2 Common Topics, The Practical Side Machine Output Voltage Equation Pitch Harmonics Circulating Currents when Paralleling Reactances and Time Constants Three Generator Curves Used for System Coordination Thermal Damage Curve Decrement Curve Reactive Capability Efficiency Parallel Operation
3 What Determines Voltage Output? E = 4 f fb kd kp N F, where f = Frequency of operation which correlates to the difference in relative speeds of the field and conductors fb = Shape of the magnetic flux wave arising from rotor lamination design kd = Winding distribution factor related to winding details kp = Winding pitch N = Number of turns per phase in winding F = Total magnetic flux per pole, which includes machine stack length and operating magnetic flux density
4 Application of V Output Equation E = 4 f fb kd kp N F What if we want a 60 Hz machine to run at 50 Hz too? f decreases by a ratio of 50/60 E will also decrease by a ratio of 50/60 unless another factor changes: Increase magnetic flux densities (F)? May not be possible due to material characteristics. Can cause excess heating. Increase stack length (F) Increases cost. Change other aspect of the design, including different laminations and different winding configuration or turns.
5 Common Topics, The Practical Side Machine Output Voltage Equation Pitch Harmonics Circulating Currents when Paralleling Reactances and Time Constants Three Generator Curves Used for System Coordination Thermal Damage Curve Decrement Curve Reactive Capability Efficiency Parallel Operation
6 Pitch: Pole and Winding Pole pitch is the mechanical angle between adjacent poles, e.g. 4 pole = 90º. Winding pitch is the coil span divided by the pole pitch, e.g. 60º / 90º = 2/3. Key design factors include number of poles, number of slots, and number of slots spanned by coils. 1-9 coil span
7 Pitch: Common Values Specified Optimum pitch allows the designer flexibility used to balance generator performance to effectively utilize the generator s active materials. 2/3 pitch is often specified because it reduces 3rd harmonic content. However this may require a larger machine to meet the power ratings. Lower pitches E = 4 f fb kd kp N F kp decreases with lower pitch. If the voltage is to remain the same, something else has to increase. Increase magnetic flux densities Increase stack length Increase turns Use a different lamination set
8 Pitch: Effects When Reduced Coils spanning anything less than the full distance from pole to pole are called short-pitched. Reactances are reduced as pitch decreases (keeping all other design factors). Harmonics are generally reduced more than the fundamental, and specific harmonics can be cancelled entirely. 2/3 pitch reduces 3rd harmonic L-N at the expense of increasing 5th and 7th harmonics. There is never a 3rd harmonic L-L on a balanced system. Generator may need to be oversized to meet its rated power output and temperature.
9 Common Topics, The Practical Side Machine Output Voltage Equation Pitch Harmonics Circulating Currents when Paralleling Reactances and Time Constants Three Generator Curves Used for System Coordination Thermal Damage Curve Decrement Curve Reactive Capability Efficiency Parallel Operation
10 Harmonics Purely sinusoidal (clean and smooth) waveforms are desirable. Clean and smooth waveforms minimizes sudden changes in voltages, currents and power. Power system waveforms typically are NOT clean and smooth. Pure sinusoidal waveform Note: Example is for demonstration purpose only and is not typical of generator waveforms. It shows exaggerated harmonics without phase shift. Waveform with harmonics
11 Harmonics (cont.) Signals can be broken into a main (fundamental) sinusoidal (smooth) waveform and a series other smooth waveforms at frequencies that are multiples of the fundamental waveform frequency. Signal Main Harmonics Harmonics are the extra signals other than the fundamental waveform. Lowest harmonic usually has highest amplitude. Specifications call out individual harmonic limits as well as total harmonic distortion (THD).
12 Harmonics (cont.): Signal Breakdown Signal --- fundamental --- Signal --- fund+3 rd +5th --- Signal --- fund+3rd --- Signal --- fund+3 rd +5 th +7th ---
13 Load-Induced Distortion Example Pictured below is a real waveform that has notching caused by SCR loads This increased harmonic content and the issues associated with higher harmonics.
14 Harmonics (cont.): Resultant Problems Insulation systems may stress and get damaged. Generator components may overheat, requiring derating of the generator. Motors on the system may experience overheating, high audible noise or increased torque ripple. Transformers may overheat due to harmonic flux core losses. Power factor correction capacitors and other electronic equipment may receive excess currents and/or voltages. Telephone systems may get interfered with by higher order harmonics - telephone-influence factor (TIF).
