1 CHAPTER CHAPTER 23 Protection of Busbars and Lines 23.1 Busbar Protection 23.2 Protection of Lines 23.3 Time-Graded Overcurrent Protection 23.4 Differential Pilot-Wire Protection 23.5 Distance Protection Introduction Busbars and lines are important elements of electric power system and require the immediate attention of protection engineers for safeguards against the possible faults occurring on them. The methods used for the protection of generators and transformers can also be employed, with slight modifications, for the busbars and lines. The modifications are necessary to cope with the protection problems arising out of greater length of lines and a large number of circuits connected to a busbar. Although differential protection can be used, it becomes too expensive for longer lines due to the greater length of pilot wires required. Fortunately, less expensive methods are available which are reasonably effective in providing protection for the busbars and lines. In this chapter, we shall focus our attention on the various methods of protection of busbars and lines Busbar Protection Busbars in the generating stations and sub-stations form important link between the incoming and outgoing circuits. If a fault occurs on a busbar, considerable damage and disruption of supply will occur unless some form of quick-acting automatic 541
2 Principles of Power System protection is provided to isolate the faulty busbar. The busbar zone, for the purpose of protection, includes not only the busbars themselves but also the isolating switches, circuit breakers and the associated connections. In the event of fault on any section of the busbar, all the circuit equipments connected to that section must be tripped out to give complete isolation. The standard of construction for busbars has been very high, with the result that bus faults are extremely rare. However, the possibility of damage and service interruption from even a rare bus fault is so great that more attention is now given to this form of protection. Improved relaying methods have been developed, reducing the possibility of incorrect operation. The two most commonly used schemes for busbar protection are : (i) Differential protection (ii) Fault bus protection (i) Differential protection. The basic method for busbar protection is the differential scheme in which currents entering and leaving the bus are totalised. During normal load condition, the sum of these currents is equal to zero. When a fault occurs, the fault current upsets the balance and produces a differential current to operate a relay. Fig shows the single line diagram of current differential scheme for a station busbar. The busbar is fed by a generator and supplies load to two lines. The secondaries of current transformers in the generator lead, in line 1 and in line 2 are all connected in parallel. The protective relay is connected across this parallel connection. All CTs must be of the same ratio in the scheme regardless of the capacities of the various circuits. Under normal load conditions or external fault conditions, the sum of the currents entering the bus is equal to those leaving it and no current flows through the relay. If a fault occurs within the protected zone, the currents entering the bus will no longer be equal to those leaving it. The difference of these currents will flow through the relay and cause the opening of the generator, circuit breaker and each of the line circuit breakers. (ii) Fault Bus protection. It is possible to design a station so that the faults that develop are mostly earth-faults. This can be achieved by providing earthed metal barrier (known as fault bus) surrounding each conductor throughout its entire length in the bus structure. With this arrangement, every fault that might occur must involve a connection between a conductor and an earthed metal part. By directing the flow of earth-fault current, it is possible to detect the faults and determine their location. This type of protection is known as fault bus protection. Fig show the schematic arrangement of fault bus protection. The metal supporting structure or fault bus is earthed through a current transformer. A relay is connected across the secondary of this CT. Under normal operating conditions, there is no current flow from fault bus to ground and the relay remains inoperative. A fault involving a connection between a conductor and earthed sup-
3 543 Protection of Busbars and Lines 543 porting structure will result in current flow to ground through the fault bus, causing the relay to operate. The operation of relay will trip all breakers connecting equipment to the bus Protection of Lines The probability of faults occurring on the lines is much more due to their greater length and exposure to atmospheric conditions. This has called for many protective schemes which have no application to the comparatively simple cases of alternators and transformers. The requirements of line protection are : (i) In the event of a short-circuit, the circuit breaker closest to the fault should open, all other circuit breakers remaining in a closed position. (ii) In case the nearest breaker to the fault fails to open, back-up protection should be provided by the adjacent circuit breakers. (iii) The relay operating time should be just as short as possible in order to preserve system stability, without unnecessary tripping of circuits. The protection of lines presents a problem quite different from the protection of station apparatus such as generators, transformers and busbars. While differential protection is ideal method for lines, it is much more expensive to use. The two ends of a line may be several kilometres apart and to compare the two currents, a costly pilot-wire circuit is required. This expense may be justified but in general less costly methods are used. The common methods of line protection are : (i) Time-graded overcurrent protection (ii) Differential protection (iii) Distance protection Fig shows the symbols indicating the various types of relays.
