing n Type tests n Routine tests n Special tests n Applicable for tests on power and distribution transformers in factory and on-site
LIGHTNING OVERVOLTAGES AND THE QUALITY OF SUPPLY: A CASE STUDY OF A SUBSTATION Andreas SUMPER firstname.lastname@example.org Antoni SUDRIÀ email@example.com Samuel GALCERAN firstname.lastname@example.org Joan RULL email@example.com
POWERENG 2007, April 12-14, 2007, Setúbal, Portugal Anti-Islanding Protection of Distributed Generation Resources Using Negative Sequence Component of Voltage Amin Helmzadeh, Javad Sadeh and Omid Alizadeh
Advanced Fault Analysis System (or AFAS) for Distribution Power Systems Laurentiu Nastac 1, Paul Wang 1, Om Nayak 2, Raluca Lascu 3, Thomas Walker 4, Douglas Fitchett 4, and Soorya Kuloor 5 1 Concurrent
23 rd International Conference on Electricity Distribution Lyon, 5-8 June 25 Paper 48 ADVANCED VECT SHIFT ALGITHM F ISLANDING DETECTION Murali KANDAKATLA Hannu LAAKSONEN Sudheer BONELA ABB GISL India ABB
79/26 Series III Multimeter Instruction Sheet W Read First: Safety Information Never use the meter if the meter or test leads look damaged. Be sure the test leads and switch are in the correct position
International Journal of Engineering Research and Development e-issn: 2278-067X, p-issn: 2278-800X, Volume 8, Issue 6 (September 2013), PP.35-39 A Reduction of harmonics at the Interface of Distribution
Tab 2 Voltage Stresses Switching Transients Distribution System Engineering Course Unit 10 2017 Industry, Inc. All rights reserved. Transient Overvoltages Decay with time, usually within one or two cycles
Great Northern Transmission Line: Behind the (Electrical) Design November 8, 2017 Christian Winter, P.E. Minnesota Power Sivasis Panigrahi, P.E. POWER Engineers, Inc. What is the Great Northern Transmission
EPCOS Product Brief 2017 Power Quality Solutions of Active Harmonic Filters and Power Optimizers EPCOS has been offering a comprehensive range of key components for power factor correction (PFC) and power
Power Quality Monitoring and Analytics for Transmission and Distribution Systems Doug Dorr Electric Power Research Institute Manager Advanced Monitoring Applications Group PQSynergy 2012 Evolving Smarter
EMC Philosophy applied to Design the Grounding Systems for Gas Insulation Switchgear (GIS) Indoor Substation Marcos Telló Department of Electrical Engineering Pontifical Catholic University of Rio Grande
GRID CONNECTION CODE FOR RENEWABLE POWER PLANTS (RPPs) CONNECTED TO THE ELECTRICITY TRANSMISSION SYSTEM (TS) OR THE DISTRIBUTION SYSTEM (DS) IN SOUTH AFRICA Version 2.9 (July 2016) This document is approved
Global Journal of Researches in Engineering: F Electrical and Electronics Engineering Volume 15 Issue 7 Version 1.0 Type: Double Blind Peer Reviewed International Research Journal Publisher: Global Journals
Features Small size of 2 x 4 x 1.3 75W convection cooled/115 Watts with 200 LFM Universal Input 90-264Vac Meets EN55015 Conducted EMI Meets IEC61000-3-2 Class C for less than 1 Watt to full power Approved
AccuLoss MODELS ALMS 2100, ALMS 4100, ALMS 4200, ALMS 6200 & ALMS 4300 The measurement of electric power and energy at high voltages and currents at low power factors is becoming increasingly important
Emission Limits for Customer Facilities Connected to the Hydro-Québec Transmission System Études de réseaux Direction Planification des actifs Hydro-Québec TransÉnergie Original in French dated December
E6500 Power Quality Analyzer E6500 power quality analyzer can record and analyze all power quality parameters such as harmonics, voltage, current, frequency, fluctuation, flicker, power and three-phase
CHAPTER 4 Distribution Transformers Introduction A transformer is an electrical device that transfers energy from one circuit to another purely by magnetic coupling. Relative motion of the parts of the
W o r l d C l a s s P o w e r S o l u t i o n s Internal power supply UPS mains operation UPS battery operation Bypass operation Parallel operation Manual bypass Overload Inverter failure Mains failure
Harmonic Filters for Power Conversion Equipment (Drives, rectifiers, etc) Effects of Harmonics IEEE - 519 Solutions Harmonics Tutorial 1 Power Conversion Equipment can save energy and control motors, heaters,
DECATHLON DA80 The all around power Class-leading single rail with 70A @ 0 C 00% modular cables Dual PCI-E 8 pin connector & quad PCI-E 6 pin connectors Quiet running 0mm fan Support for ATX V. & EPS V
Power Plant and Transmission System Protection Coordination Volts Per Hertz (24), Undervoltage (27), Overvoltage (59), and Under/Overfrequency (81) Protection System Protection and Control Subcommittee
Electrical Energy Saving and Economic Benefits from Power System Harmonics Mitigation in the Petrochemical Plants Sherif M. Ismael Electrical Engineering Division, Engineering for the Petroleum and Process
COURSE FILE POWER SYSTEM ENGINEERING Name Branch Session Semester : Dr. Dinesh Birla : Electrical Engineering : 2012-13, Odd Semester : B. Tech VII Semester Index: Course File Sr. No. 1 Students Detail
Power Quality Overview October 2015 Dan Carnovale, PSEC Manager firstname.lastname@example.org 2007 2013 Eaton Corporation. All rights reserved. Power Quality Events Outage 1 Surge 2 Swell 3 Sag 4 Harmonics
Grid Converters for Photovoltaic and Wind Power Systems by R. Teodorescu, M. Liserre and P. Rodriguez ISBN: 978 0 470 05751 3 Copyright Wiley 2011 Chapter 3 Grid Requirements for PV Grid connection requirements
Utility System Lightning Protection Many power quality problems stem from lightning. Not only can the high-voltage impulses damage load equipment, but the temporary fault that follows a lightning strike
Thyristor Based Static Transfer Switch: Theory, Modeling and Analysis M. N. Moschakis* N. D. Hatziargyriou National Technical University of Athens Department of Electrical and Computer Engineering 9, Iroon
The world is changing but our power is constant...... Su-Kam Online UPS Su-Kam Power Systems Ltd. Corporate Office: Plot No. 54, Udyog Vihar Phase VI, Sector-37, Gurgaon-122001, Haryana, India. Tel.:+91-124-4030700,4170500,Fax:+91-124-4038700/1/2.
Agenda High Power MW and LW The NX Series Complete system packages Some examples MDCL makes $ence! AUI functionality Nautel Commissioning, Training and Support Your Questions Chuck Kelly Director of Sales