16 Common Topics, The Practical Side Machine Output Voltage Equation Pitch Harmonics Circulating Currents when Paralleling Reactances and Time Constants Three Generator Curves Used for System Coordination Thermal Damage Curve Decrement Curve Reactive Capability Efficiency Parallel Operation
17 Circulating Currents When Paralleling Circuit diagram is of two generators in parallel. When there are differences in specific harmonics (3rd harmonic in this diagram) then circulating currents will flow through the generators + Ic + _ V 3A X o A _ V 3B X o B I C = V 3A -V 3B 3 (X 0A + X 0B ) V 3 is L-N third harmonic voltage. X 0 is zero-sequence reactance of each source (including external grounding reactance).
18 Circulating Currents When Paralleling For non-2/3 pitch generators, the key harmonic is the third The difference in third harmonic voltage is the driving force behind circulating currents. It flows in neutral and can cause false tripping of the differential protection relay and other problems. The grounding method used can greatly decrease current magnitudes. Identical generator pitch does NOT guarantee successful parallel operation. + Ic + _ V 3A X o A _ V 3B X o B
19 Common Topics, The Practical Side Machine Output Voltage Equation Pitch Harmonics Circulating Currents when Paralleling Reactances and Time Constants Three Generator Curves Used for System Coordination Thermal Damage Curve Decrement Curve Reactive Capability Efficiency Parallel Operation
20 Reactances Reactance is the opposition to AC current flow (like resistance, but recall that there are more than just simple toasters in power systems). Reactances are used to describe the behavior of a generator during certain operating conditions. X d is used in motor starting calculations. - lower X d results in better motor starting (i.e. lower voltage dip). X d is used in short-circuit current and arc flash calculations. - lower X d results in higher short circuit currents. There are other reactances for different situations. - e.g. direct and quadrature axis, zero and negative sequence, saturated and unsaturated.
21 Reactances (Cont.) Test method to obtain X d, X d: Machine operating at rated voltage, no-load, manual excitation Short circuit is applied across all three phases simultaneously Current envelope in each phase is captured over time as it decays Sample data
22 Time Constants Time constants characterize the length of time that currents flow during a specific instant in time of a given configuration. The two most common are the subtransient time constant T d and the transient time constant T. Sub-transient time constant T d determines length of time sub-transient (damper) current flows. Transient time constant T d determines length of time transient current flows.
23 Time Constants
24 Time Constants (cont.) Another time constant example: Open circuit transient T d0. This represents the decay in armature output voltage when main field excitation is lost This requires a different test setup than previously mentioned time constants: slip rings to manually control the main field.
25 Reactances, Time Constants: Why are they Important? Very useful to predict performance in large system simulations because they simplify and speed up calculations. Now, for many users, the reactances and time constants are plugged into simulators used for system modeling and coordination studies. Generator manufacturers use this information to produce three curves commonly used for system coordination: Thermal damage curve Short-circuit decrement curve Reactive Capability
26 Common Topics, The Practical Side Machine Output Voltage Equation Pitch Harmonics Circulating Currents when Paralleling Reactances and Time Constants Two Generator Curves Used for System Coordination Thermal Damage Curve Decrement Curve Reactive Capability Efficiency Parallel Operation
27 Thermal Damage Curve Plot of armature current vs. time for the class of insulation provided. Sample damage curve for a Class-H insulated, Class F rise machine.