4 Principles of Power System 23.3 Time-Graded Overcurr current Protection In this scheme of overcurrent protection, time discrimination is incorporated. In other words, the time setting of relays is so graded that in the event of fault, the smallest possible part of the system is isolated. We shall discuss a few important cases. 1. Radial feeder. The main characteristic of a radial system is that power can flow only in one direction, from generator or supply end to the load. It has the disadvantage that continuity of supply cannot be maintained at the receiving end in the event of fault. Time-graded protection of a radial feeder can be achieved by using (i) definite time relays and (ii) inverse time relays. (i) Using definite time relays. Fig shows the overcurrent protection of a radial feeder by definite time relays. The time of operation of each relay is fixed and is independent of the operating current. Thus relay D has an operating time of 0 5 second while for other relays, time delay* is successively increased by 0 5 second. If a fault occurs in the section DE, it will be cleared in 0 5 second by the relay and circuit breaker at D because all other relays have higher operating time. In this way only section DE of the system will be isolated. If the relay at D fails to trip, the relay at C will operate after a time delay of 0 5 second i.e. after 1 second from the occurrence of fault. The disadvantage of this system is that if there are a number of feeders in series, the tripping time for faults near the supply end becomes high (2 seconds in this case). However, in most cases, it is necessary to limit the maximum tripping time to 2 seconds. This disadvantage can be overcome to a reasonable extent by using inverse-time relays. (ii) Using inverse time relays. Fig shows overcurrent protection of a radial feeder using * The amount of time delay depends upon the speed of breaker tripping. Sufficient time delay must be allowed to permit the breaker on the faulted section to clear the fault before the next relay in the sequence trips. The time-delay usually varies from 0 25 second to 0 5 second.
5 545 Protection of Busbars and Lines 545 inverse time relays in which operating time is inversely proportional to the operating current. With this arrangement, the farther the circuit breaker from the generating station, the shorter is its relay operating time. The three relays at A, B and C are assumed to have inverse-time characteristics. A fault in section BC will give relay times which will allow breaker at B to trip out before the breaker at A. 2. Parallel feeders. Where continuity of supply is particularly necessary, two parallel feeders may be installed. If a fault occurs on one feeder, it can be disconnected from the system and continuity of supply can be maintained from the other feeder. The parallel feeders cannot* be protected by non-directional overcurrent relays only. It is necessary to use directional relays also and to grade the time setting of relays for Inverse Time Relay selective trippings. Fig shows the system where two feeders are connected in parallel between the generating station and the sub-station. The protection of this system requires that (i) each feeder has a non-directional overcurrent relay at the generator end. These relays should have inverse-time characteristic. (ii) each feeder has a reverse power or directional relay at the sub-station end. These relays should be instantaneous type and operate only when power flows in the reverse direction i.e. in the direction of arrow at P and Q. Suppose an earth fault occurs on feeder 1 as shown in Fig It is desired that only circuit breakers at A and P should open to clear the fault whereas feeder 2 should remain intact to maintain the continuity of supply. In fact, the above arrangement accomplishes this job. The shown fault is fed via two routes, viz. (a) directly from feeder 1 via the relay A (b) from feeder 2 via B, Q, sub-station and P Therefore, power flow in relay Q will be in normal direction but is reversed in the relay P. This causes the opening of circuit breaker at P. Also the relay A will operate while relay B remains inop- * Referring to Fig. 23.6, suppose relays at P and Q are non-directional type and their time settings are lower than relays at A and B. When a fault occurs at the shown point, the relay at Q will operate first and disconnect the feeder 2, and then feeder 1 will be cut off. Thus even the sound feeder (No. 2) is isolated.