28 Short-Circuit Decrement Curve Plot of fault current vs. time that the generator produces for various fault conditions PH, SYM, NL, MAN, HOT PER UNIT LINE CURRENT PH, SYM, NL, REG, HOT 3PH, ASYM, FL, REG, COLD L-L, SYM, NL, MAN, HOT L-L, ASYM, FL, REG, HOT L-N, SYM, NL, MAN. HOT L-N, ASYM, FL, REG, HOT TIME IN SECONDS
29 Reactive Capability Curve 3000 Inductive Load Capacitive Load Leading -- Reactive Load kvar -- Lagging (Power Factor) Power (kw) Limited by rotor heating Limited by stator heating Limited by control stability Limited by dynamic stability
30 Common Topics, The Practical Side Machine Output Voltage Equation Pitch Harmonics Circulating Currents when Paralleling Reactances and Time Constants Three Generator Curves Used for System Coordination Thermal Damage Curve Decrement Curve Reactive Capability Efficiency Parallel Operation
31 Efficiency Ratio of electrical energy output against the required mechanical energy input. Usually expressed as a percentage and always less than 100 percent. Usually improves with increasing sizes. For a 5 kw output, a typical efficiency is about 80%. For a 500 kw output, efficiency is typically 93% or better. Reduced by losses: Fixed losses (independent of load current) Variable losses (directly proportional to load current)
32 Efficiency: Fixed Losses Fixed losses Friction and windage losses: Bearing friction and wind resistance spinning rotor and associated fans Reduce by optimizing fan blade pitch Laminated core losses: Hysteresis Heat losses in the stator core due to change in magnetic flux flow Reduce by using low-loss silicon steel Eddy-current losses Loses due to induced current in the stator core Reduce by using low-loss silicon steel
33 Efficiency: Variable Losses Variable losses I 2 R losses in the armature and field coils Losses in the form of heat due to resistance in the windings Main armature I 2 R losses can be reduced by using insulation with higher dielectric strength and adding more copper. Main field I 2 R losses can be reduced by controlling the load power factor and reducing excitation requirements. Brushless exciter losses are typically negligible. Stray losses Due to changes in the flux distribution, eddy currents, and highorder harmonics. Can be reduced by using higher cost materials for the lamination clamping plates and stranding the armature copper into thinner cross sections.
34 Efficiency: Example Assume a generator is 90 percent efficient; that means if 1000 kw is applied to the generator shaft, only 900 kw can be extracted as electrical energy. The prime mover must provide the real power of the alternator. One horsepower is equal to kw. So, for a generator to deliver 900 kw of three-phase power at 90% efficiency, a prime mover with the following horsepower is required (no capability for overload is included): 900 kw = 1340 HP 0.9 efficiency x kw per HP
35 Common Topics, The Practical Side Machine Output Voltage Equation Pitch Harmonics Circulating Currents when Paralleling Reactances and Time Constants Three Generator Curves Used for System Coordination Thermal Damage Curve Decrement Curve Reactive Capability Efficiency Parallel Operation
36 Parallel Operation: Basics The generators share the power needed by the load. The operating points will depend on the load and set ups Why? To increase the power of an installation, To add flexibility, reliability or dependability. G1 Load G2
37 Requirements Must have +/- the same Frequency Voltage Phase angle Phase sequence The voltage regulator must have parallel operation capability and fitted with a paralleling CT or be controlled by a bias signal coming from the genset controller. The active and reactive power sharing must be balanced or prorated if they are of different sizes.
38 Metering Required V A kw Volts 60 Amperes Watts Hz Frequency Cos ᵠ or A PF or exciter field current
39 Synchronizing Parameters: Frequency DF = +/- 0.2% Ex. For 60 Hz: Period min = ms Period max = ms (Speed must be practically equal!) -100 t Maximum frequency shift: ± 0.12 Hz
40 Synchronizing Parameters: Voltage 150 %(Un) 100 U t Maximum voltage difference: ±5%
41 Synchronizing Parameters: Phase %(Un) t Maximum phase offset: ±10
42 Synchronizing Parameters: Phase Order Clockwise rotation from drive end Generator terminals U1 -V1 -W1 T1 -T2 -T3 Network connections L1 - L2 - L3 U2 V2 W2 CCW rotation From drive end Generator terminals U1 -V1 -W1 T1 -T2 -T3 Network connections L3 - L2 - L1 U2 V2 W2 U1 V1 W1 U1 V1 W1 L1 L2 L3 L3 L2 L1
43 Sequence 1. Verify the wiring and polarity of the sensing voltage and paralleling CT. 2. Equalize perfectly the no-load voltage of each generator. 3. Set the same droop for each generator. 4. Run the generators at the same voltage, phase sequence, frequency and phase angle. 5. Monitor the meters as you close the breaker and open it if the Amp meter fluctuates wildly. 6. After closing the breaker, adjust the engine governors per their power. 7. Ensure the reactive power of identical sets is roughly the same without any voltage adjustment.