6 Principles of Power System erative. It is because these relays have inverse-time characteristics and current flowing in relay A is in excess of that flowing in relay B. In this way only the faulty feeder is isolated. 3. Ring main system. In this system, various power stations or sub-stations are interconnected by alternate routes, thus forming a closed ring. In case of damage to any section of the ring, that section may be disconnected for repairs, and power will be supplied from both ends of the ring, thereby maintaining continuity of supply. Fig shows the single line diagram of a typical ring main system consisting of one generator G supplying four sub-stations S 1, S 2, S 3 and S 4. In this arrangement, power can flow in both directions under fault conditions. Therefore, it is necessary to grade in both directions round the ring and also to use directional relays. In order that only faulty section of the ring is isolated under fault conditions, the types of relays and their time settings should be as follows : (i) The two lines leaving the generating station should be equipped with non-directional overcurrent relays (relays at A and J in this case). (ii) At each sub-station, reverse power or directional relays should be placed in both incoming and outgoing lines (relays at B, C, D, E, F, G, H and I in this case). (iii) There should be proper relative time-setting of the relays. As an example, going round the loop G S 1 S 2 S 3 S 4 G ; the outgoing relays (viz at A, C, E, G and I) are set with decreasing time limits e.g. A = 2 5 sec, C = 2 sec, E = 1 5 sec G = 1 sec and I = 0 5 sec Similarly, going round the loop in the opposite direction (i.e. along G S 4 S 3 S 2 S 1 G), the outgoing relays (J, H, F, D and B) are also set with a decreasing time limit e.g. J = 2 5 sec, H = 2 sec, F = 1 5 sec, D = 1 sec, B = 0 5 sec. Suppose a short circuit occurs at the point as shown in Fig In order to ensure selectivity, it is desired that only circuit breakers at E and F should open to clear the fault whereas other sections of the ring should be intact to maintain continuity of supply. In fact, the above arrangement accomplishes this job. The power will be fed to the fault via two routes viz (i) from G around S 1 and S 2 and (ii) from G around S 4 and S 3. It is clear that relays at A, B, C and D as well as J, I, H and G will not trip. Therefore, only relays at E and F will operate before any other relay operates because of their lower time-setting Differ ferential ential Pilot-Wir ire e Protection The differential pilot-wire protection is based on the principle that under normal conditions, the current entering one end of a line is equal to that leaving the other end. As soon as a fault occurs between the two ends, this condition no longer holds and the difference of incoming and outgoing currents is arranged to flow through a relay which operates the circuit breaker to isolate the faulty line. There are several differential protection schemes in use for the lines. However, only the follow-
7 547 Protection of Busbars and Lines 547 ing two schemes will be discussed : 1. Merz-Price voltage balance system 2. Translay scheme 1. Merz-Price voltage balance system. Fig shows the single line diagram of Merz- Price voltage balance system for the protection of a 3-phase line. Identical current transformers are placed in each phase at both ends of the line. The pair of CTs in each line is connected in series with a relay in such a way that under normal conditions, their secondary voltages are equal and in opposition i.e. they balance each other. Under healthy conditions, current entering the line at one-end is equal to that leaving it at the other end. Therefore, equal and opposite voltages are induced in the secondaries of the CTs at the two ends of the line. The result is that no current flows through the relays. Suppose a fault occurs at point F on the line as shown in Fig This will cause a greater current to flow through CT 1 than through CT 2. Consequently, their secondary voltages become unequal and circulating current flows through the pilot wires and relays. The circuit breakers at both ends of the line will trip out and the faulty line will be isolated. Fig shows the connections of Merz-Price voltage balance scheme for all the three phases of the line.
8 Principles of Power System Advantages (i) This system can be used for ring mains as well as parallel feeders. (ii) This system provides instantaneous protection for ground faults. This decreases the possibility of these faults involving other phases. (iii) This system provides instantaneous relaying which reduces the amount of damage to overhead conductors resulting from arcing faults. Disadvantages (i) Accurate matching of current transformers is very essential. (ii) If there is a break in the pilot-wire circuit, the system will not operate. (iii) This system is very expensive owing to the greater length of pilot wires required. (iv) In case of long lines, charging current due to pilot-wire capacitance* effects may be sufficient to cause relay operation even under normal conditions. (v) This system cannot be used for line voltages beyond 33 kv because of constructional difficulties in matching the current transformers. 2. Translay scheme. This system is similar to voltage balance system except that here balance or opposition is between the voltages induced in the secondary windings wound on the relay magnets and not between the secondary voltages of the line current transformers. This permits to use current transformers of normal design and eliminates one of the most serious limitations of original voltage balance system, namely ; its limitation to the system operating at voltages not exceeding 33 kv. The application of Translay scheme for a single phase line has already been discussed in Art This can be extended to 3-phase system by applying one relay at each end of each phase of the 3-phase line. However, it is possible to make further simplification by combining currents derived from all phases in a single relay at each end, using the principle of summation transformer (See Fig ). A summation transformer is a device that reproduces the polyphase line currents as a single-phase quantity. The three lines CTs are connected to the tapped primary of summation transformer. Each line CT energises a different number of turns (from line to neutral) with a resulting single phase output. The use of summation transformer permits two advantages viz (i) primary windings 1 and 2 can be used for phase faults whereas winding 3 can be used for earth fault (ii) the number of pilot wires required is only two. Schematic arrangement. The Translay scheme for the protection of a 3-phase line is shown in Fig The relays used in the scheme are essentially overcurrent induction type relays. Each relay has two electromagnetic elements. The upper element carries a winding (11 or 11 a) which is energised as a summation transformer from the secondaries of the line CTs connected in the phases of the line to be protected. The upper element also carries a secondary winding (12 or 12 a) which is connected is series with the operating winding (13 or 13 a) on the lower magnet. The secondary windings 12, 12 a and operating windings 13, 13 a are connected in series in such a way that voltages induced in them oppose each other. Note that relay discs and tripping circuits have been omitted in the diagram for clarity. * This drawback is overcome in the Beard-Hunter system. In this system, each pilot-wire is surrounded by an insulated metallic sheath with a break half-way along its length. Half the pilot charging current thus comes from the sending end and half from the receiving end. Therefore, voltage applied to the relay at the sending end is balanced by an equal voltage at the receiving end.
9 549 Protection of Busbars and Lines 549 Operation. When the feeder is sound, the currents at its two ends are equal so that the secondary currents in both sets of CTs are equal. Consequently, the currents flowing in the relay primary winding 11 and 11 a will be equal and they will induce equal voltages in the secondary windings 12 and 12a. Since these windings are connected in opposition, no current flows in them or in the operating windings 13 and 13a. In the event of a fault on the protected line, the line current at one end must carry a greater current than that at the other end. The result is that voltages induced in the secondary windings 12 and 12 a will be different and the current will flow through the operating coils 13, 13a and the pilot circuit. Under these conditions, both upper and lower elements of each relay are energised and a forward torque acts on the each relay disc. The operation of the relays will open the circuit breakers at both ends of the line. (i) Suppose a fault F occurs between phases R and Y and is fed from both sides as shown in Fig This will energise only section 1 of primary windings 11 and 11a and induce voltages in the secondary windings 12 and 12a. As these voltages are now additive*, therefore, current will circulate through operating coils 13, 13a and the pilot circuit. This will cause the relay contacts to close and open the circuit breakers at both ends. A fault between phases Y and B energises section 2 of primary windings 11 and 11a whereas that between R and B will energise the sections 1 and 2. (ii) Now imagine that an earth fault occurs on phase R. This will energise sections 1, 2 and 3 of the primary windings 11 and 11a. Again if fault is fed from both ends, the voltages induced in the secondary windings 12 and 12a are additive and cause a current to flow through the operating coils 13, 13a. The relays, therefore, operate to open the circuit breakers at both ends of the line. In the event of earth fault on phase Y, sections 2 and 3 of primary winding 11 and 11a will be energised and cause the relays to operate. An earth fault on phase B will energise only section 3 of relay primary windings 11 and 11a. Advantages (i) The system is economical as only two pilot wires are required for the protection of a 3-phase line. (ii) Current transformers of normal design can be used. (iii) The pilot wire capacitance currents do not affect the operation of relays. * Because the fault is being fed from both sides.
10 Principles of Power System 23.5 Distance Protection Both time-graded and pilot-wire system are not suitable for the protection of very long high voltage transmission lines. The former gives an unduly long time delay in fault clearance at the generating station end when there are more than four or five sections and the pilot-wire system becomes too expensive owing to the greater length of pilot wires required. This has led to the development of distance protection in which the action of relay depends upon the distance (or impedance) between the point where the relay is installed and the point of fault. This system provides discrimination protection without employing pilot wires. The principle and operation of distance relays have already been discussed in chapter 21. We shall now consider its application for the protection of transmission lines. Fig (i) shows a simple system consisting of lines in series such that power can flow only from left to right. The relays at A, B and C are set to operate for impedance less than Z 1, Z 2 and Z 3 respectively. Suppose a fault occurs between sub-stations B and C, the fault impedance at power station and sub-station A and B will be Z 1 + Z and Z respectively. It is clear that for the portion shown, only relay at B will operate. Similarly, if a fault occurs within section AB, then only relay at A will operate. In this manner, instantaneous protection can be obtained for all conditions of operation. In actual practice, it is not possible to obtain instantaneous protection for complete length of the line due to inaccuracies in the relay elements and instrument transformers. Thus the relay at A [See Fig (i)] would not be very reliable in distinguishing between a fault at 99% of the distance AB and the one at 101% of distance AB. This difficulty is overcome by using three-zone distance protection shown in Fig (ii). In this scheme of protection, three distance elements are used at each terminal. The zone 1 element covers first 90% of the line and is arranged to trip instantaneously for faults in this portion. The zone 2 element trips for faults in the remaining 10% of the line and for faults in the next line section, but a time delay is introduced to prevent the line from being tripped if the fault is in the next section. The zone 3 element provides back-up protection in the event a fault in the next section is not cleared by its breaker.