44 Summary When an generator is running in island mode supplying power to a load or a factory, there is no requirement to synchronize it. The engine will regulate the RPM or the frequency and voltage regulator will regulate the voltage and the load connected will dictate how much power is drawn. When more than one generator run together or with the utility, it is necessary to synchronize them together. In order to synchronize one generator with another unit or with the mains, both sinusoidal wave forms must match. Any greater-than-rated difference could damage the generator to be synchronized.
GENERATOR DATA JANUARY 30, 2015 For Help Desk Phone Numbers Click here Generator Specification Frame: 1822 Type: SR5 No. of Bearings: 2 Winding Type: FORM WOUND Flywheel: 21.0 Connection: SERIES STAR Housing:
SYNCHRONOUS MACHINES The geometry of a synchronous machine is quite similar to that of the induction machine. The stator core and windings of a three-phase synchronous machine are practically identical
Unit 4 AC s UNIT OBJECTIVE After completing this unit, you will be able to demonstrate and explain the operation of ac induction motors using the Squirrel-Cage module and the Capacitor-Start Motor module.
Effects of Harmonic Distortion I Harmonic currents produced by nonlinear loads are injected back into the supply systems. These currents can interact adversely with a wide range of power system equipment,
Power Plant and Transmission System Protection Coordination Reverse Power (32), Negative Sequence Current (46), Inadvertent Energizing (50/27), Stator Ground Fault (59GN/27TH), Generator Differential (87G),
Placement Paper For Electrical Q.1 The two windings of a transformer is (A) conductively linked. (B) inductively linked. (C) not linked at all. (D) electrically linked. Ans : B Q.2 A salient pole synchronous
Exclusive e-rated Provider PRODUCT SHEET HARMITIGATOR TM Low Pass Harmonic Filters A solution for electrical distribution systems that require stable, reliable power, characterized by unparalleled power
- Winding 312 Technical Data Sheet SPECIFICATIONS & OPTIONS STANDARDS Stamford industrial generators meet the requirements of BS EN 60034 and the relevant sections of other national and international standards
- Winding 312 Technical Data Sheet SPECIFICATIONS & OPTIONS STANDARDS Stamford industrial generators meet the requirements of BS EN 60034 and the relevant sections of other national and international standards
3.1.Introduction Synchronous Machines A synchronous machine is an ac rotating machine whose speed under steady state condition is proportional to the frequency of the current in its armature. The magnetic
Harmonics and Their Impact on Power Quality Wayne Walcott Application Engineering Manager June, 2017 Presentation Overview A little about harmonics What are harmonics What are NOT harmonics What creates
PM734D - Winding 312 Technical Data Sheet PM734D SPECIFICATIONS & OPTIONS STANDARDS Marine generators may be certified to Lloyds, DnV, Bureau Veritas, ABS, Germanischer-Lloyd or RINA. Other standards and
Application Guidance Notes: Technical Information from Cummins Generator Technologies AGN 087 Power Factor DEFINITIONS What is Power Factor? Power factor is a way of identifying the electrical relationship
VIDYARTHIPLUS - ANNA UNIVERSITY ONLINE STUDENTS COMMUNITY UNIT 1 DC MACHINES PART A 1. State Faraday s law of Electro magnetic induction and Lenz law. 2. Mention the following functions in DC Machine (i)
MAIN TOPICS DISCUSSED Electric Rates Electrical system utilization ELECTRICAL SYSTEMS AND ELECTRIC ENERGY MANAGEMENT SECTION K Power quality Harmonics Power factor (Cos phi) improvement Section K - 2 ELECTRIC
PRACTICALWORKBOOK Electrical Machines (EE-343) For TE (ELECTRICAL) Name: Roll Number: Year: Batch: Section: Semester: Department: N.E.D University of Engineering &Technology, Karachi Electrical Machines
Inductance, capacitance and resistance As previously discussed inductors and capacitors create loads on a circuit. This is called reactance. It varies depending on current and frequency. At no frequency,
Alternators Reactance for Nonlinear Loads Allen Windhorn. P.E. 26 July, 2013 Introduction Widespread invocation of IEEE Std 519 on systems powered by generators, together with increased use of equipment
Course Name Course Code Class Branch INSTITUTE OF AERONAUTICAL ENGINEERING (Autonomous) Dundigal, Hyderabad - 500 043 ELECTRICAL AND ELECTRONICS ENGINEERING QUESTION BANK : ELECRICAL MACHINES I : A40212
Alternating Current 26201 11 Page 1 30 Calculate the peak and effective voltage of current values for AC Calculate the phase relationship between two AC waveforms Describe the voltage and current phase
1 DC Motor The direct current (dc) machine can be used as a motor or as a generator. DC Machine is most often used for a motor. The major adantages of dc machines are the easy speed and torque regulation.
IOCL Electrical Engineering Technical Paper 1. Which one of the following statements is NOT TRUE for a continuous time causal and stable LTI system? (A) All the poles of the system must lie on the left
INTERCONNECTION REQUEST FOR A LARGE GENERATING FACILITY Internal Use Only Date Received Time Received Received By: 1. The undersigned Interconnection Customer submits this request to interconnect its Large
Engineering data submittal Page 1 WHO SHOULD FILE THIS SUBMITTAL : Anyone in the final stages of in terconnecting a Generation System with Otter Tail Power. This submittal shall be completed and provided
KINGS COLLEGE OF ENGINEERING DEPARTMENT OF ELECTRICAL AND ELECTRONICS ENGINEERING ACADEMIC YEAR 2010-2011 / EVEN SEMESTER QUESTION BANK SUBJECT CODE & NAME: EE 1352 - ELECTRICAL MACHINE DESIGN YEAR / SEM
Three-Phase Induction Motors 1 2 3 Classification of AC Machines 1. According to the type of current Single Phase and Three phase 2. According to Speed Constant Speed, Variable Speed and Adjustable Speed
UNIT II MEASUREMENT OF POWER & ENERGY Dynamometer type wattmeter works on a very simple principle which is stated as "when any current carrying conductor is placed inside a magnetic field, it experiences
Analysis of Harmonic Distortion in Non-linear Loads Anne Ko Department of Electrical Power Engineering Mandalay Technological University, Mandalay, Myanmar.Phone:+95-09-2225761 email@example.com Wunna
1991 1.12 The operating state that distinguishes a silicon controlled rectifier (SCR) from a diode is (a) forward conduction state (b) forward blocking state (c) reverse conduction state (d) reverse blocking
EVALUATION OF REACTANCES AND TIME CONSTANTS OF SYNCHRONOUS GENERATOR Shaheena Khanum 1, K.L Ratnakar 2, Ramesh K.N 3, Ravi.R 4 1 PG Student, Department of Electrical and Electronics Engineering, Sri Siddhartha
1. Which of the following is the major consideration to evolve a good design? (a) Cost (b) Durability (c) Compliance with performance criteria as laid down in specifications (d) All of the above 2 impose
Chapter L Power factor correction and 1 2 3 4 5 6 7 8 9 10 Contents Reactive energy and power factor 1.1 The nature of reactive energy L2 1.2 Equipment and appliances requiring reactive energy L2 1.3 The
Power Quality Monitoring and Power Metering Tutorial Power generation and transmission today are accomplished using three phase alternatingcurrent. To understand electrical power quality monitoring and
WHITE PAPER Medium Voltage On-Site Generation Overview BY MIKE KIRCHNER Technical Support Manager at Generac Power Systems INTRODUCTION It seems that just about everyone is looking for more power. As our
Our energy working for you. TM Power topic #9016 Technical information from Cummins Power Generation Paralleling Dissimilar Generators: Part 2 Compatible Alternators White Paper By Gary Olson, Director
and Drives Control R Interface OBICON Perfect Harmony Short overview 14.03.2007 1 System overview Product features Truly Scaleable Technology 300 kw to 30 MW (Single Channel) Large Number of Framesizes
22 CHAPTER 2 D-Q AXES FLUX MEASUREMENT IN SYNCHRONOUS MACHINES 2.1 INTRODUCTION For the accurate analysis of synchronous machines using the two axis frame models, the d-axis and q-axis magnetic characteristics
90 16 kva - 0 Hz 1 6 kva - 60 Hz 38 en - 11.04 / g PARTNER ALTERNATORS LSA 44.2-4 Pole Electrical and mechanical data SPECIALLY ADAPTED FOR APPLICATIONS The LSA 44.2 alternator is designed to be suitable