11 551 Protection of Busbars and Lines 551 SELF - TEST 1. Fill in the blanks by inserting appropriate words/figures : (i) Differential protection scheme for longer lines is... costly. (ii) The bus-bar zone, for the purpose of protection, includes...,... and... (iii) The two most commonly used schemes for bus-bar protection are..., and... (iv) The probability of faults occurring on the lines is much more due to their... and... (v) In time-graded overcurrent protection,... discrimination is incorporated. 2. Pick-up the correct words/figures from the brackets and fill in the blanks : (i) The parallel feeders... be protected by non-directional overcurrent relays alone. (can, cannot) (ii) The Translay scheme is essentially a... balance system. (current, voltage) (iii) A summation transformer is a device that reproduces the polyphase line currents as a... phase quantity. (single, two) (iv) The ideal scheme of protection for lines is... protection. (differential, distance) (v) Accurate matching of current transformers is... in Merz-Price voltage balance system. (essential, not essential) ANSWERS TO SELF-TEST 1. (i) very (ii) bus-bars, isolating switches, circuit breakers (iii) differential protection, fault bus protection (iv) greater length, exposure to atmospheric conditions (v) time 2. (i) cannot (ii) voltage (iii) single (iv) differential (v) essential CHAPTER REVIEW TOPICS 1. What is the importance of bus-bar protection? 2. Describe the following systems of bus-bar protection : (i) Differential protection (ii) Fault-bus protection 3. What are the requirements of protection of lines? 4. Discuss the time-graded overcurrent protection for (i) Radial feeders (ii) Parallel feeders (iii) Ring main system 5. Describe the differential pilot wire method of protection of feeders. 6. Explain the Translay protection scheme for feeders. 7. Describe distance protection scheme for the protection of feeders. 8. Write short-notes on the following : (i) Fault-bus protection (ii) Merz-Price voltage balance system for protection of feeders (iii) Translay scheme DISCUSSION QUESTIONS 1. What methods can be used to prevent saturation of current transformers? 2. What factors govern choosing pilot-wire installation? 3. Why must directional relays be used on a ring main system? 4. How do time-delay overcurrent relays work on a radial system? 5. Do overhead systems need differential protection schemes than underground systems? 6. How are pilot-wire relays built for transmission-line protection?
Application of Low-Impedance 7SS601 Busbar Differential Protection 1. Introduction Utilities have to supply power to their customers with highest reliability and minimum down time. System disturbances,
Al-Balqa Applied University Power systems Protection course Department of Electrical Energy Engineering 1 Part 5 Relays 2 3 Relay Is a device which receive a signal from the power system thought CT and
UProtection Requirements Ufor a Large scale Wind Park Shyam Musunuri Siemens Energy Abstract: In the past wind power plants typically had a small power rating when compared to the strength of the connected
2015 Relay School Bus Protection Mike Kockott March, 2015 History of Bus Protection Circulating current differential (1900s) High impedance differential (1940s) Percentage restrained differential (1960s)
2 Grounding of power supply system neutral 2.1 Introduction As we had seen in the previous chapter, grounding of supply system neutral fulfills two important functions. 1. It provides a reference for the
Notes 1: Introduction to Distribution Systems 1.0 Introduction Power systems are comprised of 3 basic electrical subsystems. Generation subsystem Transmission subsystem Distribution subsystem The subtransmission
Shortcomings of the Low impedance Restricted Earth Fault function as applied to an Auto Transformer Anura Perera, Paul Keller System Operator - Eskom Transmission Introduction During the design phase of
BUS2000 Busbar Differential Protection System Differential overcurrent system with percentage restraint protection 1 Typical Busbar Arrangements Single Busbar Double Busbar with Coupler Breaker and a Half
UNIT II - ELECTROMAGNETIC RELAYS Part A 1. Name the different kinds of over current relays. Induction type non-directional over current relay, Induction type directional over current relay & current differential