Thermal Imaging, Power Quality and Harmonics Authors: Matthew A. Taylor and Paul C. Bessey of AVO Training Institute Executive Summary Infrared (IR) thermal imaging (thermography) is an effective troubleshooting
29 CHAPTER 2 STATE SPACE MODEL OF BLDC MOTOR 2.1 INTRODUCTION Modelling and simulation have been an essential part of control system. The importance of modelling and simulation is increasing with the combination
UNIT II MEASUREMENT OF POWER AND ENERGY PART-A 1. A 3 500 V motor load has a pf of 0.4. Two wattmeters connected to measure the input. They show the input to be 30 kw. Find the reading of each instrument
CHAPTER 4 Distribution Transformers Introduction A transformer is an electrical device that transfers energy from one circuit to another purely by magnetic coupling. Relative motion of the parts of the
Al-Balqa Applied University Power systems Protection course Department of Electrical Energy Engineering 1 Part 5 Relays 2 3 Relay Is a device which receive a signal from the power system thought CT and
Design a Power System Simulator Model and Implement the Generator and Motor Controlling G.U De Silva, G.B Alahendra, A.C.P Aluthgama, P.G.L Arachchi Supervised by: Prof. J Rohan Lucas, Eng. J. Karunanayake
UNIVERSITY OF TECHNOLOGY DEPARTMENT OF ELECTRICAL ENGINEERING Year: Second 2016-2017 By: Fadhil A. Hasan ELECTRICAL MACHINES І Module-II: AC Transformers o Single phase transformers o Three-phase transformers
CHAPTER 5 CONCEPTS OF ALTERNATING CURRENT INTRODUCTION Thus far this text has dealt with direct current (DC); that is, current that does not change direction. However, a coil rotating in a magnetic field
Excitation and Control of a High-Speed Induction Generator by Steven Carl Englebretson S.B., Colorado School of Mines (Dec 2002) Submitted to the Department of Electrical Engineering and Computer Science
Power Plant and Transmission System Protection Coordination Volts Per Hertz (24), Undervoltage (27), Overvoltage (59), and Under/Overfrequency (81) Protection System Protection and Control Subcommittee
International Journal of Electrical Engineering. ISSN 974-2158 Volume 5, Number 3 (212), pp. 329-334 International Research Publication House http://www.irphouse.com Inter Harmonics of Cycloconveter Excited
Synchronous Generators II EE 340 Generator P-f Curve All generators are driven by a prime mover, such as a steam, gas, water, wind turbines, diesel engines, etc. Regardless the power source, most of prime
Harmonic Filters and Reactors Harmonics are invisible but costly If one looks up the meaning of harmonics in any one of several technical dictionaries, it is normally defined as being A sinusoidal component
Electric Power / Controls Courseware Sample 85822-F0 A ELECTRIC POWER / CONTROLS COURSEWARE SAMPLE by the Staff of Lab-Volt Ltd. Copyright 2009 Lab-Volt Ltd. All rights reserved. No part of this publication
White Paper New Redundant Automatic Voltage Regulator (AVR) Solution Author: David R. Brown, Turbomachinery Control Solutions Senior Consultant, Invensys Operations Management What s Inside: 1. Introduction
IEEE TRANSACTIONS ON ENERGY CONVERSION, VOL. 16, NO. 1, MARCH 2001 55 Analysis of Indirect Temperature-Rise Tests of Induction Machines Using Time Stepping Finite Element Method S. L. Ho and W. N. Fu Abstract
Problems connected with Commissioning of Power Transformers ABSTRACT P Ramachandran ABB India Ltd, Vadodara, India While commissioning large Power Transformers, certain abnormal phenomena were noticed.
This manual must be sent to the end user X2 Z1 X1 Z2 E+ E- J1 t (12V - 10A) ~ 10 ohms Exciter field + - Isolated DC power supply Installation and maintenance WARNING TO AVOID HARM EITHER TO PEOPLE OR TO
EE401,EC401,DEE19,DETE19 IV SEMESTER DIPLOMA EXAMINATION, JANUARY 2013 LINEAR & DIGITAL ICs Time: 3 Hours Max. Marks: 75 GROUP A : Answer any three questions. (Question No. 1 is compulsory) Q.1 What is
P2 Power Solutions Pvt. Ltd. An ISO 9001:2008 Company Quality Power within your Reach P2 Power Magnetics P2 Power Solutions Pvt. Ltd. P2 Power Solutions Pvt. Ltd. provides EMC and power quality solutions,
Application Note Application Note Guidelines For The Use Of 400-600 Volt AC Drives In Medium Voltage Applications Applicable Product: AC Drives 4kV Step-down Transformer AC Drive 400-600V Output Filter
In The Truths About Transformers Part 1, the discussion focused on the reality that not all transformers are created equal. Today, more than ever, there is a need to look at every transformer application
Transformer Protection Principles 1. Introduction Transformers are a critical and expensive component of the power system. Due to the long lead time for repair of and replacement of transformers, a major
Design, Implementation, and Dynamic Behavior of a Power Plant Model M.M. A. Rahman, Member ASEE Grand Valley State University Grand Rapids, MI firstname.lastname@example.org Daniel Mutuku Consumers Energy West Olive,
Chapter 3 Design and Simulation of Passive Filter 3.1 Introduction Passive LC filters are conventionally used to suppress the harmonic distortion in power system. In general they consist of various shunt
Motor-CAD Brushless PM motor Combined electromagnetic and thermal model (February 2015) Description The Motor-CAD allows the machine performance, losses and temperatures to be calculated for a BPM machine.
Protecting Large Machines for Arcing Faults March 2, 2010 INTRODUCTION Arcing faults occur due to dirty insulators or broken strands in the stator windings. Such faults if undetected can lead to overheating
Failure of Transformers Due to Harmonic Loads 1 Jyotirmaya Ghadai, 2 Chinmay Das 1,2 Department of Electrical Engineering, Indira Gandhi Institute of Technology Email: 1 email@example.com, 2 Chinmaydas14@gmail.com
Power Quality and Circuit Imbalances 2015 Northwest Electric Meter School Presented by: Chris Lindsay-Smith McAvoy & Markham Engineering/Itron Summary of IEEE 1159 Terms Category Types Typical Duration
8 7 9 6 5 4 C 45 en -. / a R 45 DETECT. PH PH. SENSING 5 Hz EXT FREQ 6 Hz SETTING This manual is to be given to the end user VOLT. STAB. I EXC FUSIBLES / FUSES EXT.FREQ. SET. ON ONLY FOR SPECIAL CONFIG.
Electrical Engineering Division Page 1 of 10 Rectification is the process of conversion of alternating input voltage to direct output voltage. Rectifier is a circuit that convert AC voltage to a DC voltage
Contents Figures Tables Preface xi vii xiii Acknowledgments About the Author xv xvii Chapter 1. Basic Mathematics 1 Addition 1 Subtraction 2 Multiplication 2 Division 3 Exponents 3 Equations 5 Subscripts
CONTENTS C H A P T E R46 Learning Objectives es Classes of Electronic AC Drives Variable Frequency Speed Control of a SCIM Variable Voltage Speed Control of a SCIM Chopper Speed Control of a WRIM Electronic
EE 340 Transmission Lines Physical Characteristics Overhead lines An overhead transmission line usually consists of three conductors or bundles of conductors containing the three phases of the power system.
Code: AE10 PART - I Subject: TYPICAL QUESTIONS & ANSWERS OBJECTIVE TYPE QUESTIONS Q.1 The two windings of a transformer is (A) conductively linked. (C) not linked at all. (B) inductively linked. (D) electrically
Advanced electromagnetism and electromagnetic induction This worksheet and all related files are licensed under the Creative Commons Attribution License, version 1.0. To view a copy of this license, visit
DC CIRCUITS Part I of III Parts Part II installation Part III troubleshooting Trane ComfortSite is a user-friendly Internet site designed to save you time and it s FREE for Trane Customers. Order Equipment,
A COMPARISON STUDY OF THE COMMUTATION METHODS FOR THE THREE-PHASE PERMANENT MAGNET BRUSHLESS DC MOTOR Shiyoung Lee, Ph.D. Pennsylvania State University Berks Campus Room 120 Luerssen Building, Tulpehocken
Chapter 2 The Fundamentals of Electronics: A Review Topics Covered 2-1: Gain, Attenuation, and Decibels 2-2: Tuned Circuits 2-3: Filters 2-4: Fourier Theory 2-1: Gain, Attenuation, and Decibels Most circuits
HOME APPLICATION NOTES Iron Powder Cores for High Q Inductors By: Jim Cox - Micrometals, Inc. SUBJECT: A brief overview will be given of the development of carbonyl iron powders. We will show how the magnetic