Back to the Basics Current Transformer (CT) Testing As test equipment becomes more sophisticated with better features and accuracy, we risk turning our field personnel into test set operators instead of
IMPORTANT NOTE: You should have received an email from us with a link and password to take your final exam online. Please check your email for this link. Be sure to check your spam folder as well. If you
Relay Coordination in the Protection of Radially- Connected Power System Network Zankhana Shah Electrical Department, Kalol institute of research centre, Ahemedabad-Mehshana Highway, kalol, India 1 firstname.lastname@example.org
PJM Manual 07:: PJM Protection Standards Revision: 2 Effective Date: July 1, 2016 Prepared by System Planning Division Transmission Planning Department PJM 2016 Table of Contents Table of Contents Approval...6
ELECTRICAL POWER TRANSMISSION TRAINER ELECTRICAL POWER TRANSMISSION TRAINER This training system has been designed to provide the students with a fully comprehensive knowledge in Electrical Power Engineering
1 1.1 Overview of Electrical Energy Systems They may occupy different angular positions, but all machines rotate at the same electrical speed. This close knitting implies an embedded interaction of generators
thepower to protect i-gard LITERATURE Low and medium voltage distribution systems Arc Flash Hazards and High Resistance Grounding Grounding of Standby and Emergency Power Systems Neutral Grounding Resistors
Overview of Grounding for Industrial and Commercial Power Systems Presented By Robert Schuerger, P.E. HP Critical Facility Services delivered by EYP MCF What is VOLTAGE? Difference of Electric Potential
UNIT II MEASUREMENT OF POWER & ENERGY Dynamometer type wattmeter works on a very simple principle which is stated as "when any current carrying conductor is placed inside a magnetic field, it experiences
The Electrical Power Engineers Qual-Tech Engineers, Inc. 201 Johnson Road Building #1 Suite 203 Houston, PA 15342-1300 Phone 724-873-9275 Fax 724-873-8910 www.qualtecheng.com ARC FLASH PPE GUIDELINES FOR
Transmission Line Protection Objective General knowledge and familiarity with transmission protection schemes Transmission Line Protection Topics Primary/backup protection Coordination Communication-based
SIPROTEC Protection Technology The Basis for Highest Availability of Supply Unrestricted Siemens AG 2016 www.siemens.com/ Objectives of this Brochure Objective The following examples give an overview of
Line Protection Roy Moxley Siemens USA Unrestricted Siemens AG 2017 siemens.com/digitalgrid What is a Railroad s Biggest Asset? Rolling Stock Share-holders Relationships Shipping Contracts Employees (Engineers)
6CARRIER-CURRENT-PILOT AND MICROWAVE-PILOT RELAYS Chapter 5 introduced the subject of pilot relaying, gave the fundamental principles involved, and described some typical wire-pilot relaying equipments.
OPEN-PHASE DETECTION TECHNIQUES FOR CRITICAL STANDBY SUPPLIES U AJMAL, GE Grid Solutions UK Ltd, email@example.com S SUBRAMANIAN, GE Grid Solutions UK Ltd, firstname.lastname@example.org H Ha GE Grid Solutions
Transformer Protection Principles 1. Introduction Transformers are a critical and expensive component of the power system. Due to the long lead time for repair of and replacement of transformers, a major
Residual current circuit breakers (RCCBs) Description Automatically trips in event of earth leakage fault Provides protection against direct & indirect contact with live parts Technical data IS 12640-1,
ODEN:TEDX/(TEE-7217)/1-12/(26) ndustrial Electrical Engineering and Automation entral or ocal ompensation of Earth-Fault urrents in Non- Effectively Earthed Distribution Systems Dept. of ndustrial Electrical
(7) (7) (5) Applications Installation Guide 7SR224 7SR21 ARGUS-M 7SR21 Recloser 7SR22 ARGUS-M Controller 7SR21 DOCUMENTATION SET This document is part of a set. The full list of documents in the set, and
Types CDG 11 and CDG 16 Inverse Time Overcurrent and Earth Fault Relay Types CDG 11 and CDG 16 Inverse Time Overcurrent and Earth Fault Relay Relay withdrawn from case Application The type CDG 11 relay
High Voltage DC Transmission 2 1.0 Introduction Interconnecting HVDC within an AC system requires conversion from AC to DC and inversion from DC to AC. We refer to the circuits which provide conversion
Fig 1. High impedance differential protection relay 7VH83 Features l Integral CT shorting relay. l Robust solid state design. l Inrush stabilisation through filtering. l Fast operating time. l LED indicator.
Application and Commissioning Manual for Numerical Over Current Protection Relays Type MIT 121/131 CONTENTS PAGE APPLICATION 2-4 INSTALLATION 5-11 COMMISSIONING 12-16 DRAWINGS 17-18 1 1. INTRODUCTION APPLICATION
ELEC0014 - Introduction to power and energy systems The power transformer Thierry Van Cutsem email@example.com www.montefiore.ulg.ac.be/~vct November 2017 1 / 35 Power transformers are used: to transmit
SPEEDFAX TM 2017 TSection C o n t e n t s Types of Power Distribution Systems T-2 T-4 Ground Fault Protection T-5 T-10 Overcurrent Protection and Coordination T-11 System Analysis T-12 Current Limiting
The Importance of the Neutral-Grounding Resistor Presented by: Jeff Glenney, P.Eng. and Don Selkirk, E.I.T. Presentation Preview What is high-resistance grounding (HRG)? What is the purpose of HRG? Why
Case Study Electromagnetic compatibility (EMC) study Breakdown of low voltage electronic equipment in a 25 kv substation Conrad Bottu Laborelec January 2008 Power Quality Power Quality 1 Introduction Description
2017 IJSRST Volume 3 Issue 2 Print ISSN: 2395-6011 Online ISSN: 2395-602X National Conference on Advances in Engineering and Applied Science (NCAEAS) 16 th February 2017 In association with International
DP&L s Technical Requirements for Interconnection and Parallel Operation of Distributed Generation Technical Requirements for Interconnection and Parallel Operation of Distributed Generation Single Phase
System Protection and Control Seminar Desirable Protection We want to detect a fault within 100% of the zone of protection. We want to avoid interrupting non-faulted zones of protection. We want to clear
PROTECTION SIGNALLING 1 Directional Comparison Distance Protection Schemes The importance of transmission system integrity necessitates high-speed fault clearing times and highspeed auto reclosing to avoid
1 Power System Protection Where Are We Today? Meliha B. Selak Power System Protection & Control IEEE PES Distinguished Lecturer Program Preceding IEEE PES Vice President for Chapters firstname.lastname@example.org PES
FAULT AND STABILITY ANALYSIS OF A POWER SYSTEM NETWORK BY MATLAB SIMULINK 1.Mrs Suparna pal Asst Professor,JIS College of Engineering (Affiliated to West Bengal University of Technology), Nadia, Kalyani,West
EE 1402 HIGH VOLTAGE ENGINEERING Unit 5 TESTS OF INSULATORS Type Test To Check The Design Features Routine Test To Check The Quality Of The Individual Test Piece. High Voltage Tests Include (i) Power frequency
Exercise 2 Overcurrent and Overload Protection of AC Machines and Power Transformers EXERCISE OBJECTIVE When you have completed this exercise, you will understand the relationship between the power rating
Current will always try to return to its source In order for there to be current, there must be a complete circuit Current will take as many paths or circuits available to it to return to the source The
MULTILIN GER-2681B GE Power Management Phase Comparison Relaying PHASE COMPARISON RELAYING INTRODUCTION Phase comparison relaying is a kind of differential relaying that compares the phase angles of the
Unit 4 AC s UNIT OBJECTIVE After completing this unit, you will be able to demonstrate and explain the operation of ac induction motors using the Squirrel-Cage module and the Capacitor-Start Motor module.
Section 3. Information contained within this section shall be read in conjunction with all sections of this manual Non - Compliant Test Results Where acceptable results are not attained in accordance with
Proceedings of the 5th WSEAS Int. Conf. on SIMULATION, MODELING AND OPTIMIZATION, Corfu, Greece, August 7-9, 5 (pp567-57) Power differential relay for three phase transformer B.BAHMANI Marvdasht Islamic
PART 1: GENERAL 1.01 Transformer A. This section includes liquid filled, pad mounted distribution transformers with primary voltage of 12kV or 4.16kV (The University will determine primary voltage), with
Lightning test in lab Symmetrical fault and protection Olof Samuelsson Outline Three-phase short-circuit fault current Network representation Circuit breakers and disconnectors Measurement transformers
Problems connected with Commissioning of Power Transformers ABSTRACT P Ramachandran ABB India Ltd, Vadodara, India While commissioning large Power Transformers, certain abnormal phenomena were noticed.
EH27401 Communication and Control in Electric Power Systems Lecture 2 Lars Nordström email@example.com 1 Course map 2 Outline 1. Power System Topologies Transmission Grids vs Distribution grids Radial grids
Design, Engineering and Application of New Firm Capacity Control System (FCCS) Mohammed Y. Tageldin, MSc. MIET Senior Protection Systems Engineer ABB United Kingdom firstname.lastname@example.org Hamdy Faramawy
Ground Fault Currents in Unit Generator-Transformer at Various NGR and Transformer Configurations A.R. Sultan, M.W. Mustafa, M.Saini Faculty of Electrical Engineering Universiti Teknologi Malaysia (UTM)
Reliability Guideline Transmission System Phase Backup Protection NERC System Protection and Control Subcommittee Draft for Planning Committee Approval June 2011 Table of Contents 1. Introduction and Need
Downloaded from orbit.dtu.dk on: Apr 23, 2018 System grounding of wind farm medium voltage cable grids Hansen, Peter; Østergaard, Jacob; Christiansen, Jan S. Published in: NWPC 2007 Publication date: 2007
Reducing the Effects of Short Circuit Faults on Sensitive Loads in Distribution Systems Alexander Apostolov AREVA T&D Automation I. INTRODUCTION The electric utilities industry is going through significant
UNVERSTY OF SWAZLAND SUPPLEMENTARY EXAMNATON, SECOND SEMESTER MAY 2017 FACULTY OF SCENCE AND ENGNEERNG DEPARTMENT OF ELECTRCAL AND ELECTRONC ENGNEERNG TTLE OF PAPER: Switchgear and Protection COURSE CODE
PS3: Substation Design: New Solutions and Experiences Bus-Node Substation A Big Improvement in Short-Circuit and Switching Properties at Reduced Substation Costs G. KOEPPL Koeppl Power Experts Switzerland
Distribution Feeder Principles Distribution Feeder Principles Introduction Electrical distribution is the final stage in the delivery of electricity to end users. The distribution system s network carries
Working Group D-3, Line Protection Subcommittee IEEE PES Power System Relaying Committee Considerations in Choosing Directional Polarizing Methods for Ground Overcurrent Elements in Line Protection Applications
Summary Paper for C37.243 IEEE Guide for Application of Digital Line Current Differential Relays Using Digital Communication Participants At the time this draft was completed, the D32 Working Group had
Demagnetization of Power Transformers Following a DC Resistance Testing Dr.ing. Raka Levi DV Power, Sweden Abstract This paper discusses several methods for removal of remanent magnetism from power transformers.
Three-Phase Induction Motors 1 2 3 Classification of AC Machines 1. According to the type of current Single Phase and Three phase 2. According to Speed Constant Speed, Variable Speed and Adjustable Speed
Transformer differential protection Page 1 Issued June 1999 Changed since July 1998 Data subject to change without notice (SE970883) Features Three phase differential protection with two, three, five or
Grounding and Bonding of Service Equipment 1. Grounding means: attached to an earth ground. 2. Bonding means: physically connected to insure electrical continuity. NEC 250.4 1. Grounding: Electrical Systems
Protecting Large Machines for Arcing Faults March 2, 2010 INTRODUCTION Arcing faults occur due to dirty insulators or broken strands in the stator windings. Such faults if undetected can lead to overheating
Alberta Interconnected Electric System Protection Standard Revision 0 December 1, 2004 APEGGA Permit to Practice P-08200 Table of Contents Signature Page... 2 Table of Contents... 3 1.0 STAKEHOLDER REVIEW
In this lecture Electromagnetism Electromagnetic Effect Electromagnets Electromechanical Devices Transformers Electromagnetic Effect Electricity & magnetism are different aspects of the same basic phenomenon:
Power Plant and Transmission System Protection Coordination Phase Distance (21) and Voltage-Controlled or Voltage-Restrained Overcurrent Protection (51V) NERC Protection Coordination Webinar Series June
Effective System Grounding By Andrew Cochran of I-Gard and John DeDad of DeDad Consulting The costs associated with losses stemming from ground faults are staggering. For example, over a seven year period,
WHITE PAPER Medium Voltage On-Site Generation Overview BY MIKE KIRCHNER Technical Support Manager at Generac Power Systems INTRODUCTION It seems that just about everyone is looking for more power. As our
Testing of Circuit Breaker and over Current Relay Implementation by Using MATLAB / SIMULINK Dinesh Kumar Singh email@example.com Abstract Circuit breaker and relays are being utilized for secure,
Transmission Line Applications of Directional Ground Overcurrent Relays Working Group D24 Report to the Line Protection Subcommittee January 2014 Working Group Members: Don Lukach (Chairman), Rick Taylor
Current transducer ITC 2000-S/SP2 N = 2000 A For the electronic measurement of current: DC, AC, pulsed..., with galvanic separation between the primary and the secondary circuit. Features Bipolar and insulated